Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
ODORS GASES SMELLS, DIAGNOSIS & CURE
AIR CLEANER PURIFIER TYPES
AIR POLLUTANTS, COMMON INDOOR
AIR QUALITY IMPROVEMENT STRATEGIES
ANIMAL ODORS IN buildings
BACKDRAFTING HEATING EQUIPMENT
BOOK MOLD, Moldy Book Cleaning
CAR MOLD CONTAMINATION
CARPETING & INDOOR AIR QUALITY
CAT DANDER in buildings
CHINESE DRYWALL HAZARDS
CHEMICAL CONTAMINANTS in WATER
CHLORINE IN DRINKING WATER
COMBUSTION GASES & PARTICLE HAZARDS
DIRT FLOOR MOLD CONTAMINATION
DUCT SYSTEM & DUCT DEFECTS
EMERGENCY RESPONSE, IAQ, GAS, MOLD
Fireplaces & Woodstove Contaminants
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
GASES, EXPOSURE, TESTING
GAS DETECTION INSTRUMENTS
GAS EXPOSURE LIMITS & STANDARDS
GLUES ADHESIVES, EXTERIOR CONSTRUCTION
HEATING OIL EXPOSURE HAZARDS, LIMITS
INDOOR AIR HAZARDS TABLE
INDOOR AIR QUALITY & HOUSE TIGHTNESS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
LIGHT, GUIDE to FORENSIC USE
LP & Natural Gas Safety Hazards
METHANE GAS SOURCES
MILDEW in BUILDINGS ?
MOISTURE CONTROL in BUILDINGS
MOLD ACTION GUIDE - WHAT TO DO ABOUT MOLD
MOLD or INDOOR AIR EMERGENCY RESPONSE
MOLD TEST KITS
MOTHS, MOTHBALL ODORS
MSDS Material Safety Data Sheets
MVOCs & MOLDY MUSTY ODORS
ODORS GASES SMELLS, DIAGNOSIS & CURE
OIL, HEATING, EXPOSURE HAZARDS, LIMITS
OIL HEAT ODORS
OIL TANK LEAK ODORS
OUTHOUSES & LATRINES
OZONE for MOLD OR ODORS
PAINTS & COATINGS ODORS IN BUILDINGS
Pesticide Exposure Hazards
PET ALLERGENS / PET DANDER
PET STAINS on FLOORS
PET STAINS on WALLS
PLASTIC ODORS-SCREENS, SIDING
PLUMBING SYSTEM ODORS
SEPTIC SYSTEM ODORS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP, WHAT TO DO
SEWER GAS ODORS
SMELL PATCH TEST to Track Down Odors
STAINS on & in BUILDINGS, CAUSES & CURES
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIN DIAGNOSIS on BUILDING INTERIORS
SULPHUR & SEWER GAS SMELL SOURCES
THERMAL IMAGING, THERMOGRAPHY
THERMAL IMAGING MOLD SCANS
TRAPPED MOLD BETWEEN WOOD SURFACES
Urea Formaldehyde Foam Insulation UFFI
URETHANE FOAM Deterioration, Outgassing
UV LIGHT BLACK LIGHT USES
VENTILATION in BUILDINGS
VINYL CHLORIDE HEALTH INFO
VINYL Siding or PLASTIC Window ODORS
Volatile Organic Compounds VOCs
WATER ODORS, CAUSE CURE
WATER TEST CHOICES & WATER TEST FEES
WATER TREATMENT EQUIPMENT CHOICES
Floor drain odors & smell troubleshooting: this article explains how to track down and cure a sewer gas odors that appear to be due to basement or crawl space floor drain or drain trap problems. We describe the likely sources of sewer gas or septic smells that seem to come from a floor drain, and we explain how to complete the diagnosis & cure of these odor problems. The sketch of a plumbing trap primer system shown at page top was provided courtesy of Carson Dunlop Associates.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Our photo at left shows use of a floor drain that may be an odor source. Draining air conditioning or heat pump condensate in this manner can solve two problems at once. Avoiding a dry plumbing trap and disposing of A/C or heat pump condensate.
For a case history of diagnosing sewer odors due to a broken under-floor sewer line, see CAST IRON DRAIN LEAK, ODOR, REPAIR. Also see CAST IRON DRAIN PIPING. See PLUMBING SYSTEM ODORS to start diagnosing the broad category of smells from plumbing system drains. Other types of building piping systems are discussed at GAS PIPING, VALVES, CONTROLS and at OIL TANK PIPING DEFECTS. Also see ODORS & SMELLS DIAGNOSIS & CURE for procedures to diagnose and cure all kinds of odors in and around buildings.
The articles at this website will answer most questions about water supply & drain piping, wells, & water tanks as well as many other building plumbing system inspection or defect topics. Reproduction of this web page electronically at other websites is prohibited.
I am having a heck of a time finding where the septic odor is coming from. We have a 3 story house on a septic tank and drain field.
The odor seems to be strongest and most often present in a mechanical room in the basement.
The only plumbing in the room is a floor drain [photo at left from reader]. No other drains are under the concrete slab. I know because I built the house.
I suspect that drain, but the water level in the trap seems to be full and I even sent a metal feeler down to make sure the bend in the trap was below the water level.
The concrete floor does have settling cracks. Is it possible that the plastic drain pipe could be slightly cracked or loose glue joint down stream from the trap, caused by the settling concrete?
Would plugging the 4 inch drain just outside the house and filling the drain with water up to the top of the floor drain give enough pressure to any leaks thereby lowering the level of the water in the drain?
Assuming all the other drains downstairs are slightly higher than the specific drain in question.
[Photo at left (from reader) shows a portion of the drain-waste-vent DWV piping in this building.]
This house is 30 years old and this problem is about a year old.
This question is a tough especially with all the floors being finished with tile or carpet.
I was an electrical contractor so I do have tools and abilities for any of your suggestions, i.e.: shove a metal fish tape down the drains and then trace the tape to verify the drain path under the concrete slab.
Any help is appreciated. Thanks, - D.M.
Reply: Floor drain and trap odor diagnosis suggestions
Rooftop plumbing vent as odor cause
It would be uncommon for leaves to block a roof vent unless the vent projection above the rooftop were very short and the vent was covered with leaves (or snow). But we have indeed seen roof vent pipes blocked by frost if there is a shower or laundry or other source of hot water that sends a lot of steam up the vent in very cold weather, esp. if the vent is small in diameter - say under 2";
We have also found roof vents blocked by wasp nests, and once even a frog.
If you can safely examine the vent from rooftop without falling off due to snow or other slippery conditions, it's worth taking a look.
Other plumbing vent failures that send odors into buildings include a vent or drain line that is disconnected inside the building due to an unglued joint or broken drain line; These should show up as an odor or when you perform a pressure test of the vent line.
Of course if your floor drain piping is actually used to drain a plumbing fixture (such as a washing machine) and the drained fixture is more than 5' from any plumbing vent, then depending on what waste flows through that drain line, it could on occasion siphon water out of the trap and allow odors into the building. It is also possible to siphon water out of a remote but un-vented trap as waste passes down the joined drain line, but that problem would have been present from the time of original construction whereas your problem has just recently appeared. And you've confirmed that there is water in the basement floor trap so that's not our first suspicion.
Drain line under the floor as odor source
Indeed we have had cases of under-floor drain lines that were leaky, sending sewage odors into the building; that problem is more common when the under-floor drain is carrying sewage. See CAST IRON DRAIN LEAK, ODOR, REPAIR for an example.
If you have easy access to this same drain line from outdoors and can temporarily block the line at that point it would be a good diagnostic tool since you are sure that there is no other plumbing connected to this drain. If you block the line from outdoors (and at a point before it joints any other sewer piping) then if that's the odor source, the odor ought to stop.
If that step confirms that the line is the odor source, and presuming the building is new enough that your piping is plastic not cast iron under the floor, I'm guessing that the bad news is the line would have to be abandoned (sealed off outside) or dug up and replaced.
Before doing so it may be worth asking a plumber who has a drain line inspection camera to send that through the line to see what's going on, on the chance that you can find and dig up just a short section of line that is damaged or disconnected.
Floor drain trap as odor source
It is interesting that you found the floor trap filled with water. Often a floor drain whose only function is to catch on-floor flooding in a basement is so seldom used that its floor trap dries out and sewer gases pass backwards into the building.
We solve that problem either by pouring some mineral oil into the drain trap or installing a floor trap that includes a check valve designed specifically to prevent gases from passing backwards up the drain line and into the building.
When a building is more than a year old and the floor trap is always filled with water, and if we think that the drain line is never used, where is that water coming from?
Is that a clue that there is water under the building leaking into the trap (i.e. an open or broken drain)?
Other Possible Sources of Basement Sewer Odors
Additional floor drain or trap odor problem diagnostic questions:
Follow-up from reader about smelly basement floor drain
Whole drain is not 4 in…4 inch is a main drain with taps off of it under the slab. The floor drain in question is a 2 inch line and trap. All abs piping.
Drain in question is just for spillage as is the other one in a different room. The reason water is in the trap is because I diligently keep it full. Have thought of putting antifreeze, like a travel trailer uses, instead of mineral oil. But not until this is settled.
Check all roof vents this morning with a 1/4in metal fish tape. No restriction and a visual with flash light showed no problem. Also, the gas odor coming out seemed consistent at all four roof vents.
Since last writing, I did plug the 4 in drain just outside the home and then filled all the pipe under the slab until the water level was even with the top of the floor drains. I left it for 14 hours and the water level never changed. Therefore, I feel there is not a big leak under the slab. I suppose a real small leak might take more time to be apparent. An air test would be more accurate but would complicate plugging the pipe completely.
After plugging the 4 inch line, I aired out the house and no odor returned. This makes sense because all the lines leading to the septic tank were plugged with water.
Also, this morning I had the tank emptied. It probably could have gone another three years, but because of the problem, I had it cleaned anyway.
After careful review of when this intermittent problem occurs, It seems like the odor follows the draining of one particular bath tub. The tub was used for three consecutive days, and each of those days we had the odor. Is there any type of flushing action that can cause the odor getting through. Remember, this is a problem that occurs when it is cold out, not neccesarily freezing, and the problem started a year or so ago and we have been here for 20 years..I can’t even think of a place where a nail could have been put through a pipe. No one works on this house but me..
Included four pics; 1. The outside four inch clean out used to plug entire house drain 2. The suspect floor drain [see at top of this Q&A] 3. Misc. piping to suspect tub/lav/ toilet area on first floor, as seen from basement [see at top of this Q&A] 4. Outside vents, all were clear…
What can you tell me about a smoke test? I am looking into plugging all pipes and putting and doing an air pressure test. This would take the talk out of a leak but would not tell me where it is..ugh…
Frequently Asked Questions (FAQs) about finding & fixing the cause of odors coming from floor drains
Questions & answers or comments about how to track down and cure basement floor drain odors & smells.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.