Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK (UST) GUIDE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
Indoor oil storage tank inspection guide: advice and example photos for the visual inspection of above ground oil tanks for leaks and damage, improper piping, wrong location, bad fire clearances, including these details: damaged or leaky oil storage tanks, improper oil tank piping, valves, and indoor-type oil tanks located outdoors.
Here are photographs & explanation of some important indicators of oil storage tank condition that any home owner or home inspector can examine when an oil storage tank is visible and accessible inside or at a building.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
If an oil or other fuel storage tank is above ground and accessible for visual inspection it can and should be inspected for evidence of leaks or damage. Here are some inspection pointers for heating oil tanks.Is the tank exterior sound, without leaking seams or excessive rust? Is there a patch or other evidence of a history of leaking?
[Click to enlarge any image]
In the photo at above-left, note the wet bottom of the tank? The inspector needs to decide if the oil on the tank exterior is from weeping at the fill or vent pipe fittings, from leaks at the oil line exiting the tank.
We were concerned about the evidence of seepage around the bottom left on this tank.
What about the next photo shown at left ? a leak at fuel line or at the Fire-o-Matic shutoff valve, or perhaps due to an actual tank perforation?
The size and wetness of the oil spill on this basement floor is a bit large to blame on a drippy fire safety valve.
But notice that in the upper portion of the photo the oil tank itself looks new. This oil spill was from the previous oil tank installed in this location.
Also look for water entry around the oil tank and don't confuse a water leak for an oil leak. Or more difficult, both leaks may be occurring at the same location. Look closely, and if necessary, touch, sniff, and sample the leak substance.
This last photo shows an actual tank leaking at its bottom from a perforation.
Memorize this photo and look under oil tanks when you're inspecting above ground indoor oil storage tanks.
If you see a tarry "stalactite" drip formation on the bottom portion of an oil storage tank, the tank is leaking, has perforated, and can leak catastrophically at any moment.
Watch out: do not pick, poke, or even touch an oil tank that looks like this. The risk is that you perforate the already thin tank bottom, leading to a much bigger and more costly oil leak mess.
For fire safety indoor oil storage tanks should not be located too close to oil burners or other heaters. Typical indoor clearance requirements specify that the oil storage tank should be 10 feet from the oil burner.
Note: the 2012 IRC changed this minimum indoor clearance distance to 5 feet between the oil burner and the oil storage tank. Update courtesy of Carson Dunlop Associates, Toronto. You can see this design in our sketch at left, provided courtesy of Carson Dunlop Associates.
Even before the 2012 IRC change, some communities permited the oil tank to be located closer, just 5 feet away from the nearest oil burner.
If you cannot meet this distance requirement your local building officials or fire officials may approve the oil tank installation if you provide a fire barrier between the oil tank and the burner.
Tanks should also be located where they will not be damaged, such as by being struck by a vehicle entering a garage.
In some communities indoor oil storage tanks located in a garage must be protected against possible vehicle damage by steel posts or similar means.
In some communities indoor oil storage tanks must also be secured against possibly falling or tipping over, such as by using angled steel piping set into the floor and ceiling or floor and wall around the oil tank.
Also see OIL BURNER INSPECTION & REPAIR for a discussion of the impace of leaks at the oil burner assembly itself.
Reader Question: what's the code on distance and clearance for metalbestos chimneys & vents vs oil storage tanks?
I am installing a pellet boiler and will need a second metal chimney as I am leaving my oil burner as a backup. I live in maine. The only place I would like the metal asbestos chimney would run 40” away from my oil tank. Do you know what the code is on this? I am having a heck of a time getting any answers regarding this? - R. B. Windham ME 2/27/2014
Insulated metal chimneys typically require a one-inch clearance from combustibles.
I think the reason you're not finding an answer to your question is that we're mixing up different constraints and safety concerns:
If you were worrying about a horizontal distance for a flue vent connector, from a heater to the chimney, that'd be a different story. Suppose we wanted to run across an entire building from the heater to the chimney: the maximum horizontal length should not be more than 75% of the chimney height above the vent connector, or 100% if the chimney is insulated.
So you'd need a chimney at least 40 feet tall. But an option that may work acceptably is to include a draft inducer fan such as the type made by Field Controls.
Continue reading at OIL FILL & VENT PIPING or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
(May 21, 2014) M. A. Valliani said:
Is it not better to locate fuel oil day tank below the burner level? In elevated tanks, pipe leakages may result in draining of tank.
Placing an oil storage tank below the burner may have the advantage you cite but it incurs other costs including
For these and perhaps other reasons, above ground tanks are widely used and are equipped with check valves to prevent accidental draining of the tank.
See OIL LINE CHECK
(Aug 14, 2014) DAVID HADDAD said:
the oil tank is inside the house and the fill pipe is outside the house , so how high should be the oil fill pipe above the ground level ?
11/11/2014 louise said:
What is the allowable distance for installation of an above ground heating oil storage tank between the tank and the next door neighbor?
Louise, figure 5-10 feet from combustibles & an oil burner plus property line setback requirements specified by your local zoning and building department.
Oil storage tank clearances are given at OIL TANK INSPECTION & TROUBLESHOOTING
However additional clearance distances between a water well and oil storage tanks might be specified in some jurisdictions. See WELL CLEARANCE DISTANCES...
Questions & answers or comments about indoor home heating oil storage tanks: installation, inspection, leaks, piping, troubleshooting
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References