How to Replace a Water Tank AVC - Air Volume Control Valve
Reader Question: Can I Replace a Round Diaphragm AVC with a Rectangular US Gauge Type 300L or 310WJ?
I was wondering where I could get a Rectangular Air Volume control with no copper tube – D.W.
U.S. Gauge makes rectangular type AVCs, as we illustrate above. So do some other companies.
Watch out: rectangular AVCs like the U.S. Gauge unit shown above and illustrated here from the company's product literature, incorporates a float inside the water tank. If you look closely at our photos you 'll see that the gauge mounts through a 1 1/4" diameter ANPT threaded pipe connection into the water tank.
Also the mounting location of the gauge has to be correct - if your tank tapping is in the wrong place on the water tank, the float may not function properly. Check your water tank to see if there is a tapping in the right location. And see the AVC product instructions and check with the manufacturer's customer service before trying this swap.
Watch out: also to be sure to order the proper air volume control model. For example the U.S. Gauge AVC Type 300L is designed for shallow well operation, and the U.S. Gauge Type 310WJ Air Volume Control is designed for deep well operation. These devices do not work in an identical fashion, so buying the wrong model for your well would be a mistake.
The shallow-well U.S. Gauge 300L AVC, for example, does not eliminate the tubing connecting the device to the water pump.
On this gauge, (photo at left, U.S. Gauge product literature), includes a brass fitting at the gauge under-side. You can see it in the bottom left of the photo at left.
That brass fitting is an air inlet valve that connects through a plastic (polyethylene) tube to a snifter valve that is mounted on the well pump itself.
Depending on the AVC float position and operation, the snifter is a one-way valve that allows air into the pump and thus into the incoming water supply and into the water pressure tank. When enough air is in the water tank the float responds and closes the air inlet valve. Quoting from US Gauge's Type 300L AVC installation instructions:
Shallow Well Operation - Type 300L: When the water level is high, the float, secured to a float
rod extending through a flexible dividing wall, opens an air
inlet valve in the body of the control. The air inlet valve is
connected through 48” long polyethylene tubing to a snifter
valve on the pump and has no direct connection into the
The snifter valve admits air into the pump but prevents
the water in the pump from escaping back through it. Air is
drawn into the pump through the air inlet valve, connecting
tubing and snifter valve and carried out with the water into
This operation continues until the volume of air
increases to the proper amount, at which time the float closes
the air inlet valve, shutting off the supply of air to the pump.
The optimum relationship between the volume of air and
water in the tank is thus maintained.
The deep-well U.S. Gauge Type 310WJ Air Volume Control, as we described and illustrated above at Rectangular Air Volume Controls, does not include this tubing connection for a snifter valve and its operation is a bit different. The Type 310WJ AVC for deep wells also uses a float inserted into the water tank interior. But there is no external fitting for a tubing connection.
A chamber inside the AVC uses an adjustable pressure relief valve to allow excess air to escape from the valve when the tank water level (and thus the float level) drops. That process explains the air volume control device "hiss" that we discuss at What is that Hissing Sound.
So if pressure in the tank exceeds the AVC pressure setting air is vented from the water tank. The device is adjustable between 15 and 40 psi, and is factory set to 25 psi. Quoting from US Gauge's Type 310WJ AVC installation instructions:
Deep Well Operation - Type 310WJ When there is an excess of air and the water level is low,
the float opens the main valve of the control, permitting air
to be vented to a chamber within the control. This chamber
contains an adjustable pressure relief valve which exhausts
the excess air to the atmosphere, providing the pressure in
the tank is higher than the relief valve setting.
As the float
rises with the increase in water level the main valve closes,
trapping the remaining volume of air in the tank. The optimum
relationship between the volume of air and water in the tank
is thus maintained.
How to Replace a Brady Air Volume Control - Brady AVCs
2016/02/22 peggy said:
How do you replace Brady air volumn control on water well?
Reply: Manufacturer's recommended steps when replacing a Brady AVC
Air volume control replacement is basically a bolt-on repair at the water pressure tank, once you've drained pressure and enough water from the tank that you don't get squirted during the removal and replacement. The new AVC will mount where the old one did, usually on the side of the water pressure tank.
Brady air volume controls are now distributed by Baker Water Systems Division 800-523-0224. Other contact information is given below. The company's product line includes repairable air volume controls that can be renovated using a factory-supplied repair kit.
See also AIR VOLUME CONTROL REPAIR
Or you can simply replace the entire device as it retails for less than $40. U.S.
You want to repair your AVC instead of replacing it, you'll need to find the part number cast into the body of your air volume control (such as AV30BLK or AV80IND) before buying a repair kit or replacement unit.
The following Brady AVC control installation suggestions are a direct quote from the manufacturer whose contact Information I'll give below
1. Check the system for leaks. Your Air Volume Control will not replenish enough air to overcome leaks in the system.
2. Make sure that the side of the control marked “tank side” is closest to the tank. The control will not function otherwise.
3. Your Brady Air Volume Control should be installed into the 1/4” or 3/8” N.P.T. tank port above and closest to the discharge port as shown below.
4. Connecting the tubing (vacuum line) to the suction port located at the center of the control and the suction port on the pump. You Air Volume
Control works on a vacuum principle, so make sure that the tubing connected to the pump is clear and not obstructed or kinked.
5. A snug fit is all that is necessary for all connections. Do not over tighten!
6. For best results and easy installation, use the Brady UK-1 Installation kit.
Contact the manufacturer if you need parts, the installation kit, or more help:
Watch out: it can be confusing tracking down the manufacturer or vendor of parts used in water systems as companys can be bought out and names change. The Brady Products website redirects to Baker Water Systems Division, http://www.bakerwatersystems.com/ Tel: 800-523-0224 [main number] and when we look at that company's contact page we find Baker Manufacturing in Evansville WI Tel: 800-356-5130 and also Campbell Manufacturing in Bechtelsville PA 6
10-367-2107. Call the manufacturer closest to you.
Watch out: yet another Brady company located in Milwaukee WI USA is not the manufacturer of this device. They make medical supplies.
Brady air volume controls controls are sold at plumbing suppliers and at building supply stores such as Lowes or Home Depot and cost about $35. U.S.
More Brady AVC sources are given at AIR VOLUME CONTROL REPAIR
Continue reading at AIR VOLUME CONTROLS, GET RID OF or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 U.S. Gauge Special Application Gauges: Type 300L and 310WJ Air Volume Controls, product description, 2002, Ametek® Inc, U.S. Gauge, 820 Pennsylvania Blvd., Feasterville PA 19053, USA, Tel: 215-355-6900 www.ametekusg.com Customer Service: 863-534-1504, web search 03/23/2011, original source: http://www.jlwinstruments.com/PDF_files/D17_MODEL300-310.PDF Sadly this URL now reroutes to a dead end
 AMTEK, 900 Clymer Avenue 8600 Somerset Drive
Sellersville, PA 18960 U.S.A. or Customer Service at AMTEK, Largo, FL 33773 U.S.A.Sales/Technical Support: 215-257-6531, Customer Service: 727-536-7831, Website: www.amtekusg.com, Email US Gauge at firstname.lastname@example.org.
 flosource.com/ provides links to some US Gauge air volume control products installation and adjustment
Rasmussen Well Drilling, Inc., 1793 Hwy 61, Two Harbors MN. Jeremy Rasmussen provides third generation well drilling and plumbing services on the North Shore of Lake Superior. Photos by DJF. Tel 218-834-3387. Email: email@example.com
We serve the north Shore – Lake, Cook, St. Louis, Carlton and Pine counties, including Duluth, Grand Marais, Clouqet, Carlton, Finland, Isabella, Silver Bay, Grand Portage, Saginaw, and everywhere in Northeastern Minnesota.
 Dill Air Controls Products, 1500 Williamsboro St., PO Box 159, Oxford, NC 27565, Tel: (919) 692‐2300, Website: http://dillaircontrols.com
Smart Tank, Installation Instructions, Flexcon Industries, 300 Pond St., Randolph MA 02368, www.flexconind.com, Tel: 800-527-0030 - web search 07/24/2010, original source: http://www.flexconind.com/pdf/st_install.pdf [Copy on file as /water/Smart_Tank_Flexcon.pdf ] -
Typical Shallow Well One Line Jet Pump Installation, Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf, [Copy on file as /water/Jet_Pump_Grove_Elect_Jet_Pumps.pdf ] -
Typical Deep Well Two Line Jet Pump Installation, Grove Electric, G&G Electric & Plumbing, 1900 NE 78th St., Suite 101, Vancouver WA 98665 www.grovelectric.com - web search -7/15/2010 original source: http://www.groverelectric.com/howto/38_Typical%20Jet%20Pump%20Installation.pdf, [Copy on file as /water/Jet_Pump_Grove_Elect.pdf ] - Cooperative Extension, School of Forest Resources, web search 07/24/2010, original source: http://pubs.cas.psu.edu/FreePubs/pdfs/XH0002.pdf
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones