Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
OIL STORAGE TANKS
ABANDONING OIL TANKS
AGE of OIL TANK
ANODES & DIP TUBES on WATER HEATERS
BURIED OIL TANK (UST) GUIDE
BURIED OIL TANKS, FINDING
COMBUSTION PRODUCTS & IAQ
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECTORY of OIL TANK EXPERTS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOATING UP OIL STORAGE or SEPTIC TANKS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GALVANIC SCALE & METAL CORROSION
GAUGES ON HEATING EQUIPMENT
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HEATING OIL CLOUD WAX GEL POINT
HEATING OIL EXPOSURE HAZARDS, LIMITS
HEATING OIL - OLD, USEABLE?
HEATING OIL PIPING TROUBLES
HEATING OIL SHELF LIFE
HEATING OIL SLUDGE
HEATING OIL TANKS
HEATING OIL TYPES & PROPERTIES
HEATING OIL USAGE RATE
HEATING SYSTEM NOISES
HOME BUYERS GUIDE TO OIL TANKS
NOISE CONTROL for HEATING SYSTEMS
NOISES COMING FROM WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FUEL TYPES & CHARACTERISTICS
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
SOOT on OIL FIRED HEATING EQUIPMENT
STAIN DIAGNOSIS on BUILDING INTERIORS
THERMAL TRACKING & HEAT LOSS
VIDEO GUIDES: Heating System Videos
VIDEO GUIDES - InspectAPedia.com
WINTERIZE A BUILDING
This document describes and provides home inspection report language for reporting evidence of buried heating oil tanks. Beyond the costly problem of leaky heating oil tanks, this series of articles lists other important safety or oil-fired equipment operational defects in home and light commercial heating oil storage and piping systems - see the links listed at the "More Reading" links at the bottom of this article .
This sample home inspection report language may assist home owners or home buyers in understanding risks associated with both buried and above ground oil or other fuel storage tanks at their property. The oil tank and oil piping inspection report language explains the need for action and indicates where more information can be obtained. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
How to Report the Presence or Suspected Presence of a BURIED OIL Storage TANK - Found or Suspected at a Property
Sample oil tank inspection report for buried oil tanks: A buried oil tank is installed and could not be inspected.
We saw the following evidence that a buried oil storage tank is or was in use at this property:
The presence of these abandoned copper pipes does not tell us whether or not the underground storage tank has been tested, abandoned in place, or removed.
The oil filler pipe found on the property shown at the top of this page is firm evidence that the underground oil storage tank is still in place - it would be improbable that a buried oil would or even could be removed while leaving its filler pipe in place. In fact home buyers need to be alert for the opposite possibility - that a buried tank remains in place, without proper abandonment, but someone has simply unscrewed and removed the oil tank fill and vent piping that previously were visible above ground.
Before completing purchase of a property that has or had a buried oil tank you need to have either had the tank removed, abandoned in place, or tested. At end of the day, you need reliable documentation that shows that either there has been no leakage and a proper tank abandonment has been performed, or if there was leakage, that a proper cleanup has been performed. If the oil storage tank is a newer buried model (perhaps a fiberglass or multi-walled oil storage tank) and if the oil tank is in good condition it may not need to be abandoned. But if older oil storage tanks were used, were removed, or remain abandoned at the property you still need to satisfy the requirements of this paragraph. The discussion which follows explains the risks and gives detailed advice about what to do about buried or above ground oil tanks and tank leaks.
Also see text and oil tank defect photographs at Visual Inspection of Oil Storage Tanks. NOTICE: while example report language is provided here, reproduction of this or any of our web pages or their contents online at other websites or in printed documents for sale is prohibited. Readers are welcome to use the text directly in home inspection reports, with citation of the website source.
This article has focused on the prime risks associated with buried oil tanks that may have caused or be soon to cause a costly leak problem. Other types of oil storage and oil piping system inspection, defects, and reports, need to be addressed - see the articles named in the links below.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References