Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
ANTIFREEZE for BOILERS
BACKUP PREVENTION, SEWER LINE
BLOCKED DRAIN REPAIR METHODS
CLEANOUTS, PLUMBING DRAIN
CLOGGED DRAIN DIAGNOSIS & REPAIR
FREEZE-PROOF A BUILDING
FROST HEAVES, FOUNDATION, SLAB
HEAT TAPE USAGE GUIDE
HOT WATER HEATERS
INSULATION INSPECTION & IMPROVEMENT
NO HEAT - BOILER
NO HEAT - FURNACE
ODORS GASES SMELLS, DIAGNOSIS & CURE
OIL FIRED WATER HEATERS
PIPING IN buildings, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PUMPS, PONY PUMPS
RELIEF VALVE LEAKS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SUMP PUMPS GUIDE
TRAPS on PLUMBING FIXTURES
WATER HEATER PROBLEM DIAGNOSIS
WATER HEATER COMPARISONS, PROPERTIES
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Freeze-protection for buildings: this article explains where, why, and how to add pipe insulation or in some cases building insulation and draft-stopping materials at cold problem spots to avoid freezing pipes.
The articles in this series will answer most questions about freeze protection for piping and other building plumbing and heating system components: how to winterize a building to avoid frozen pipes, and how to thaw frozen water supply & drain piping, wells, & water tanks, heating system piping and heating oil piping.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Add Water Pipe insulation to prevent freezing: can be added to protect pipes routed through un-heated areas or near cold building corners. We particularly like to add slip-on foam pipe insulation where a plumbing line is run past a cold spot that is hard to warm up.
Some writers believe that if you insulate all of your water supply piping you won't have a frozen pipe problem. That may be a bit optimistic: we fear that a cold corner somewhere will be missed and left un insulated, or that a house left without heat for too long will get cold enough to freeze even an insulated pipe.
The advantage of insulating pipes is that it slows the rate at which a water pipe will freeze, possibly getting the pipe through the coldest part of the night and into a (hopefully) warmer daytime to warm-up again.
Remember, when insulating a water pipe, that you need to insulate all of it. Don't leave those awkward elbows or pipe tees un insulated.
Does Insulation Prevent Pipe Freezing in Prolong Cold Periods? Probably Not.
Watch out: Here is a speculative warning about relying on pipe insulation alone to avoid freezing, that is, we don't have hard science to back up this opinion:
Plastic piping to resist freezing: modern plastic piping is considerably more tolerant of freezing without bursting than copper or steel water pipes. In a home intended for regular winterization some builders use exclusively plastic pipes to resist freeze damage.
Watch out: even when freeze-tolerant piping is used, the piping connections, elbows, unions, couplings, and plumbing fixtures are still at risk of frost damage.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about where & how to add heat to freeze-proof water pipes in a house
Question: what about using heat tape on sewer pipes - our mobile home sewer line keeps freezing
You don't say anything regarding using heat tape on sewer pipes. We have an annual problem with a mobile home sewer line freezing. The line connects a toilet, shower and tub so when it freezes it is a mess. - Anon. 9/19/11
Anon, you can add a heat tape on a sewer line provided the tape you choose is connected and secured to the sewer line the way the manufacturer instructs. Make sure that the bottom of the waste pipe is in contact with the heat tape, and provided the heat tape manufacturer permits, insulate the line as well. The combination of a proper heat tape and sewer line insulation is usually enough to stop freeze-up but here are some additional tips for mobile home waste line freeze problems:
Question: what kind of heating tapes can be used on PVC plumbing drains?
I have a PVC drain line for my water softener that goes outside. When it got very cold two winters ago, the drain line froze and it backed up into house. The drain line lays on the ground. I went to a local store to look for heat tape and they specifically stated not to use on drain lines. Is there some type of tape I could use that would be safe, and how should it be installed? - Don Corbett 9/30/11
A concern with heat tapes on plastic piping is that it may damage the pipes. And if your water softener drain is simply draining onto the ground surface, that is an improper and illegal disposition of wastewater in just about every jurisdiction. Unfortunately the proper fix is costly: reroute drainage to a drywell or other approved drainage destination.
If you use drain piping of sufficient diameter and proper slope, even exposed to cold temperatures the drainage will generally not freeze up in normal use. More help on avoiding freezing piping is at WINTERIZE A BUILDING.
Heating tapes and cables can be installed on PVC supply and drain piping provided you choose the right kind of heating tape or cable and that you follow the manufacturer's instructions. Details are in the article above at HEAT TAPES to AVOID FROZEN PIPES.
Question: is it OK for the water line to run atop a concrete slab or should it be under ground?
In a mobile home in N.E. should the water supply line be placed on top of the concrete slap for 30 feet or more. Would that be up to code? Should the line from the street be 4 feet under ground to within 6 feet of the hot water heater? - Lee Broad 1/23/12
Lee, if you are describing a water line atop the rat slab beneath a mobile home, there are a couple of hazards including freezing and also movement-caused abrasion and leakage. If the line is supported off of the slab by blocks and insulated you may be OK, else you'll need to add frost protection as well. Heating cables (see advice above in this article) are readily available in lengths up to 60 ft. so you won't have trouble finding one long enough. Don't buy one longer than you need and be sure it is connected according to the manufacturer's instructions.
Question: what is the best way to heat a well pit?
what is the best way to heat a well pit - Jim, 10/18/2012
A well pit is intended to protect its contents, well head, piping, possibly even a water tank and pump from freezing by its depth below ground. If you have to add heat then the pit was perhaps not properly constructed, not deep enough, or left uncovered.
That griping done, you could consider adding a small electric heater; We have also used a simple light bulb in a small, closed well pit. The risk of course is that electricity fails or the bulb burns out. That's why I think a small oil-filled electric heater is probably more safe. Be sure that ALL electrical components in a well pit are protected from water, including the occasional well pit flood. - See more at: http://inspectapedia.com/plumbing/Pipe_Heat_Add_Points.htm#sthash.Nk3hbfK8.dpuf.
Question: tips on how to use a circulating pump to prevent water from freezing
Great suggestions - good article!
Beside insulating pipes from cold weather, or trying to use heat tape, a very effective way of protecting pipes from freezing is to introduce a circulating pump into the water system. By installing a circulation system, the water from the 'hot' side of the system gets sent to the 'cold' water line. This greatly reduces the possibility of water pipes freezing because the water temperature never reaches the critical freezing point.
The best circulation system on the market that I've seen is available at http://avoidfrozenpipes.com/ It is the only circulating pump I've seen that doesn't need electricity to run. It can be installed anywhere in the water system, and save hundreds if not thousands of dollars in home repairs if frozen pipes burst from water expansion.
That's my two cents; I hope it helps! - Vincent 1/21/2013
Thanks so much Vincent. We welcome content critique & suggestions for InspectApedia articles. Working together we are smarter than any individual. - Daniel
Questions & answers or comments about how & where to add heat as a means to protect pipes from freezing. .
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References