Leaky Oil Tank Filler or Vent Piping Repair Procedures
A diagnosis & repair guide for leaky oil storage tank fill or vent pipe leakage.
OIL FILL / VENT PIPE LEAKS - CONTENTS: What causes leaks at oil tank filler piping? What to do about leaky oil tank vent or filler piping; oil tank piping sources of leaks and oil odors or smells. Example of stopgap measures to control small oil tank fill and vent pipe leaks, permanent oil seepage leak repairs using epoxy, and proper oil tank piping repairs by re-making the pipe joints using a proper thread sealant.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Oil tank leaks at the fill or vent piping:
This article discusses the causes of leaks at oil tank fill or vent piping, what the leak and other hazards are, and what to do about oil tank piping leaks. We illustrate the places where both minor and more significant oil leaks can occur and we describe and illustrate how to repair those leaks using any of several methods ranging from trivial leak control (using a rag) to permanent leak repairs using an epoxy sealant or by re-making the pipe joints using an oil-resistant pipe thread joint sealant compound. .
Why Oil Storage Tank Piping Leaks & How to Fix Leaky Oil Storage Tank Filler or Vent Piping
This article discusses the causes & cures of leaks at the oil storage tank fill or vent pipes.
It is very common for there to be leakage around the oil filler pipe or vent pipe where they are connected to the top of an oil tank.
If the tank is buried these leaks may go undetected for some time, but on an above ground oil tank, inside or outside, the seepage is quickly visible and also can be smelled by most owners shortly after an oil delivery.
[Click to enlarge any image]
A separate article found at OIL LINE PIPING LEAKS discusses leaks in the smaller-diameter piping between the oil storage tank and the oil burner(s) it serves.
Diagnose the Causes of Oil Tank Fill or Vent Pipe Leaks
There are the reasons for the leakage:
Heating oil leak problems at oil tank fittings and pipe threads
The pipe threads (NPT) which are cut into an oil tank top tapping intended to accept the filler pipe or vent pipe are not precisely machined - they are a bit rough.
So are the threads on most large-diameter iron piping used to screw into the tapping.
Having installed a few of these, we can testify that it requires some very careful workmanship to make a leak-tight joint, combining cleaning of the threads, use of a high quality pipe dope rated for use on petroleum products, and turning the pipe into the tapping with sufficient force to seal it without damaging threads. In sum, often the connection is simply not very tight.
Heating oil leak problems due to pressurized oil storage tank fill procedures
In the mind of the installer, "What the hey, after all, the tank is just going to be at atmospheric pressure and filled by gravity from above, right?"
Wrong. Oil companies recognize that the time needed to complete an oil delivery is part of their profit or loss picture. Modern oil delivery trucks are designed to pump heating oil into the tank under pressure in order to speed the delivery process.
Photo at left: the oil delivery operator is demonstrating the correct and thoughtful way to fill an indoor or buried oil storage tank.
During oil tank filling the driver is listening to the tank whistle or tank alarm to avoid over-filling the tank - a common source of seepage and occasional heating oil or fuel oil spills. If the plumber or installer locates oil fill and vent pipes where they are difficult to access, don't expect such careful oil deliveries.
In fact most modern oil tank filler caps have a special fitting, often different from one oil company to the next, that permits the installer to "lock" the filler hose to the filler pipe during the fill-up procedure.
Usually an oil storage tank is filled right to its top during an oil delivery. This is because the way that the delivery driver knows that the tank is full is that s/he is (supposed to be) listening at the filler pipe. Tank fill or vent valves are (supposed to be) equipped with a whistling noisemaking device that indicates when the tank is full as the heating oil reaches the sounding device.
So if, unlike the driver in our photo above, the oil delivery pumper is not listening, say s/he went aside to smoke a cigarette or make a cell call, or if the tank top fittings are not absolutely tight, it is common to see some leakage around the tank top after a fill-up. We discuss details of oil tank pressures created during the oil tank filling operation.
See OIL TANK PRESSURE
Oil Tank Fill/Vent Pipe Leak Diagnosis
When and what should you do something about a leak at the top fittings of an oil tank?
Find the exact point of oil leakage: If you see oil on the floor, check the bottom of the tank, sides and welded seams,
and be sure to check the oil lines to the boiler and in particular, check the oil tank safety valve or other tank bottom fittings as
there are often leaks at these valves, as shown in this photograph.
Before addressing tank top filler pipe fittings as a leak source, make sure the oil leakage is from the top of the oil tank.
Other tank leaks such as at a seam or at perforations indicating a rusted tank need immediate evaluation by an expert, since these
could spell major trouble like a big and costly oil spill should the tank break or a fitting blow off.
Check for more than one leak point: Make sure that you know where the seepage is coming from. There may be separate spillage outside at the filler pipe from that occurring inside at the tank top or other fill or vent pipe fittings.
Check condition of oil piping: Make sure that the piping you're using is proper in material (steel is safer against rupture than plastic), and in diameter (2" or larger)
for both vent and fill pipes.
[The soldered copper fill and vent piping at the oil tank in the photo just above
was unusual and may not be permitted. At the top of this page, the silver-colored (galvanized steel) oil tank vent pipe in the tank is probably too small for modern tank fill methods.]
An older-installed small diameter vent or fill pipe [like the one shown at the page top photo] risks over pressuring the tank during fill-up, and risks a costly oil spill should an old tank or fill or vent line rupture. Ask your oil company to review the condition of the piping and the condition of the tank.
How to Repair Seepage or Small Oil Tank Fill or Vent Pipe Leaks
Small oil leaks at the heating oil storage tank: If the seepage is trivial in amount, say simply a light stain just a few inches around the tank top, clean it
off and live with it. Or re-make the joints when other plumbing work is planned.
(It's quite a bit of trouble to re-make these joints,
especially if the filler and vent piping have been routed through and cemented into a masonry wall.)
On our oil tank which recently "developed" a seep after our oil company bought a new, improved,
higher pumping pressure delivery truck, I cleaned the tank surface and tied a rag around the filler pipe at the top of the tank to try
intercepting the leak before it spreads over the tank and smells up our garage. I am doubtful that this will be effective long term but
changing the rag after each tank fill was easier than scrubbing off the whole side of the tank.
Watch out: a leaky oil tank gauge can be mistaken for an oil vent piping leak. Ultimately we traced this leak to seepage at the plastic-threaded oil tank gauge cover. The repair required making a new rubber gasket used at the bottom of the plastic oil tank gauge cover.
See OIL TANK GAUGE LEAK REPAIR
Subsequently we made a permanent repair by cleaning and sealing those threads using alcohol, then epoxy to stop the seepage without having to disassemble the piping - shown below.
Seal small to modest oil tank filler or vent pipe oil leaks using an epoxy sealant - shown below
How to Repair a Significant Oil Fill or Vent Pipe Leak
Significant oil piping leaks: If the seepage is enough to wet the tank or run down the whole tank and drip onto the floor (above) this is an
unacceptable condition that needs correction.
At above left the oil tank has been soaked by recurrent spills around oil piping connections and there is heating oil on the floor below the tank as well.
It's likely that the piping will have to be removed and (possibly new) piping installed.
I am doubtful that any "band-aid" approach like pushing epoxy putty or other sealers around the existing fitting is going to work. The surfaces will be rough, rusty, and oily.
Above and continuing with more photographs below we illustrate an oil tank whose fill and vent piping has been removed to permit tank relocation and re-piping. That is a convenient time to take extra care that the oil piping connections are well sealed when they are re-made. At above right we illustrate taking care to seal the oil vent or fill piping where it passes through the building wall, avoiding water entry, drafts, and insect damage by keeping these wall penetrations well-sealed.
Shown at above left is the outside view of the oil fill or vent pipe - well-sealed at the building wall: we caulked on both sides of the exterior wall sheathing in this installation.
If a reader or product manufacturer has a sealant that is actually effective in this application, dealing with the rust, oil, surface shapes, and fill pressure, I'll be glad to report on that product here. It would indeed be less trouble than re-piping the tank. Make sure the new piping is properly sealed and secured. If heating oil has been dripped on the floor, ask your oil company to clean it up and deodorize the area.
Repair significant oil tank fill or vent pipe leaks by disassembly, cleaning, and re-sealing the pipe joints using an oil-resistant pipe joint thread compound / sealant
Above we show re-made and properly-sealed oil fill and vent piping connections using an oil-resistant pipe joint thread compound. We have had good success sealing even the rough threaded pipe joints in large diameter oil tank fill and vent piping using "Brush-on/Blue Block", a pipe thread and gasket sealant compound provided by Hercules / Oatey Block pipe joint and gasket sealer. An 8-ounce container retails for less than $7.00 U.S.D. and is available from your local plumber supplier or building supply store such as Davies Hardware in Poughkeepsie, NY or at Home Depot and Loews building suppliers.
A similar Oatey product, Oatey SCS 15707 Hercules Block Greenish-Blue Thread and Gasket Sealant is also effective for sealing oil tank fill and vent pipes. Oatey's Great Blue® pipe joint sealing compound is also rated for use with diesel fuel oil, gasoline and many other liquids.
Actual oil spills:
If there is an actual oil spill, indoors or out, most state departments of environmental protection require that they be notified within 24 hours of the spill, an inspection is performed, and an expert specifies the amount of cleanup needed.
Remove un-used oil filler and vent piping: Never ever leave an oil and vent pipe installed at a home where the oil tank has been removed.
There is a risk that a mistaken oil delivery driver will attempt to deliver to the wrong pipes, flooding and ruining the home with heating oil.
Enclosing indoor oil tanks: Don't try simply enclosing a tank that is leaking - you prevent inspection of it, can miss a deteriorating condition, may interfere with service procedures for the heating equipment, and you won't control the odors. If an oil tank is going to be covered for aesthetic reasons, make the covering easily removable for inspection and service.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
(July 6, 2014) lee said:
I have a two line fuel oil furnace I can change to a single the one line is leaking is there a good product u can pump in like with a caulking gun ? I believe the leak is just below the top of the cement floor '
this question was answered when you posted it on other articles, Lee. Please post in just one place.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 Fuel Storage] Tank Corrosion Study, U.S. EPA report on gasoline and oil tank corrosion, James H. Pim, P.E., John M. Searing, Suffolk County DOHS, 15 Horseblock Place, Farmingville Long Island, NY 11728, November 1988, for the Office of Underground Storage Tanks, U.S. EPA. ATTN: David O'Brien. The report presents a study of 500 underground storage tanks spanning 24 February 1987 and September 1 1988 and summarizes earlier reports on this same study. Tank sizes ranged from 175 gallons to 50,000 gallons, and oil tank ages ranged from two years to 70 years old. All 500 oil storage tanks were constructed of welded steel, and 12 other tanks that were other than plain steel were also examined. Summary [with minor edits for clarity by DJF] Five hundred plain steel [underground fuel storage] tanks plus twelve corrosion protected [under ground oil] storage tanks were removed from the ground over an eighteen month period in Suffolk County, Long Island, New York. The oil tanks were examined carefully before disposal to gather statistics on the nature and extent of steel oil storage tank corrosion that had attacked them. Information was gathered on the number, type, location, and size of oil storage tank perforations [oil storage tank leak points] the general interior and exterior corrosion condition of the oil storage tank, soil, backfill, and groundwater conditions; the presence of leaked product [heating oil], and oil storage tank statistics such as tank volume, steel plate thickness, location, product [type of heating oil stored], tank age, etc. The statistics were compiled and compared, observations made, and conclusions developed. The major conclusions [were] summarized as follows:
Size is more important than age in predicting oil storage tank failures
In general, small tanks are much more likely to perforate than large tanks due to thinner walls found in smaller oil storage tanks
Compared to external corrosion, internal corrosion is insignificant [in the underground oil storage tanks examined - warning from DF: the opposite is probably the case regarding above ground storage tanks].
Fuel oil tanks are just as susceptible to leak perforation as gasoline tanks of the same size
Existing fuel storage tanks are in worse shape than is demonstrated by storage tank testing
Storage tanks to not always leak immediately on perforation
 Thanks to Arlene Puentes for for technical edits on oil tank leak advice- 12/2005. Arlene Puentes is a licensed home inspector, educator, and building failures researcher in Kingston, NY.
 "A Case Study of a Large Scale Precision [oil or fuel] Tank Testing Program", Diane H. Heck, Tetra Tech Richardson, Newark, Delaware, web search 4/27/12, original source: http://info.ngwa.org/GWOL/pdf/870143411.PDF, copy on file as /heating/OIl Tanks UST/Tank_Test_Heck_870143411.pdf Abstract:
In September 1986, a precision tank testing program was started to bring a major Maryland utility into compliance with the State of Maryland Oil Spill Control Regulations regarding underground storage tanks. This program involved the testing of over 240 tanks ranging in size from 300 gallons to 1,500 gallons located throughout the entire state of Maryland.
Analyses of the testing results revealed that 40% of the systems tested leaked. Piping leaks caused 82% of the testing failures and tank leaks caused the remaining 18%. Tank systems located in urban areas experienced a 50% testing failure rate, while tank systems located in rural areas experienced only a 25% failure rate. Leaks in tank systems in urban areas appear to be the result of structural loading and corrosion, affects [effects] absent in rural areas. The age, capacity, and usage of the tanks did not have a role in causing leaks either in the piping or the tank.
 Fuel Oil and Oil Heat Magazine, August 1985 p.18. Fuel Oil & Oil Heating Magazine, 3621 Hill Rd., Parsippany, NJ 07054, 973-331-9545
 Standards of the National Board of Fire Underwriters, as referenced by "Domestic and Commercial Oil Burners,", Charles H. Burkhardt, 1961, 3rd Ed., McGraw Hill Book Company, p. 172
 NFPA - the National Fire Protection Association can be found online at www.nfpa.org
 "The Interim Prohibition Guidance for Design and Installation of Underground Oil Storage Tanks", U.S. EPA, EPA/530-SW-85203, Office of Underground Storage Tanks, Washington D.C.
 US EPA "How do you Properly Close a UST?" is summarized at epa.gov/OUST/fsprevnt.htm These details for temporary and permanent closing of underground oil storage tanks are provided by the US EPA as well.
 "How do you choose the right tank testing method?", Cynthia Johnson, Fuel Oil & Oil Heat Magazine, November 1995
 National Association of Oil Heat Service Managers, PO Box 380, Elmwood Park, NJ 07407
 "Homeowners Guide to Fuel Storage," Agway Energy Products, Verbank, NY, November 1990
 "Causes of Underground Corrosion", Harco Corporation, Paper HC-36, Median OH
 "Toxicological profile for fuel oils", U.S. Department of Health and Human Services, Public Health Service, Agency for Toxic Substances and Disease Registry (ATSDR) Atlanta, GA 1995. - http://www.atsdr.cdc.gov/toxprofiles/tp75.html
 Public Health Statement for Fuel Oils, ATSDR, (the full document original source can be found at http://www.atsdr.cdc.gov/toxprofiles/phs75.html). An excerpt from this document is just below. ATSDR,
Division of Toxicology,
1600 Clifton Road NE, Mailstop F-32,
Atlanta, GA 30333 888-422-8737.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones