Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
MOLD: A COMPLETE GUIDE to TEST CLEAN PREVENT
ACTIVITY of MOLD in BUILDINGS
AGE of MOLD, HOW OLD
AIR CLEANER PURIFIER TYPES
AIR FILTERS for HVAC SYSTEMS
AIR TEST SAMPLING CASSETTE STUDY
AIRBORNE MOLD COUNT NUMBER GUIDE
AIRBORNE PARTICLE ANALYSIS METHODS
ALLERGEN TESTS for BUILDINGS
BROWN HAIRY BATHROOM MOLD
BIBLIOGAPHY for ENVIRONMENTAL HEALTH, MOLD, IAQ
BLACK MOLD, HARMLESS COSMETIC
BLACK MOLD, TOXIC & ALLERGENIC
BLEACHING MOLD, Advice about
BOOK MOLD, CLEANING
BOOKSTORE - ENVIRONMENTAL
CACTUS FUNGI / MOLD
CAR MOLD CONTAMINATION
CARPET DUST IDENTIFICATION
CARPET PADDING ASBESTOS, MOLD, ODORS
CARPET FUNGICIDAL SPRAY
CARPET STAIN DIAGNOSIS
CARPET & other STAIN TESTS
CARPET TEST PROCEDURE
CARPETING & INDOOR AIR QUALITY
CHAIN OF CUSTODY - TEST SAMPLE
CLEARANCE INSPECTIONS - MOLD CLEANUP
DIRECTORY of MOLD / ENVIRONMENTAL EXPERTS
DIRT FLOOR MOLD CONTAMINATION
DISINFECTANTS & SANITIZERS, SOURCES
DISINFECTING BUILDINGS with BLEACH
DO-IT-YOURSELF MOLD CLEANUP WARNINGS
DUST ANALYSIS for FIBERGLASS
DUST, HVAC CONTAMINATION STUDY
EFFLORESCENCE SALTS & WHITE DEPOSITS
FEAR of MOLD - MYCOPHOBIA
FIBERBOARD INSULATION SHEATHING MOLD
FIBERGLASS INSULATION MOLD
FIND MOLD, ESSENTIAL STEPS
MOLD in BUILDINGS
FIRE DAMAGE vs MOLD DAMAGE
FLOODS in BUILDINGS, MOLD PREVENTION
FOXING STAINS on books & papers
FUNGICIDAL SPRAY & SEALANT USE GUIDE
GAS DETECTION INSTRUMENTS
GAS EXPOSURE EFFECTS, TOXIC
GAS EXPOSURE LIMITS & STANDARDS
GAS TEST PROCEDURES
HOUSE DUST ANALYSIS
HOUSE DUST COMPONENTS
HUMIDITY CONTROL & TARGETS INDOORS
LAB PROCEDURES MICROSCOPE TECHNIQUES
LIGHT, GUIDE to FORENSIC USE
MEDIA BLASTING for MOLD REMOVAL
METHANE GAS SOURCES
MICROSCOPE DIGITAL PHOTOGRAPHY
MEDIA BLASTING for MOLD REMOVAL
METHANE GAS SOURCES
MICROSCOPE DIGITAL PHOTOGRAPHY
MILDEW ERRORS, IT's MOLD
MILDEW REMOVAL & PREVENTION
MOISTURE CONTROL in BUILDINGS
MOLD: A COMPLETE GUIDE TO MOLD
MOLD EXPERT, WHEN TO HIRE
MVOCs & MOLDY MUSTY ODORS
MYCOPHOBIA, STAINS MISTAKEN for MOLD
MYCOTOXIN EFFECTS of MOLD EXPOSURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
RENTERS GUIDE TO MOLD & IAQ
ROBIGUS & Wheat Rust Fungus
SMELL PATCH TEST to Track Down Odors
STAINS on & in BUILDINGS, CAUSES & CURES
THERMAL IMAGING MOLD SCANS
TRAPPED MOLD BETWEEN WOOD SURFACES
UV LIGHT BLACK LIGHT USES
VAPOR BARRIERS & CONDENSATION
VENTILATION in BUILDINGS
VOCs VOLATILE ORGANIC COMPOUNDS
WATER ENTRY in BUILDINGS
Mold cleanup mistakes: inadequate mold cleanup plan, too-narrow a scope of work. Here we explain how an inadequate mold cleanup plan can end up costing unnecessarily when hiring a mold cleaning company. This section of our "How to Clean Mold" article describes common mistakes people make when attempting to clean up mold. Avoiding these mold cleanup errors can save you money and may also avoid dangerous side effects of bleach, mold chemicals, or ozone when improperly applied.
We also discuss common errors made when cleaning wood surfaces, such as relying on bleach or performing expensive and unnecessary cleaning on cosmetic black mold on wood surfaces.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
MOLD CLEANING MISTAKES people make when cleaning-up moldy building materials and moldy surfaces, continued.
Mold tests with no inspection: The most common complaint we hear from readers is that they have just paid a "mold expert" (read "weekend mold class") to "inspect and test" their building for toxic mold, but the expert, who may have been paid $600. to $2400. did not do a thorough job.
Tests for mold, used without an accompanying building inspection by an expert, are not reliable when they give a negative ("no mold found") result.
Do the job right: If a professional mold inspection and test was justified in the first place, (see MOLD EXPERT, WHEN TO HIRE), then it the job should have been done with sufficient expertise and thoroughness that the building owners and occupants can have reasonable confidence in the conclusions reached.
Our photo at left shows a very moldy pantry in a home. Even if this is all the mold that was seen, mold growth this heavy suggests damp indoor conditions - it may be appropriate to inspect the building carefully and completely.
If you are betting the health of building occupants and perhaps also many thousands of dollars on the results of a "mold test" then shouldn't the test be thorough and valid?
In our opinion, we'd rather have no tests performed than accept the "findings" of unreliable tests and screens for mold.
Mold Cleanup Workmanship, Procedures, & Asbestos: We add that during any building demolition or remodeling you should be alert for other building contaminants that might need attention and which can be most-economically addressed by combining them into the mold remediation project.
A common example is the discovery of asbestos pipe or surface insulation in a building which because of its location or condition needs to be encapsulated or removed.
Since the technology for mold remediation involves similar containment and cleaning standards, if you have an asbestos problem at a different area on a moldy building you should discuss adding that work to the job.
If asbestos materials are in the mold-remediation area and will be disturbed by the mold cleanup process, removing and cleaning this material will probably be unavoidable and will, unfortunately, add to the cost of the job.
INCOMPLETE MOLD CLEANUP or incomplete removal of moldy materials, or RELYING ON of BIOCIDES, MOLD SPRAYS and MOLD ENCAPSULANT PAINTS
Leaving moldy insulation that looks "OK" but was wet or was exposed to mold, demolition dust, and debris. See INSULATION MOLD TEST.
Leaving moldy surfaces: from failing to examine the work area and other building areas; leaving moldy areas even outside of the remediation area can prevent a successful clearance inspection and test.
Leaving mold reservoirs that were missed at the initial inspection (client says "just inspect the basement") can also significantly add to the mold cleanup cost if the mold remediation crew has to return to the property to address a moldy area that should have been included in (but was omitted from) the original work plan. (Photo at left shows moldy flooring left under a built-in bureau).
Failure to remove moldy debris or mold-suspect insulation, leaving demolition debris, and just failure to actually sweep up and HEPA vacuum the cleanup area are surprisingly common among un-trained (and lower-initial-cost) mold cleanup company work.
Our photo (left) shows a crawl space that was "sprayed with mold encapsulant) in a $14,000. crawlspace mold cleanup job. Our client did not get what they needed.
Moldy fiberglass insulation was not removed
The crawl space floor was littered with debris
Occasional "where easy" joists had been sprayed - this work was expensive and ineffective.
See MOLD CLEARANCE INSPECTIONS for a description of tests and inspections to be sure that a mold cleanup job has been done properly. A paid professional mold clearance inspection is appropriate if the mold cleanup job itself involved a significant cost.
Spraying biocides or fungicidal sealants over moldy dust, dirt and debris that should have been removed (photo above right) is a common mold cleanup error. You may be leaving "dead" but toxic or allergenic particles at high levels in the building.
We like biocides as a final wash, and we like fungicidal sealants in problem areas because by reducing the moisture-uptake of wood surfaces they probably retard future mold growth. Our photo (above left) shows a worker applying biocide to carpeting - not a procedure that we recommend. Moldy wall to wall carpets should be removed.
But biocides, fungicidal sprays, and encapsulating mold paints are not an effective substitute for removing the problem mold reservoir in a building. See FUNGICIDAL SPRAY & SEALANT USE GUIDE for additional details. See MOLD SPRAYS, SEALANTS, PAINTS for a discussion of when where how and why to use biocide or fungicidal sprays and encapsulating mold sprays and paints.
Here we show the results of a professional and well-executed moldy crawlspace cleanup job during our clearance inspection and test. This crawl space was difficult because building management was reluctant to take the necessary steps to keep out water. See HOW TO PREVENT FUTURE MOLD for a photo of a water entry source at this crawl space.
Even with these steps, unless the property manager takes the necessary steps to prevent future water in the crawl space this area could have a new problem, especially if it is re-insulated using fiberglass batts.
Continue reading at INCOMPLETE MOLD CLEANUP, RELYING ON SPRAYS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Mold Contamination Testing, Cleanup, Prevention: references & products
OTHER IAQ ISSUES: How To Find and Address Other Indoor Air or Indoor Environment Contaminants Besides Mold
Mold or allergens may not be the only or even the main indoor environmental contaminant. Don't let media attention to mold cause so much enviro-scare fear that other, possibly more urgent hazards go un-addressed.