Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AGE of WATER HEATERS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
ALTERNATIVE HOT WATER SOURCES
ANODES & DIP TUBES on WATER HEATERS
ANTIFREEZE for BOILERS
ANTI SCALD VALVES
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
AQUASTAT CONTROL Functions
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER, HEATER WATER FEEDER
CARBON MONOXIDE - CO
CHECK VALVES, WATER SUPPLY
CHEMICAL CONTAMINANTS in WATER
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CLOGGED SUPPLY PIPING
DEBRIS in WATER SUPPLY, Water Heater
DRAIN a WATER HEATER TANK
ELECTRIC WATER HEATERS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
GALVANIC SCALE & METAL CORROSION
GAS BURNER FLAME & NOISE DEFECTS
GAS FIRED WATER HEATERS
GAS PIPING, VALVES, CONTROLS
HOT WATER SUPPLY
INDIRECT FIRED WATER HEATERS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
NO HEAT - NO HOT WATER: HEATER DIAGNOSIS
NOISE / SOUND DIAGNOSIS & CURE
NOISE CONTROL for HEATING SYSTEMS
NOISE, PLUMBING CHECKLIST
NOISE, WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
PIPING IN buildings, Clogs Leaks Types
PLASTIC PLEXVENT ULTRAVENT RECALL
PLUMBING FIXTURES, KITCHEN, BATH
RELIEF VALVE LEAKS
RELIEF VALVE, WATER HEATER
SCALE REMOVAL, WATER HEATERS
SEWER GAS ODORS
SOLAR HOT WATER HEATERS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCH, FLUE GAS DETECTOR
TANKLESS WATER HEATERS
Temperature Pressure Relief Valves - Water Heaters
THERMOSTATS, WATER HEATER
TIMERS for ELECTRIC WATER HEATERS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PIPES, Clogs Leaks Types
WATER PRESSURE MEASUREMENT
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER QUANTITY IMPROVEMENT
WATER SOFTENERS & CONDITIONERS
WINTERIZE A BUILDING
Water heater or calorifier scale & lime prevention:
How to stop scale and lime formation in water heaters: here we explain how to Prevent Future Scale Deposits in Water Heater Tanks or on Electric Water Heater Electrodes - Scale formation in water heaters and methods of prevention.
The articles at this website will answer most questions about diagnosing and curing noisy domestic water heaters and about the procedure to remove mineral deposits, lime, water scale, silicates, sulfates, aluminates, or silt and sand from a water heater tank.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Step 3: How to Prevent Future Scale Deposits in Water Heater Tanks or on Electric Water Heater Electrodes
Scale formation in water heaters and methods of prevention
At WATER HEATER SCALE DE-LIMING PROCEDURE we discussed how to remove existing scale and line from a water heater. Here we continue with water heater de-liming Step 3: advice on how to prevent scale and lime formation in or on water heating equipment.
Photo at left: Limescale deposits, SEM scanning electron microscopy micro-graph with a field of view of just 64 x 90 microns. Source: "Limescale" - Wikipedia, retrieved 11/13/2013 [Click to enlarge any photo or image]
Lime and scale in a hot water tank, caused by hard water as well as silicates, sulfates, and similar materials form water scale that coats the bottom of a hot water tank or the surface of the electrodes in an electric water heater, interfering with proper water heater operation, causing water heater noises, reduction in hot water quantity, increased water heater operating costs, and a shorter water heater life.
Silt and soil debris can also collect in a water heater tank where it can cause similar problems even if the water supply is not hard.
Silt and debris can be easily removed from a hot water tank by periodic flushing. In fact if your water heater is quite noisy, it will probably be easier to remove un-wanted mineral deposits from the water tank than it will be later if you wait until the heater is no longer making much noise (because the mineral layer has solidified). Install a sediment filter on the incoming water supply to avoid this problem in the first place.
But lime or water scale are more difficult to remove from (and easier to prevent in) a water heater: manually scraping the tank bottom through the drain opening or use of a de-limer chemical will be needed. Below we describe these procedures. Readers should also see our discussion of mineral clogging of water piping, water heaters, and tankless coils, organized at HOT WATER IMPROVEMENTS.
Other gas fired water heater noises are discussed at GAS FLAME & NOISE DEFECTS.
Lowering Hot Water Heater Temperature Will Significantly Reduce the Rate of Lime & Scale Formation in a Water Heater Tank
The rate of deposition of scale inside of a water heater tank depends on
Water heated to higher temperatures deposits lime much faster than at lower temperatures. The Purdue University bulletin cited above charts the relationship between water temperature, total gallons of hot water used per day, and the annual quantity of lime deposition in a plumbing system. Our table below shows data for typical residential use of a hot water heater. At larger volumes of daily use the same relationship holds but the total quantity of lime deposited is much greater.
Thanks to researcher Robyn Goldstein for the full citation of Scale formation in water heaters and methods of prevention", Purdue Bulletin No. 74.
Surprisingly, while scale formation in water heaters was found to be rapid at higher temperatures, the water heater thermal efficiency was not as significantly effected as the researchers anticipated. It was also interesting that scale formation in the heater was not uniform - because temperatures across a water heater and its parts are themselves not uniform.
What is important about this data is the dramatic reduction in scale and lime formation in water heaters when the temperature was reduced from 175 degF. down to 140 degF. Considering that hot water is dangerously scalding even at 140 degF, only where scale formation is not a problem (low mineral content in the water source) and where a cold water mixing valve has been installed for safety, would it be reasonable to operate a residential water heater at high temperatures.
Back in 1940 Krappe reported that unlike high temperature residential heating boilers (heating water to 180-200 degF) where lime and scale formed rapidly in a tankless coil (TANKLESS COILS) ,
in side-arm type water heaters ( RANGE BOILER WATER HEATER
or SIDE ARM COIL WATER HEATER) attached to boilers, (and in separate water heaters heated to high temperatures), gas fired water heaters fitted with temperature controls that kept water below 140 degF. were often found to run for 8 years or longer with little or no scale formation problems.
The role of high temperature in water heater lime and scale formation also explains the rapid clogging of tankless coilsused for domestic hot water production. Residential heating boilers regularly operate at temperatures between 180 degF. and 200 degF., causing rapid scale formation where hard water is passing through the tankless coil.
Types of Water Heaters & Scale Formation
Krappe listed the following types of water heating devices in order of their tendency to "give service difficulty from scale formation"
How Mineral Deposits and Heating May Weaken a Water Heater Tank Bottom, Contributing to BLEVE Explosion
The photo (left) shows a hole in the roof made when a water heater exploded, becoming a rocket that passed up through the building.
[Click to enlarge any image]
But if the safety valve has been damaged, modified, or even omitted (as we saw on our neighbor's water heater), that condition, combined with overheating can cause a water tank to explode, creating a BLEVE - boiling liquid vapor explosion that releases tremendous force and causing extreme damage to a building.
Because repeated heating of the water tank bottom may combine with other conditions (such as corrosion or excessive heating due to mineral deposits on the tank bottom) to produce a weak water heater tank bottom, that is the part more likely to fail in an overheat and overpressure condition.
A failure at the water tank bottom may explain why a BLEVE can produce a water tank explosion that behaves like a rocket, sending the water tank skyrocketing up through a building.
Why and how the calorifier coils are affected by scale and corrosion
7 Jan 2015 Prabhu said
Could please suggest me why and how the calorifier coils get affected by scale and corrosion?
Also suggest to me some points to avoid these effects.Thanks
Let's separate calorifier scaling from calorifier corrosion.
Scaling is the formation of a hard mineral deposit on the internal surfaces of a water heating device. Scaling occurs because of the combination of a water supply that is high in mineral content (usually calcium and magnesium) and heat that causes minerals to precipitate out of the water and onto the heater surfaces forming scale. The article above addresses scale prevention.
Corrosion is the deterioration of (in this case) metal surfaces in a calorifier or piping surfaces, not scale deposition (though both can occur in a single system). Corrosion in water systems is a feature of water chemistry. Some water may have a high index of corrosivity.
Municipal water supplies are in most communities required by law to be maintained within acceptable limits of hardness (mineral content) and corrosiveness (corrosivity index). But property owners served by a private well bear that responsibility themselves.
Have your water tested for hardness and corrosivity - that can tell you what water treatment equipment may be needed.
8 January 2015 prabhu said:
"Water quality" is a rather broad and vague term. The answer is yes but only by being more specific can we be useful The specific water qualities involved in tankless coil clogging are hardness and the specific qualities involved in corrosion include a corrosivity inde of the water along with possibly other chemicals in it.
See also CORROSIVITY or ACIDITY of WATER
Cures for Hard Water that Clogs Hot Water Tanks, Tankless Coils, and Plumbing Pipes
See WATER SOFTENERS & CONDITIONERS for suggestions about dealing with hard water in buildings. [Live link is given just below]
Continue reading at WATER HEATER SCALE DE-LIMING PROCEDURE or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
None here yet - post yours.
Questions & answers or comments about scale and lime formation in water heaters.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References