Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK ADVICE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
Causes of oil storage tank leaks: this article describes the causes of leaks in buried oil tanks and above ground oil storage tanks. Water may leak into oil storage tanks, or may enter tanks by other means; oil such as heating oil or fuel oil may leak out of oil storage tanks, risking a costly environmental problem.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
At least some of these causes of oil leaks or spills can be avoided by simple inspection and maintenance. The modest oil spill shown in this photo could have been avoided by properly sealing the brass oil line fittings at the bottom of the oil storage tank.
On an outdoor or buried oil tank a leak like this could go un-detected for many years and could form a more serious oil spill. This is a chapter of our "Heating Oil Underground & Above ground Oil Storage Tank Leaks, Testing, Problems & Solutions, Home Buyer's / Home Owner's Guide" which offers extensive free un-biased oil storage tank inspection and testing advice for property buyers and owners.
In-Tank corrosion: Underground fuel or heating oil storage tanks usually fail from rust perforation due to several effects of water inside the tank including, in the case of heating oil, combination of water with sulphur in the fuel, bacterial action, and other factors. External rust, unless very heavy, isn't highly correlated with internal rust. Leaks can occur due to tank damage or at piping connections.
Oil Tanks in Corrosive Soils: Oil storage tank leaks are more likely if a steel tank has been buried in corrosive soil or if the tank was damaged during installation, such as gouging it or bouncing it off of a rock as it was placed into a hole for burying.
Oil Tank Piping Leaks: Oil tank leaks may occur at buried piping connections as well.
Delivery Oil Spills: occur around the tank fill pipe and range from trivial to more extensive requiring soil removal and cleaning. These leaks are usually obvious at the ground surface around the oil tank or tank filler.
Inadequate fill or vent pipe diameter is blamed by some for leaks at buried or above ground oil tanks, asserting that because oil tanks are filled under pressure from the oil delivery pumper-truck, a corroded, damaged, or poorly-plumbed oil storage tank, or one with a too-small vent opening, may not withstand the pressure of the filling process.
Indoor oil spills during tank fill or later from a leaky oil tank range from trivial local cleanup and deodorizing efforts to very serious contamination problems if an oil tank bursts during oil delivery (which I suspect is rare) and on occasions when an indoor oil tank has been removed but someone (some fool) has left the oil filler pipe installed on the building, and when subsequently an oil delivery is mistakenly made through the filler pipe onto the empty basement or crawl space floor. This may sound crazy but it actually happens.
Home buyers should be sure to review OIL TANK LEAK TEST METHODS - Leaky Heating Oil Tanks - How Oil Tanks are Tested for Evidence Leaks, of Current or Previous Oil Spills and OIL TANK LEGAL ISSUES - Home Buyers and Home Owners Guide to Leaky Heating Oil Tanks - What to Do About & When to Report Oil Tank Leaks. Leaky Heating Oil Tanks.
Home owners who have old oil tanks above ground or any age oil tank below ground should also be sure to review OIL TANK ABANDONING PROCEDURE - Abandoning Commercial vs. Residential Underground Oil Storage Tanks (UST) - Procedures & Regulations A separate website addresses Septic Tanks.
What are the most-common sources of heating & fuel oil leaks in storage systems?
Question/Comment: researching statistical data on percentage of leaks in oil piping systems vs. leaks in oil storage tanks
I have worked for Shell in Brazil for several years, our petroleum regulatory agency has no data on it, and the state environmental regulatory agency has no data either.
If there is any link or peace of good information that you van lead me to it, I will appreciate the indication.
[Photo at left by InspectApedia.com illustrates leaky flange and brass-to-steel threaaded adapter at an oil burner]]
Concré-S Gestão Empresarial
Reply: some reasons for lack of early UST, AST, & fuel or heating oil piping leak data
Siento que eo não falo portugés Sr. Roberto but discussing in Ingléa, you raise a very interesting oil leak data question for which I have not seen nor been able to find satisfying data; but as I'm not an expert researcher on the topic, we can probably find some credible research - perhaps via Google Scholar or from other industry experts.
Previously I have reported on old data on oil tank leaks in the northeastern U.S. - that original data at the source (Fuel Oil & Oil Heat Magazine) subsequently seemed to disappear from public view though the publication itself continues. (OIL TANK LIFE)
As a property inspector alert for signs of possible UST or UST piping leaks over some years I developed some opinions about clues one might see that would raise a red flag and call further testing.
Because of the occasional very large oil spill cleanup costs involved, I and surely other field investigators encounter questionable situations (to put it politely) where a property owner or even an oil delivery company knew that leaks had occurred but didn't want to report that condition. At a few inspections the property owner basically threw us off of the land rather than permit us to even raise a question about the possibility of underground oil storage tanks, and in other cases clients reported that a seller would not permit leak or contamination testing.
Such oil contamination problems linger until the property is sold and the new buyer, being diligent, has some inspetions and tests performed. Some of my advice to property buyers is at OIL TANK, BURIED, ADVICE.
Follow-up & Discussion about the most-common sources of heating & fuel oil leaks in storage systems
R.A. -> D.F.
I have done some library search and found a very interesting study from the Missouri Petroleum Storage Tank Insurance Fund  (figure at left) and some additional data from Maryland ..
[Underpinning the data shown at left, the PSIF has insured 7093 oil storage tanks thorugh December 2012, has paid 1061 claims and has 421 outstanding. Ed. - Source MIssouri PSIF Facts & Finances Decembe 2012]
Those two studies make sense to me and are well aligned with my initial perception and personal experience.
Steel piping failures are harder to detect especially when we consider hand stick measuring systems and no automatic reconciliation procedures as it was by the eight´s.
In Brazil, we started moving from steel piping to HDPE in 1994 and by 1996 100% off all new installations were made off HDPE pipes, HDPE sumps, etc.
In general, we do not use pressure lines and we can consider that all of it is based on suctions systems (Tank/Pump System) with check valves.
Reply: DF -> R.A. - About the the most common UST, AST & Oil piping leak points,
Documented in more detail at OIL TANK LEAK POINTS it is my OPINION that
How do we prove that an oil tank is not leaking
The Missouri PSIF lists the following seven methods that the insurance fund will accept as evidence that a fuel/heating oil storage system is not leaking - listed just below, but because these tanks address different environments and kinds of potential leaks it's not clear to us that any single test is a complete guarantee about oil leaks:
- Source MIssouri PSIF Insuring Tanks 
Reply: R.A. -> DF: further research on & field experience reports of sources of fuel oil & heating oil leak points
I could not agree more with your opinion about why [heating oil] pipes leak. Back in 1989, when I started working with gas stations, USTs & heating/fuel oil pump installations, every piece of pipe was made of steel and all joints were threaded. The biggest steel length used at that time was 6 meters, and a typical connection line between UST and pump was about 10 meters[ - requiring multiple connections, where more connections means more leak risk].
As an average, we can consider that those connection lines had about 10 to 12 threaded connections (Joints, curves, elbows), or potential leak points; and as you very correctly said, mechanical stress and poorly made services caused most of the leaks.
At that time, those[oil piping, tank to appliance] connection lines had no check valves; instead we used foot valves, turning [oil] leak detection an enormous challenge considering that leaks were of a very small in instantaneous volume, constant in duration and random in location.
Statistics about leaking points are very hard to find and the reason is quite simple
Taknology was one of the first companies to start a successful local operation and they really did an outstanding job. Several others came and then the market exploded for the UST tightness test segment until late 1990´s.
By 2000 no more steel pipes were allowed in gas stations in Brazil and all old ones were under conversion to HDPE with suction systems, as it is today. I took part in this study - it was very informative. I will be continuing to dig around for data on oil leaks.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.