Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
ACCURACY vs PRECISION of MEASUREMENTS
AIR CLEANER PURIFIER TYPES
AIR LEAK DETECTION TOOLS
AIR POLLUTANTS, COMMON INDOOR
AIR QUALITY IMPROVEMENT STRATEGIES
ANIMAL or URINE ODOR SOURCE DETECTION
BACKDRAFTING HEATING EQUIPMENT
BIBLIOGAPHY for ENVIRONMENTAL HEALTH, MOLD, IAQ
BIOGAS PRODUCTION & USE
BLOWER DOORS & AIR INFILTRATION
BOOKSTORE - ENVIRONMENTAL
BUILDING SAFETY HAZARDS GUIDE
CARPETING & INDOOR AIR QUALITY
CHINESE DRYWALL HAZARDS
CHLORINE IN DRINKING WATER
COMBUSTION PRODUCTS & IAQ
COMBUSTION GASES & PARTICLE HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
CPSC Indoor Air Pollution Book Online Copy
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DUST SAMPLING PROCEDURE
EMERGENCY RESPONSE, IAQ, GAS, MOLD
ENVIRO-SCARE - PUBLIC FEAR CYCLES
ENDOCRINE DISRUPTERS at BUILDINGS
Fireplaces & Woodstove Contaminants
FLAME COLOR, BLUE vs YELLOW COMBUSTION
Formaldehyde Gas Hazard Reduction
GAS DETECTION INSTRUMENTS
GAS LP & NATURAL GAS SAFETY HAZARDS
GAS LP & Natural Gas Pressures
HEATING OIL EXPOSURE HAZARDS, LIMITS
HOUSE DUST ANALYSIS
HOUSE DUST COMPONENTS
HUMIDITY CONTROL & TARGETS INDOORS
HYDROGEN SULFIDE GAS
Indoor Air Pollution Book Online CPSC
INDOOR AIR QUALITY & HOUSE TIGHTNESS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
LP & Natural Gas Pressures
GAS LP & NATURAL GAS SAFETY HAZARDS
MOLD ODORS, MUSTY SMELLS
MSDS MATERIAL SAFETY DATA SHEETS
MVOCs & MOLDY MUSTY ODORS
Museum Artifact Preservation
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
OXYGEN - O2
PARTICLE SIZES & IAQ
PESTICIDE EXPOSURE HAZARDS
PLASTIC ODORS-SCREENS, SIDING
PLUMBING SYSTEM ODORS
PVC - VINYL BUILDING PRODUCTS
RADON HAZARD TESTS & MITIGATION
METHANE GAS HAZARDS
SEPTIC SYSTEM ODORS
SMELL PATCH TEST to Track Down Odors
SULPHUR & SEWER GAS SMELL SOURCES
UFFI UREA FORMALDEHYDE FOAM INSULATION
URETHANE FOAM Deterioration, Outgassing
VAPOR CONDENSATION & BUILDING SHEATHING
VENTILATION in BUILDINGS
VINYL SIDING or WINDOW PLASTIC ODORS
VOCs VOLATILE ORGANIC COMPOUNDS
WATER ODORS, CAUSE CURE
This article lists the components in the flue gas or exhaust gas produced by the combustion of natural gas (and similarly propane gas or liquefied natural gas (LNG) such as when gas is burned in a home heating appliance like a water heater or a heating boiler.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Natural gas, currently supplying about 22% of energy in the U.S., has been used as a fuel since its development by the Chinese more than 2500 years ago.
Today it is used in buildings for heating as well as for production of hot water and in some cases even for cooling. In industry gas is used as a heating fuel for many processes.
In the U.S. the first natural gas well was dug in Fredonia New York in 1821.
Perfect combustion of natural gas (Methane – CH4) produces only CO2 and water vapor The equation for the combustion of natural gas is CH4[g] + 2 O2[g] -> CO2[g] + 2 H2O[l] + 891 kJ
But this is a simplification since natural gas is not pure. Natural gas, as it is produced from a gas well, also contains ethane C2H6, propane C3H8, butaneC4H10, carbon dioxideCO2, nitrogen (N), helium (He), and hydrogen sulfide H2S.
Before it is distributed to consumers, ethane, propane, butane are removed from natural gas. Small quantities of other molecules may be produced during natural gas combustion than those in the “pure” case we listed above.
In the table shown here we list the relative quantities of combustion products produced when burning natural gas. the numbers are pounds produced per million Btus of NG burned:
Table of Combustion & Flue Gas Products in Natural Gas
-- from various information sources on natural gas. We anticipate that the combustion products from burning liquefied natural gas LNG and propane (C3H8) will be similar.
Normal natural gas combustion: In a practical sense in a home or office building if we are considering a small natural gas appliance such as a water heater, and provided that the equipment and its flue vent connector and chimney area all working correctly and that there is adequate combustion air, once the equipment has warmed up and draft is established, the system is producing CO2 and H2O (in the form of water vapor) and not much else that will be detected by the building occupants.
Imperfect (and unsafe) natural gas combustion, short on Oxygen from too little combustion air or from a chimney problem, will produce CO as well as nitrogen oxides (NOx), organic particulate material, and polynuclear aromatic hydrocarbons (PAH). Incomplete combustion of natural gas may also release un-burned methane CH4 itself.
The reason for the initial versus stabilized- burn CO level spec is that until the appliance heats up combustion is incomplete and higher levels of CO are produced.
The percentage makeup in flue gas from a gas fired water heater will probably not be given as a general overall standard in many references and by most onsite HVAC technicians or inspectors except in theoretical combustion instances because of the wide variability in equipment, vents, and chimneys.
Continue reading at GAS DETECTION INSTRUMENTS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: exposure limits for kerosene & diesel
(Jan 12, 2012) einar gislason said:
what is the allowable breathable levels of both kerosene and diesel when used in a space heater
Einar the exposure limits you seek are described at HEATING OIL EXPOSURE HAZARDS, LIMITS where we include health effects, exposure limits, and MSDS data for heating oil - which is essentially the same as diesel fuel. Because both Benzene and Kerosene are likley to be present together, typically an MSDS gives exposure limits for both as we excerpt from Irving Oil's Kerosene MSDS sheet (citation below):
The ACGIH-TLV exposure limit for Benzene is specified as:
The OSHA-PEL for Benzene is specified as
The ACGIG-TLV exposure limit for Kerosene is specified as:
An OSHA PEL for kerosene is not established.
Many oil companies and others provide an MSDS for Kerosene. An example from Irving Oil is given in the preceding link. - Retrieved 8/19/14 original source https://irvingoil.com/files/03500_Kerosene_-_English.pdf
Question: can an electric water heater produce methane gas?
Hello, I was reading your website about possible odors associated with systems in the home. Is it possible for an electric water heater to produce a methane gas? I have recently verified readings from a hot water line that had methane readings in the flammable ranges. Any input or information would be appreciated. Thanks, R.T.
Reply: an electric water heater does not naturally produce methane gas but there can be other methane gas sources in a building water supply and other odor sources in a water heater or in water supply
A competent onsite inspection by an expert usually finds additional clues that help accurately diagnose a problem with the water heater or with gas piping in the building, but none of these ought to involve methane induced into the water heater tank interior from the appliance or its fuel piping. And simply heating water does not innately produce methane gas.
An electric, or oil fired water heater does not produce methane gas (CH4). A gas fired water heater indeed uses a fuel gas that includes methane plus an odorant. However a gas-fired water heater might leak LP or natural gas into the air but as there is no under-water gas piping at a conventional water heater I'm doubtful that the fuel gas would be likely to leak directly into the water supply or hot water tank from the heater itself or its gas piping.
Watch out: in some public and private well water supplies methane gas from mining, natural gas drilling and removal from the earth, or other sources may result in high levels of methane gas entering well water.
We have moved the details of this discussion to METHANE GAS SOURCES
Watch out: If you do have methane gas in your water supply it could be dangerous, presenting a possible explosion hazard. But if methane is in your water supply, it ought to be present in both hot and cold water, though due to the temperature differences it might be more obvious in one than the other.
Questions & answers or comments about gas fuels, methane gas leaks, odors, and hazards, and about gas fired heating appliances.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References