Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AFUE DEFINITION, RATINGS
AGE of CHIMNEYS & FIREPLACES
AGE of AIR CONDITIONERS & HEAT PUMPS
AGE of HEATERS, BOILERS, FURNACES
AIR CONDITIONING & HEAT PUMP SYSTEMS
AIR FILTERS for HVAC SYSTEMS
AIR HANDLER / BLOWER UNITS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
ANODES & DIP TUBES on WATER HEATERS
ANTIFREEZE for BOILERS
ANTI SCALD VALVES
APPLIANCE EFFICIENCY RATINGS
ASBESTOS IDENTIFICATION IN buildings
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BACKFLOW PREVENTER, HEATER WATER FEEDER
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BIOGAS PRODUCTION & USE
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BLUE vs YELLOW COMBUSTION FLAMES
BOILER CHEMICAL TREATMENTS
BOILER COMPONENTS & PARTS
BOILER CONTROLS & SWITCHES
BOILER LEAKS CORROSION STAINS
BOILER LEAKS, HOW TO LOCATE
BOILER NOISE SMOKE ODORS
BOILER OPERATING PROBLEMS
BOILER OPERATING STEPS
BOILER PRESSURE & TEMPERATURE SETTINGS
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
BUILDING SAFETY HAZARDS GUIDE
CAPACITORS for HARD STARTING MOTORS
CARBON DIOXIDE - CO2
CARBON MONOXIDE - CO
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CHIMNEYS & Flues - Asbestos Transite Pipe
CIRCULATOR PUMPS & RELAYS
COOL OFF HEAT, Thermostat Switch
COMBUSTION AIR for TIGHT buildings
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
COMPLETE COMBUSTION, Stoichiometric
CREOSOTE FIRE HAZARDS
CONDENSING BOILERS/FURNACES DAMAGE
CONVECTOR HEATERS - HYDRONIC COILS
DEFINITION of Heating & Cooling Terms
DEFINITIONS of ELECTRICAL TERMS
DEFINITIONS: OIL PIPING CONTROLS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DIRECTORY of OIL TANK EXPERTS
DRAFT HOODS - gas fired
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
DUST, HVAC CONTAMINATION STUDY
DUST SAMPLING PROCEDURE
ELECTRIC HEAT, DIAGNOSIS, REPAIR
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRICAL POWER SWITCH FOR HEAT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON Thermostat Switch
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN LIMIT SWITCH
FILTERS, AIR for HVAC SYSTEMS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FIREPLACES & HEARTHS
FLAME COLOR, BLUE vs YELLOW COMBUSTION
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
FLUE VENT CONNECTORS
FREEZE-PROOF A BUILDING
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
FURNACE CONTROLS & SWITCHES
FURNACE HEAT EXCHANGER LEAKS
FURNACE OPERATION DETAILS
FURNACE OPERATING TEMPERATURES
GALVANIC SCALE & METAL CORROSION
GAS BURNER Flame & Noise Defects
GAS FIRED WATER HEATERS
GAS PIPING, VALVES, CONTROLS
GAUGES ON HEATING EQUIPMENT
GEOTHERMAL HEATING SYSTEMS
HEAT EXCHANGER LEAK TEST
HEAT LOSS in BUILDINGS
HEAT LOSS DETECTION TOOLS
HEAT LOSS INDICATORS
HEAT LOSS PREVENTION PRIORITIES
HEAT LOSS R U & K VALUE CALCULATION
HEAT PUMPS, DIAGNOSIS, REPAIR
HEAT TAPES & CABLES on Roofs for Ice Dams
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING LOSS DIAGNOSIS-BOILERS
HEATING LOSS DIAGNOSIS-FURNACES
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SMALL LOADS
HEATING SYSTEM INSPECT DIAGNOSE REPAIR
HEATING SYSTEM NOISES
HEATING SYSTEM SERVICE FAQs
HEATING SYSTEM TYPES
HIGH EFFICIENCY BOILERS/FURNACES
HOT WATER HEATERS
HOT WATER IMPROVEMENT
HUMIDITY LEVEL TARGET
ICE DAM PREVENTION
INSULATION INSPECTION & IMPROVEMENT
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
LP & Natural Gas Safety Hazards
MANUALS & PARTS GUIDES - HVAC
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MIX VALVE SCALD PROTECTION, Best Practices
MOTOR OVERLOAD RESET SWITCH
Natural Gas Combustion
NO HEAT - BOILER
NO HEAT - FURNACE
NOISE / SOUND DIAGNOSIS & CURE
NOISE AIR CONDITIONER / HEAT PUMP
NOISE, DUCT VIBRATION DAMPENERS
NOISE, HEATING SYSTEMS
NOISE, WATER HEATER
ODORS & SMELLS DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL BURNER FUEL UNIT
OIL BURNER INSPECTION & REPAIR
OIL BURNER NOISE SMOKE ODORS
OIL BURNER NOZZLE & ELECTRODES
OIL BURNERS, RETENTION HEAD
OIL BURNER SOOT & PUFFBACKS
OIL FILTERS on HEATING EQUIPMENT
OIL FILTER MISSING
OIL FUEL TYPES & CHARACTERISTICS
OIL LINE CLOGGING FIX
OIL LINE QUICK STOP VALVES
OIL LINE SAFETY VALVES
OIL FILL PIPE LEAKS
OIL PUMP FUEL UNIT
OIL SPILL CLEANUP / PREVENTION
PLASTIC HEATER VENT
PULSE COMBUSTION HEATERS
PRESSURE REDUCING VALVES
PRESSURE REGULATOR, WATER
PUFFBACKS, OIL BURNER
PUMPS, PONY PUMPS
RADIANT HEAT Floor Mistakes to Avoid
RADIANT HEAT TEMPERATURES
RADIANT SLAB FLOORING CHOICES
RADIANT SLAB TUBING & FLUID CHOICES
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
Reset Switch - Heater Primary Control
Reset Switch Broken - Quick RepaiR
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY HAZARDS & INSPECTIONS
SAFETY HAZARDS GUIDE
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCHES - Flue Gas Detection
SPLIT SYSTEM AIR CONDITIONERS & HEAT PUMPS
STACK RELAY SWITCHES
STAIN DIAGNOSIS on BUILDING INTERIORS
STEAM HEATING SYSTEMS
Thermal Expansion Cracking of Brick
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL MASS in BUILDINGS
THERMAL TRACKING & HEAT LOSS
THERMOSTATS, HEATING / COOLING
THERMOSTATS, WATER HEATER
THERMOSTATIC EXPANSION VALVES
TRANSITE PIPE CHIMNEYS & FLUES
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WATER HEATER SAFETY
WATER HEATERS for HOME HEATING USE?
WATER HEATER NOISES
WATER HEATER SCALE - De-Liming Procedure
WATER HEATER SCALE PREVENTION
WATER SOFTENERS & CONDITIONERS
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
Leaky oil storage tank guidance for homeowners: issues surrounding leaking oil tanks, describes oil tank inspection and tank testing methods, suggests what a home owner or home inspector is obligated to do and report if an oil leak is found. This article also provides links to more detail about above ground and buried oil and other storage tanks.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Leaking oil tanks are not only a concern as contaminants of the water supply, but have become an increasing general environmental concern addressed by the DEC. Leaking commercial equipment and even simply-suspect equipment have been extremely costly to address.
Such burdens were never anticipated when the equipment was installed. While similar regulations pertaining to residential installations are scarce, this topic is of growing concern to home owners and home buyers. This article explores opinions and suggestions culled from news articles, discussions in several states and provinces, and discussions among several home inspectors. Also see OIL FILL PIPE LEAKS
Back in 1961, traditional heating oil tank installation procedures and standards recommended that all oil-storage tanks be buried outside wherever feasible. That was then. This is now.
New concerns about leakage and environmental pollution raise warnings about buried tanks. (Reference: Standards of the National Board of Fire Underwriters, as referenced by "Domestic and Commercial Oil Burners,", Charles H. Burkhardt, 1961, 3rd Ed., McGraw Hill Book Company, p. 172.)
In states where oil is used for residential space and water heaters, oil storage tanks are found buried outside (550 or 1080 gallons), outside above ground (often a 275-gallon "indoor" tank never intended for weather exposure), and inside (275 to 550 gallons maximum). Leaks at any of these tanks are at risk of causing environmental damage. In one older property we found an indoor tank leaking directly into the casing of a private well which was located in the basement!
New York State's Department of Environmental Conservation has been developing and enforcing a Petroleum Bulk Storage Program since the early 1980's. The goal of this program is to prevent leaks and spills of petroleum into the environment.
The New York State DEC estimates that there may be as many as 185,000 above and underground tanks storing petroleum in New York State subject to DEC regulations. Many of the tanks installed in the 1950's and 60's are bare steel and have a fifty percent chance of developing leaks today.
Currently the regulations apply to any facility with a combined capacity (liquid non-waste petroleum-based oils) which exceeds 1,100 gallons but is less than 400,000 gallons. No individual unregulated site can exceed 1,100 gallons; if the owner has a 1,000 gallon tank out by the garage and another 275 gallon tank for heating oil the regulations still apply. (Reference: Telephone conversation, author with Southern New York office of the Department of Environmental Conservation, DEC ca 1988.)
The regulations require that these facilities must be registered with the state. Depending on the size, age, location, and type of product stored the system may have to be upgraded or tested.
Frequency of Oil Storage Tank Leaks & Heating Oil Piping Leaks, Frequency of & Responding to Oil Leaks in Underground (Buried) Oil Storage Tanks - Residential
In New England for a two year period [1984-5] among customers who have buried heating oil tanks (16% of total customers or one buried oil tank per 10,000 oil heat customers) surveyors found an average of 1.7 tank leaks per thousand customers.
They also found 2.5 fuel line leaks per 1000 customers. (Fuel Oil and Oil Heat magazine, August 1985 p.18.)
A study of 500 underground fuel storage tanks was completed for the U.S. EPA and studied tanks on Long Island in New York in 1988. See "[Fuel Storage] Tank Corrosion Study", U.S. EPA report on gasoline and oil tank corrosion, November 1988. Of those 500 storage tanks about half were used for gasoline storage and about one fourth were used for home heating oil storage. But significantly the underground storage tank leak rate did not depend on what fuel was being stored.
More recent oil tank leak data scan be difficult to obtain, but the two articles below provide additional detail and specifics.
Usual Reasons for Oil Storage Tank Leaks - Rust Perforation, or Mechanical Damage / Corrosion at Piping
Underground fuel storage tanks usually fail from rust perforation due to several effects of water inside the tank including, in the case of heating oil, combination of water with sulphur in the fuel. External rust, unless very heavy, isn't highly correlated with internal rust. A new tank can involve significant expense.
Oil tank leaks are also caused by mechanical damage during installation,oil fill, vent, or supply piping errors, corrosive soil conditions, possibly by oil tank manufacturing defects, possibly indirectly, by weather conditions and in-tank condensation, and finally, by delivery of bad oil that contains excessive amounts of water.
The U.S. Department of Environmental Conservation has a program registering buried tanks at any site storing more than 1100 gallons of heating oil. Requirements for gas (auto fuel), or other fuels may be different. Eventually this concern may spread to smaller residential tanks. The concern is for leaks which contaminate the environment.
Oil storage tanks located where they may leak into a local waterway or into the water supply are a special environmental concerns.
Free publications are available from New York DEC regional offices: Petroleum Storage Regulations, How to Register Your Petroleum Storage Facility, Testing Underground Storage Tanks. A New York Help-line number is also available at 1-800-242-4351. Other state environmental regulators and their contact information are listed at OIL TANK REGULATIONS.
OIL TANK REGULATIONS gives details about the regulations which require reporting leaks and which govern oil tank abandonment
Oil Tank Leak Actual Environmental Impact & Leak Regulations: How are we affected by oil tank regulations?
On-site oil storage capacity can require tank registration: It is not unusual for a homeowner in the Northeastern U.S. to have installed additional storage tanks during the energy crisis of the 1970.
The added storage can bring the capacity of the property above the 1,100 gallon threshold and under the DEC regulations.
Many older homes with underground steel tanks have a good chance of developing a leak. We should provide our clients with this information. They can then make an informed decision to seek additional data and can also decide if testing should be performed.
What to Do if the Oil Tank is Leaking or Has Leaked? - What if an oil-fired heating tank or system is leaking? Oil Tank Leak Reporting Requirements
A leaking above ground oil tank may be discovered by simple visual observation. Leaks in buried tanks require special testing methods to locate and then test the tank for leaks or the soil for past leakage.
If you see a leaky oil tank or an oil spill: In New York (and in most other jurisdictions) anyone visually inspecting a petroleum storage tank of any size and finding that the system is leaking must report the leak to state environmental authorities. In New York State an oil leak must be reported within two hours to New York DEC. The New York Oil spill hotline is 1-800-457-6362. For other states see the state contact information listed at OIL TANK REGULATIONS.
We do not consider a minor drip onto the boiler room floor at a bad fitting a reportable leak for these purposes. (Beware! A small leak at an oil line can result in air entry into the system which can create other dangerous conditions at the equipment.)
Buried fuel tanks should be tested for amount of water present in tank bottom, and any water should be pumped out. Water corrodes the tank and leads to leaks. So if there is a lot of water in the tank we are more concerned about the chances that inside-tank corrosion is severe and there is a greater risk of tank leaks.
While we've found them lasting longer, a common life expectancy of buried oil tanks is 10-15 years. We do not have the same data for gas tanks. Life may be similar. If the tank is to remain in use, ask your fuel supplier about using an additive or other methods to help remove water.
A buried oil storage tank is installed at this property. Such components are not inspected (tested) during a home or building inspection unless specific prior test arrangements have been made for advice by an appropriate expert. More information on what to do about inspecting, testing, abandoning, or replacing oil tanks is available at the "Oil Tank Home Page" found at http://inspectapedia.com/oiltanks/Oil_Storage_Tanks.htm
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.