Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS - home
ABANDONING OIL TANKS
ABOVE GROUND OIL TANK (AST) GUIDE
BURIED OIL TANK (UST) GUIDE
HEATING OIL TYPES & PROPERTIES - home
HOME BUYERS GUIDE TO OIL TANKS
OIL SPILL CLEANUP / PREVENTION
OIL TANK ABANDONING PROCEDURE
OIL TANK INSPECTION & TROUBLESHOOTING
OIL TANK LEAKS & SMELLS
OIL TANK PIPING & PIPING DEFECTS
OIL TANK REGULATIONS
OIL TANK REMOVAL COs
OIL TANK SPILL CLEANUP / PREVENTION
OIL TANK LEAK TEST METHODS
OIL TANK TESTING & REMOVAL COs
OIL TANK WATER CONTAMINATION
Sources of oil smells in or outside of buildings: how to track down the source of an oil smell traced to fuel oil, heating oil, or even crude oil leaks from heating equipment, oil piping, or oil storage tanks. This article describes common sources of indoor or outdoor oil odors due to fuel oil, heating oil, or similar products.
A close look at the bottom of the outdoor above ground oil storage tank shown at page top shows what looks like oil seepage [click to enlarge]. We suspect this oil tank is leaking.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
[Click to enlarge any image]
Heating or Fuel Oil Spills During Oil Storage Tank Fill-Up
While usually oil delivery drivers are quite careful, on occasion there may be some spillage around the fill of an oil storage tank occurring during tank fill procedures.
Look for oil stains on the ground around the fill or vent piping for both above ground fill and vent pipes and at the fill and vent pipes for buried oil tanks. If you see an oil spill contact your heating oil company to request cleanup help.
The reporting of fuel oil and heating oil spills of this nature may be required by federal or state laws.
Heating Oil Storage Tank Fill or Vent Pipe Leaks
It is very common for there to be leakage around the oil filler pipe or vent pipe where they are connected to the top of an oil tank. If the tank is buried these leaks may go undetected for some time, but on an above ground oil tank, inside or outside, the seepage is quickly visible and also can be smelled by most owners shortly after an oil delivery.
Details are at OIL FILL PIPE LEAKS.
Usually an oil storage tank is filled right to its top during an oil delivery. This is because the way that the delivery driver knows that the tank is full is that s/he is (supposed to be) listening at the filler pipe.
If the oil delivery driver is not listening to the tank whistle or tank alarm, or if the tank top fittings are not absolutely tight, it is common to see some leakage around the oil tank top after a fill-up.
(Also see Oil Tank Pressures for an explanation of the stresses on oil tanks and piping during fill-up.
If you see oil on the floor, check the bottom of the tank, sides and welded seams,
and be sure to check the oil lines to the boiler and in particular, check the oil tank safety valve or other tank bottom fittings as
there are often leaks at these valves, as shown in this photograph.
Make sure that you know where the seepage is coming from. There may be separate spillage outside at the filler pipe from that occurring inside at the tank top or other fill or vent pipe fittings.
Heating Oil Piping or Valve Leaks
Make sure that the oil fill, vent, and fuel delivery piping is proper in material (steel is safer against rupture than plastic), and in diameter (2" or larger) for both vent and fill pipes.
The soldered copper fill and vent piping at the oil tank in the photo at above left
was unusual and may not be permitted. At the top of this page, the silver-colored (galvanized steel) oil tank vent pipe in the tank is probably too small for modern tank fill methods.
If the seepage is trivial in amount, say simply a light stain just a few inches around the tank top, clean it off and live with it. Or more properly, re-make the pipe joints when other plumbing work is planned. (It's quite a bit of trouble to re-make these joints, especially if the filler and vent piping have been routed through and cemented into a masonry wall.)
If the seepage is enough to wet the tank or run down the whole tank and drip onto the floor this is an
unacceptable condition that needs correction.
If heating oil has been dripped on the floor, ask your oil company to clean it up and deodorize the area.
Actual Leaks in a Fuel Oil or Heating Oil Storage Tank
Leaks at an oil storage tank may not only produce a smell, but are likely to involve significant cost to clean up spilled oil if a significant leak occurs, especially a below-ground leak. We discuss leaky oil tanks beginning
If an oil storage tank is leaking federal (and most state) laws require that the leak be reported to your local department of environmental conservation or environmental protection.
Actual heating oil spills:
If there is an actual oil spill, indoors or out, most state departments of environmental protection require that they be notified within 24 hours of the spill, an inspection is performed, and an expert specifies the amount of cleanup needed.
Leaks also occur or may have previously occurred at abandoned oil tanks in locations that can give off oil odors.
Our two photos above illustrate heating oil leaks seeping through the building foundation wall from an outside oil storage tank leak. Because of the depth of the seepage points in the foundation wall (mid-wall at left, wall bottom at above right) and because there was no oil storage tank visible above ground at these locations, we suspected that a buried oil storage tank had previously leaked close to the foundation wall. Further investigation was needed. Also
and OIL TANK LEAK POINTS.
Oil Odors Traced to Heating Equipment Malfunction
You may be smelling un-burned heating oil or fuel oil if the heating equipment is not working properly. A simple sniff test at the heating equipment may not be enough. Watch the equipment during start-up and shut down cycles, observing puffbacks, odd noises, or of course visual leaks around the equipment that occur during operation or when oil fired heating equipment is idle.
Keep in mind that in buildings heated or cooled by forced air, air ducts may transport odors from one building area to another.
Watch out: a mistake as simple as too little combustion air will produce a smoky flame and heating oil or fuel oil odors at and around oil fired heating equipment.
Oil Smells Traced to Nearby Diesel Fuel Stations, Automotive Repair Shops, or Diesel-Fueled Equipment
Our photo (left) shows a used oil collection tank that was not leaking at the time of our site visit. But at other automotive repair shops we occasionally see careless oil spills by workers or even by customers who drop off used oil for reclamation.
On occasion we observe diesel smells and even small leaks where diesel fueled equipment such as a backhoe or bulldozer is left parked.
Oil Smells Traced to Oil Pipelines or Piping
Oil odors may be traced to underground (or above ground) oil piping both from remote or curbside oil storage tank fill pipes used at some properties and even to oil pipelines that traverse properties.
In 2013 the New York Times reported that oil odors at a farm near Tioga, Colorado were traced to a small 1/4" sized leak in an oil pipeline crossing the property. While oil companies monitor pipelines for evidence of leakage and are expected to respond promptly to any leak, some pipeline sections are not required to have oil leak monitoring nor pressure sensors sufficient to detect small leaks. In cases such as the one reported by the Times, a small oil leak may continue for weeks without detection. 
Really Stupid Sources of Oil Odors
Perhaps the stupidest source of an oil smell tracked down at a residential property was a New York property that included an abandoned water well.
The six-inch casing of the well protruded 18" above ground level close to a driveway.
When we smelled oil along the drive and asked the tenant what was going on he explained that he had been disposing of his used motor oil by "dumping it down into that old pipe"! Here was another good argument for properly sealing and capping an abandoned water well.
Continue reading at OIL LINE PIPING LEAKS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References