InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Sewer line backup prevention:
This document explains for homes connected to a municipal sewer we discuss how to prevent sewer or storm drain backups into a building during rain or heavy flooding including the installation and use of backflow preventers, backwater valves, check valves and toilet drain plugs.
Here we discuss an example case of a midnight main sewer line backup into a home washing machine. Use of check valves or backwater valves to avoid basement flooding from heavy rain. Main sewer line or drain line check valve installation & inspection, maintenance. Choose or make a plug for toilets that overflow during sewer line backups? Check valves for basement floor drains.
Definition of backwater valve: as used here a backwater valve is a check valve installed on a building drain to prevent backup should the drain line receive floodwaters from outside the building, such as due to area flooding or a septic or sewer line backup.
The sewer line back flow prevention valve shown at page top is produced by Mainline Backflow Products - Backwater Valves (image use permission).
If toilets are overflowing, see TOILET OVERFLOW EMERGENCY.
If your building drains are already backing up, especially during a time of heavy use such as with guests in the home, see SEPTIC BACKUP REPAIR
or for homes connected to municipal sewer, see CLOGGED DRAIN DIAGNOSIS & REPAIR
If your sewer or septic system uses a sewage pump, be sure to review SEPTIC PUMPS
If your home is connected to a private septic system and drains are already backing up, especially during a time of heavy use such as with guests in the home, see SEPTIC BACKUP REPAIR.
One of our clients in Cold Spring New York reported waking during the night to hear their old basement clothes washer running. Having just moved into the home the occupants wondered what ghost was doing laundry at 2 AM. Investigating they found that the local municipal sewer had backed up into the home through the main drain line.
Because their washing machine drain was improperly connected (without an air gap) to a drain line, and as it was the lowest plumbing fixture in the home, the clothes washer had literally filled up with sewage. Since this old clothes washer included a pressure switch that automatically turned on the washer when it sensed that the tub was filled, the washer had not only received backing up sewage, but had begun agitating it in the middle of the night.
Further investigation showed that sewer backups were notorious in the neighborhood, and that this home lacked a sewage backflow preventer at the home's connection to the sewer line. The home suffered from
I had a sewer backup into my home again yesterday at a basement toilet. Our main line has a sewer back-up flap [a wastewater check valve or backwater valve].
The main sewer line check valve works fine when sewer is full from a very heavy rain in a short time. But yesterday we had 60 cm rain in 30 minutes. I had back-up valves on the sink, vanity, shower,clothes washer (drains).
The only place where backup occurred is the basement toilet. I managed placing a ball of rags into the toilet and applying pressure that stopped the water.
Our backup was actually clean water from a flat roof draining into the sewer venting pipe. This is a duplex home.
Is there such a thing as a soft plastic or other material filled that would take the shape of the toilet and prevent water coming back up as overflow. Like I did with a ball of cloths, and a brick wrapped in plastic. It did the trick in an emergency, but it's not practical. - (Anonymous by request)
The advantage of installing a main sewer line backup prevention valve is that this device will avoid having to plug multiple drains in the home, and the valve, basically a big check valve, is always in place - you don't have to do a thing to get it to work.
If you are having plumbing or sewer line drains back up, including at the toilet, then either your main sewer line check valve is not working, or your backup is occurring (as you suspect) because water or wastewater is draining into your in-house building drain/waste/vent system before or ahead of the main sewer drain check valve.
While you could install another check valve at or near the basement toilet waste line, it makes more sense to install just one such valve to protect the entire building and to make sure that one is working properly.
Stuffing a rag or any other temporary "block" into a toilet or other drains is not the best approach to this problem. Not only can it be unsanitary and a health risk in some cases , but also, who is going to stuff drains when flood conditions occur and no one is at home?
First you may want to have your main waste line backup check valve inspected - if the sewer line is backing up from the street into your home, your main sewer sewer backup valve (waste backwater valve) or a flood guard valve is not working properly it won't protect from flooding from storm drainage or sewage backups.
Here is a CHECK VALVE MAINTENANCE GUIDE [PDF] from the City of Ann Arbor, MI.
Mainline Backflow Products, a producer of sewer line check valves and related products, informs us that:
Many municipal Building Codes require you to have a backwater valve if your plumbing fixtures are below the top of the first upstream manhole on your street. A properly operating backwater valve allows flow to only go in one direction (out), preventing wastewater from entering your building during regular sewer system maintenance or accidental sewer system backups.
To find out if you have or need a backwater valve, check your plumbing plans or consult with your builder or a professional plumber. Remember, if sewage backs up into your home, the cost to repair damages and clean up the mess will be well high than the cost to install a valve. Laws allow that towns and municipalities cannot be held liable for damages when a backwater valve has not been installed by a property owner.
The City of Chicago and folks writing about Chicago sewer backups offer advice about avoiding sewer backups including the use of basement floor drain standpipes:
A stand pipe is a short section of pipe that when screwed into the basement floor drain will prevent water from coming in through the drain.
However, if there is enough pressure in the sewer system, the sewage will rise through the wash machine drain connection, utility sink, and basement bathroom fixtures. A stand pipe does nothing to relieve the pressure in the sewer system, and can cause the sewer lines to crack or break under the foundations.
When this happens, the sewage will cause cracks in the basement floor, and may come through the basement walls. If there is enough pressure, the basement walls can collapse, or the foundation can "float" out of its hole. In the worst case, the entire house can collapse into the basement. Because of these dangers, stand pipes and other methods of blocking the drains ARE NOT RECOMMENDED!
Second, you should disconnect your roof drainage from the sewer piping system entirely, routing it to a nearby storm drain, or to the ground surface (at least 12 feet away from the building and to a location that drains away from the building to avoid basement flooding).
If connecting roof runoff drains to the sewer system is actually permitted in your neighborhood, try changing the drain connection to one that is downstream from your main sewer line trap and check valve.
By the way, in some communities it is illegal to rout roof runoff into the sewer piping. Doing so significantly increases the wastewater volume load on the municipal sewer treatment system so severely that during a storm the sewage treatment plant simply overflows, dumping raw sewage into nearby rivers or waterways.
A clogged building drain can also lead to a sewage backup or toilet overflow even if the main drain is properly protected from sewer line backups. Flushing needles, diapers, paper products, sanitary products, and grease into drains is always a bad idea.
We discuss some of these items for homes served by private septic systems at NEVER FLUSH INTO SEPTICS. It's a good idea to keep those same items out of drains connected to a municipal sewer as well.
See CLOGGED DRAIN DIAGNOSIS & REPAIR for details about slow or clogged plumbing drain diagnosis, prevention, and repair.
In addition, or sometimes instead of a main sewer line check valve, flood guards are often installed in individual floor drains for drains up to 4" in diameter. But if a main sewer drain check valve is installed and we are not draining roof runoff into the building drain piping, these should not be needed except on floor drains that connect not to the sewer piping but to a separate storm drain system.
Quick question, when it rains hard where I live our basement toilet backs up with water. Is there a plug of some sort I can put in it to stop this from happening.
Something like a shower plug but that would work in toilets. Thank you for your time. J.P.
A competent onsite inspection by a plumbing expert who is familiar with sewer backups usually finds additional clues that help accurately diagnose a problem such as an improper house drain installation, other sewer backup risk points such as basement floor drains or sinks, even washing machines, or the need for a check valve or backflow preventer valve at your home main drain.
How to plug or seal off a basement toilet against sewer backups - temporary toilet seals are unreliable and risky but here are some suggestions for preventing sewage backing up through a toilet on the building's lowest floor.
We don't know about a functional plug that fits in a toilet bowl and that reliably seals any toilet bowl shape against sewer backups.
As we describe here, there are however plumbing drain test plugs designed for all sizes of drain piping including ones commonly used to close off a toilet drain opening when no toilet is installed. And one type of these might work to seal some toilet bowls, depending on the toilet bowl shape and dimensions.
Typically a toilet drain piping itself is 4" in diameter and can sealed easily using a 4" expanding test plug. But sealing the drain inside a toilet bowl against sewer backups is a different matter.
Nylon or metal based expanding plumbing drain test plugs using rubber, silicone, neoprene, nitrile, or vitron flexible seals are devices that employ a screw and compression plate to permit a plug to be inserted and expanded to seal a round drain opening.
Plumbing drain test plugs used for testing plumbing drains for leaks (openings are plugged and the drain system is pressurized) are available from most plumbing suppliers.
But most plumbing drain system test plugs such as Pipestoppers™ won't work nor seal properly in openings that are not round. 
An exception that might fit some toilet bowls and permit plugging an in-place toilet against occasional sewer backups are inflatable plumbing test plugs such as the Petersen line of inflatable plumbing test plugs and the Test Ball® Inflatable Plumbing Test Plugs produced by Cherne Industries.  
Watch out: plugging a basement toilet or toilet drain might stop sewer backups that have been flowing up and out into the building through one or more toilets found on its lowest level.
But if other drain openings are present, the rising pressure from a sewer line backup may simply find the next higher drain opening (bath tub, sink, shower floor, even washing machine). That's why we recommend the alternative sewer backup prevention steps listed
If your home includes a basement toilet that is a source of sewer backups, and if there are no other low-building drains that will assume that role if the toilet is eliminated, we suggest you consider removing the toilet completely, abandoning its use, and plugging the toilet drain line at floor level.
But if the basement toilet is needed and/or if there are simply other drains that will become the sewage backup and entry points if the toilet is removed, abandoning the toilet doesn't make sense.
That said, our last suggestion is the best solution - a check valve (properly referred to as a backflow prevention valve or in some areas a "backwater valve") can be installed on the main building drain can prevent sewer backups through the toilet when the area sewer lines are flooding.
If your home is subject to frequent risk of flooding or water entry or sewer backups, look into a flood alarm that can be installed along with the backflow preventer valve on your main building drain.
Alarms are available that sense water on the basement floor, indicating the beginning of water entry and provided someone is at home, giving time to investigate and take action.
But when discussing sewage backups through lower floor drains or toilets, we refer you instead to a somewhat different product such as the Rialco™ flood alarm  that is integrated into your backflow preventer, informing you when that special check valve has closed against a sewer backup.
By installing a replacement waterproof cap on the backwater valve installed at the main building drain, the modified back-water valve cap permits connection of the Rialco flood alarm sensor tubing to a port that will inform the alarm that the backwater valve has been activated.
Thus the building owner or occupants are informed of sewer line flood conditions as well as of the fact that the valve is working.
Besides backflow preventers, other types of check valves used on building plumbing and heating systems are discussed at CHECK VALVES, WATER SUPPLY.
Don't confuse a backwater valve with a backflow preventer used on water supply piping and discussed separately at BACKFLOW PREVENTER on Heating Sys Water Feed.
(Aug 13, 2014) Denny Mack said:
In regards to J.P.'s question regarding sticking a plug inside the toilet bowl to prevent an emergency sewer backup, I performed a test. I have a Kohler Adair toilet in my basement. The hole in the bowl is approximately 3 inches give or take. I inserted a 3 inch Cherne Inflatable test plug three quarters of the way in the hole.
Even though these plugs are not specifically made for this application, I was desperate to try anything to avoid a sewage disaster. Important notes: It took about a half second shot with my compressor to inflate. (A bicycle pump will not work) Know your compressor. You may want to hold the plug in your hand and test inflate before putting it in the bowl. Also, read the test plug instructions regarding PSI.
After inflating, I flushed the toilet to trap some water. I marked the water level, then returned 2 hours later to check it. The water level was unchanged. Even though I have no clue if the inflatable plug stresses the porcelain, if carefully done, it appears to be an effective plug for this model toilet.
25 June 2015 karen holmes said:
How much does it normally cost to put a check valve in..We had one backup of sewer and don't want another
The installed cost for a sewer line check valve (backwater valve) is the sum of parts plus labor and ranges from $1000. to two or more times that depending on just what is required. For a ballpark estimate consider the following cost for an indoor basement floor check valve then read the added details we give just below:
Parts for the sewer line backwater valve and floor access box: $300.
Labor to install an in-floor backwater valve in a basement including concrete removal, excavation, sewer line cut, valve installation, installation of a floor access box, and concrete repair: $750.
Total installed cost for a sewer line check valve cost: $1050. USD.
Plumbing permits and inspections may be required in some jurisdictions as well.
The price of a backwater valve also referred to as a main sewer line check valve or "mainline check valve"ranges between about $150. and $300. USD depending on the backwater valve model and features. Add an additional $70. if an in-floor access box is required for your location.
The labor for installation of a backwater valve is likely to be significantly more than the cost of the valve itself and is typically billed in hours for plumbing service to which an added cost for backhoe and excavation or concrete removal is required in some situations. Those costs vary depending on where you live but you can figure roughly $100-$350 per day and up to rent a small backhoe, or you can expect to pay $50. to $100. per hour to hire a backhoe operator if outdoor excavation is required to expose your sewer line.
The installation cost for a sewer line check valve varies depending on
Continue reading at SEPTIC BACKUP REPAIR or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
(Nov 2, 2012) m said:
i live in Brooklyn NY and have experienced a flood in the basement during both Irene and Sandy. This last time we had 5 feet of water that came up through the drain in the floor of the basement. Is there any product i can use that would prevent this?
(Mar 20, 2013) email@example.com said:
One story house, no one at home, no water running, no rain for MONTHS but my sewer backed up and flooded half the house with raw sewage! How & why? Any ideas?
If the public sewer or even a private septic system is blocked and flooded with water or sewage from other site drainage or other sewer system users, the system can certainly back up into a home.
(June 2, 2015) anonymous said:
I have a Backflow Prevention (Check) Valve installed on my main drain line just outside my house. Can I install a second Backflow Check Valve just before the sidewalk as "double protection" (in case one fails)?
Yes. In some situations and jurisdictions double backflow prevention check valves may even be required. Check with the manufacturer for the speciific product you intend to use.
Try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website