Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
BACKDRAFTING HEATING EQUIPMENT
DRAIN & SEWER PIPING
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
GAS DETECTION INSTRUMENTS
GAS EXPOSURE EFFECTS, TOXIC
GAS EXPOSURE LIMITS & STANDARDS
GAS FIRED WATER HEATERS
GAS LP & NATURAL GAS SAFETY HAZARDS
GAS PRESSURES LP vs NATURAL GAS
GAS PIPING, VALVES, CONTROLS
GAS BTUH, CUBIC FEET & ENERGY
GAS CONVERSION LP-NATURAL GAS
GAS FLAME & NOISE DEFECTS
GAS IGNITER DEFECTS & REPAIRS
GAS LEAK DETECTION, LP / NG
GAS LIGHTING, PIPES, FIXTURES
GAS PIPING DEFECTS
GAS REGULATORS for APPLIANCES
GAS REGULATORS for LP TANKS
GAS REGLATORS, TWO STAGE
GAS SHUTOFF VALVES
LP / PROPANE GAS TANKS
GAS LP & NATURAL GAS SAFETY HAZARDS
LP & Natural Gas Pressures
METHANE GAS SOURCES
Natural Gas Combustion Products
SPILL SWITCH, FLUE GAS DETECTOR
TYPES OF FUEL GAS SOURCE
MANUALS & PARTS GUIDES - HVAC
METHANE GAS SOURCES
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS, SEPTIC or SEWER
ODORS, SULPHUR SMELL SOURCES
OIL TANK PIPING & PIPING DEFECTS
PIPING IN buildings, Clogs Leaks Types
SEWER GAS ODORS
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
Working or antique or abandoned gas piping & fixtures:
This article describes how to recognize & evaluate the safety of antique gas fixtures and piping that may be found in historic homes or other older buildings. Gas piping in older buildings may have been cut-off from its source, re-used for electical wiring, or, surprise, antique gas piping is sometimes found still connected and "live"!.
Here we provide descriptions and photographs of unsafe gas piping, indications of unsafe or improperly operating gas appliances, gas meters, and other gas installation defects are provided.This document series on inspecting gas piping in buildings also provides free sample draft home inspection report language for reporting defects in oil and gas piping at residential properties.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Watch out: improper installation and even improper inspection and testing methods involving natural or "LP" gas can involve dangerous conditions and risk fire or explosion. If you smell gas you should leave the building immediately and should do so without doing anything that could create a spark such as operating a light switch or telephone. From a safe location, call your gas company's emergency line and/or your fire department.
Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution. Also see How to Report Defects in Oil Piping. NOTICE: while example report language is provided here, reproduction of this or any of our web pages or their contents at other websites or in printed documents for sale is prohibited.
Evaluating old gas lighting and other gas fixtures and fittings in older homes. It may be possible to make safe use of gas lighting in homes, both indoors and out, provided that the piping and fixtures have been installed according to contemporary building codes and that the piping and fixtures are in good condition.
But here we address the discovery of antique gas lights and piping in homes. Generally such fixtures and pipes should be considered a safety hazard, unless the system has been thoroughly inspected and brought to modern safety standards.
Our photo (left) and the next wall-mounted antique gas-light shown below illustrates an intact wall lighting sconce located in the Samuel Morse Home in Poughkeepsie, NY.
The photographs of various antique and even historic gas lights as well as remains of wall-mounted gas lights in other older buildings found in this article are a reminder that a building owner or her home inspector should never assume that old gas lines in a building are no longer connected to a gas source.
The photo at left shows another type of wall mounted gas light, also in the Samuel Morse historic homestead in Poughkeepsie, NY.
While the gas piping routes in some older Victorian homes have often been converted to use for electrical wiring, often we've been surprised to find that supposedly long-abandoned gas fixtures, pipes, and fittings, are actually still active, and potentially dangerous.
These photographs show still-active gas-lighting piping in homes built around 1900, with the gas fittings still active nearly 100 years later! A child pulling on the towel on that funny "towel rack" could have resulted in a catastrophe.
Old or Abandoned Gas Piping & Fixtures: safety warnings
Heating equipment which the inspector (or building occupant or manager) judges to be an immediate life safety hazard should be shut down and appropriate emergency services called.
See GAS LEAK DETECTION, LP / NG for leak detection procedures and alternatives.
Other LP & Natural Gas Home Safety recommendations
Continue reading at GAS LP & NATURAL GAS SAFETY HAZARDS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about gas piping in antique or other old buildings: gas piping, gas lighting & other gas fixtures in historic homes.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References