TANKLESS COILS - home - CONTENTS: Tankless Coils on heating boilers: a guide to tankless coils for domestic hot water supply: capacity, safety, clogging, adjustment, cleaning, & Repair Guide. How much water can we get out of a tankless coil before running out? What can we do to improve the amount of hot water from a tankless coil? Preventing scalding where a tankless coil is used for hot water - setting the hot water temperature and using anti-scald valves. Use of a Single Function Boiler Temperature Limit switch and Anti Scald Valves with Tankless Coils
POST a QUESTION or READ FAQs about tankless coils used to produce domestic hot water: clogging, leaks, water quantity, water temperature, scale formation and cleaning
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Tankless coils unwound: using a tankless coil for domestic hot water for washing and bathing.
Here we explain the function, use, capacity, inspection, and repair of Tankless Coils on heating boilers: a guide to tankless coils for domestic hot water supply: capacity, safety, clogging, adjustment, cleaning, & Repair Guide
This article series answers most questions about Heating System Boiler Controls on central heating systems to aid in troubleshooting, inspection, diagnosis, and repairs. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
A Guide to Tankless Coils for Domestic Hot Water Production
Tankless coils used on heating boilers: This device, basically a coil of finned copper tubing which is inserted into the heating boiler, is used to provide
domestic hot water to some buildings.
[Click to enlarge any image]
Watch out for leaks at piping fittings or more seriously the coil mounting plate which bolts the coil to the
boiler (leaks at this location can destroy a steel boiler).
Watch out also for missing a mixing/tempering valve which mixes cold in with the outgoing hot water to avoid scalding temperatures
at nearby taps. Some building jurisdictions require a separate temperature/pressure relief valve on hot water piping at the boiler.
The photo shows a pile of tankless coils found in a building basement next to the heating boiler. We suspected that high mineral content
in the building's water supply was causing frequent coil clogging.
Hot Water Temperature Control with Tankless Coil Heating Systems
The heating boiler, hot water or steam, will include a temperature limit control switch dedicated to maintaining temperature in the heater's interior for purpose of heating the coils of the tankless coil.
As the illustration at left shows, domestic hot water is heated by passing cold water through a finned copper coil which is in turn immersed in hot water inside of a heating boiler.
The temperature and effective quantity of domestic hot water received at a fixture in the building for washing and bathing is set, affected, or controlled by these things:
The water temperature inside the boiler and in contact with the tankless coil
The volume of hot water inside the boiler in contact with the tankless coil - larger boiler or larger volume of hot water in the boiler means that there is more heat to transfer into the coil
The thermal mass of the boiler itself - steel boilers have less thermal mass than cast iron boilers of the same size, and modern, small-sized high-efficiency heating boilers are likely to have much less thermal mass than an antique and huge cast iron boiler. Running the small efficient boiler at higher temperatures can grab back a little of this thermal storage.
The rate at which incoming water passes through the tankless coil - faster flowing water absorbs less heat from the boiler. HOT WATER CIRCULATOR PUMP SPEEDS DELIVERY can speed up the water flow, at the cost of drawing heat out of the boiler faster, thus possibly reducing the time duration over which hot water is provided.
The settings of the aquastat or low-limit LO and differential DIFF controls. Keeping the boiler at a higher temperature and setting a higher DIFF will in general store more heat in the boiler and should thus allow a tankless coil to provide a greater volume of hot water before the system runs out of heat.
See AQUASTAT CONTROL FUNCTIONS.
The settings of the anti-scald valve or mixing valve - setting the anti-scald valve to a lower output temperature means that it mixes more cold in with outgoing hot, drawing heat out of the boiler and through the tankless coil more slowly than otherwise. You get "longer hot water on time" because you draw heat out of the boiler more slowly.
See ANTI SCALD VALVES.
Considering these factors, you can understand that converting a large old cast iron home heating boiler with a tankless coil to a new small high-efficiency steel heating boiler that also includes a tankless coil may result in a new heating system which is more efficient and economical, but it may provide less total domestic hot water than the old system.
Use of a Single Function Boiler Temperature Limit switch and Anti Scald Valves with Tankless Coils
Here is a photo of a more traditional single-function heating boiler limit controls. In this example the limit switch is being used on a tankless coil, and in the enlarged version of the photo you'll see that the temperature limit on the control is set to about 140 degF.
When a heating boiler uses a tankless coil to produce domestic hot water, a third single-function control may be installed for that purpose. In this photo a Honeywell limit control switch is being used to monitor hot water temperature at the tankless coil which is in turn mounted on a steam boiler of an older home in Portland, Maine. You can see the black-handled mixing valve in the lower right of this photo.
Cold water from the building is entering the tankless coil via the bottom pipe (green corrosion) and hot water, heated by the coil is leaving at the upper part of the tankless coil, where it turns downwards to enter the left side of the mixing valve.
Additional cold water is permitted to enter the bottom of the mixing valve, and tempered (non-scalding) hot water then leaves at the right side of the mixing
Anti-scald valve used with water heater limit switch: In this photograph a single function limit switch is in use on a water heater, not on a heating boiler.
Here too you will notice that there is also a mixing valve installed to prevent scalding - the gray-handled device to the right of the control (and leaking we might add).
The use of a mixing valve or anti-scald valve permits us to set the Honeywell 6006 limit control switch to a higher number, keeping the water in the heater at a higher temperature.
The mixing valve in this photo adds cold to the outgoing hot water to avoid scalding, and at the same time we have more total domestic hot water for washing and bathing than if we omitted this pair of controls.
How to avoid being scalded by hot water from a tankless coil
See MIXING / ANTI-SCALD VALVES for details about mixing valves on boilers and tankless coil systems and for an explanation of how an anti-scald or tempering valve can increase the volume of hot water available from a tankless coil hot water system.
How to deal with clogged hot water piping that reduces hot water pressure and flow
Questions & answers or comments about tankless coils used to produce domestic hot water: clogging, leaks, water quantity, water temperature, scale formation and cleaning
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: firstname.lastname@example.org
 Bosch Tankless Water Heaters - http://www.boschhotwater.com/
[1a] Bosch, "Instrucciones de instalacion y manejo, Calentador de agua instantaneo, Confort / Confort S 6BP / 6BP n 10BP / 10BP N 13BP / 13BP N"
Robert Bosch, S. de R.L. de C.V., Calle Robert Bosch 405, Zona Industrial, Toluca, Edo de Mexico CP 50070, website: www.bosch.com.mx, Tel: 800-11-26724 (2010)
 Chromolite Tankless Water Heaters
 U.S. Department of Energy on Tankless Water Heaters - http://apps1.eere.energy.gov/consumer/your_home/water_heating/index.cfm/mytopic=12820
 "Tankless or Demand Type Water Heaters,"U.S. Department of Energy, retrieved 10/14/2012, original source: http://energy.gov/energysaver/articles/tankless-or-demand-type-water-heaters [Copy on file as Tankless_Water Heaters_DOE..pdf] retrived anew 2/25/2014
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones