Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC HEAT, DIAGNOSIS, REPAIR
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
LP & Natural Gas Safety Hazards
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC HEATER VENT
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
Gas fireplace & gas space heater inspection & defect checklists. This article lists significant gas heater or gas fireplace defects, definitions, and home inspection education topics. This article series, beginning at BUILDING DEFECTS LISTS, provides lists of common building defects and basic defect knowledge that also outline recommended curriculum content for home inspector education. The building defects and inspection points listed in these articles also guide homeowners and home buyers to building areas that merit careful attention and often point areas of safety concern or important maintenance and repair tasks.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
4.8 Gas Space Heaters and Fireplaces Inspection Recommendations & Lists of Defects
Safety Warnings about Gas-Log Fireplaces & Gas-Fueled Space Heaters in Buildings
Improper installation, venting, combustion air supply or use of gas or kerosene fired heaters can produce high indoor carbon monoxide(CO) levels.
Watch out: Never go to sleep in an enclosed space with a space heater left operating. In addition to the CO hazards there is a risk of oxygen depletion which can also lead to asphyxiation. Also see Unvented heaters, below.
Tight House conditions can cause dangerous carbon monoxide hazards where gas fired fireplaces or space heaters are in use
Even if previously there were no backdrafting or CO problems at a building, retrofits to improve the energy efficiency of a home can change its air leakage rate and might lead to backdrafting.
Unsafe models of space-heating equipment
For some examples see SAFETY RECALLS CHIMNEYS VENTS HEATERS - warning: this is not an exhaustive list
Un-vented heaters or space heaters installed in buildnings
4.8.1 Knowledge Base for Gas Heaters & Fireplaces: Inspections & Defects
1. Describe the function of gas space heaters and gas fireplaces.
2. Describe the types of gas space heaters including wall furnaces, floor furnaces and room heaters. Highlight the difference between these and forced air furnaces.
3. Describe gas fireplaces and gas logs, highlighting the differences between these and wood burning fireplaces.
4. List the materials and components of each of the systems listed above.
5. Describe the features of good installation and repair technique for each of these systems.
6. Define the following terms with respect to gas space heaters and fireplaces: decorative appliance, radiant system, convective system, vent, unvented appliance, direct vent system, fire stop spacer, inspection cap (for furnace).
7. Identify the code or standards which apply to gas fired space heaters and fireplaces in your area.
4.8.2 Inspection skills for Gas Heaters & Fireplaces: Inspections & Defects
1. Describe the inspection procedure for gas fired space heaters and fireplaces.
2. Identify the following common defects listed on the next page.
3. Describe the implication of each defect.
4. Identify safety issues for the inspector and occupant of the home (gas explosion, electric shock, fire, combustion products poisoning occupants, injury due to moving parts).
5. Communicate findings with client verbally and in writing, recommending corrective action where needed.
Typical Visually-Obserable Gas Fired Space Heater, Room Heater, or Fireplace Defects
Combustion Air Hazards
Heat Exchanges in Gas-Fired Space Heaters
• Cracks, holes or rust
• Soot or deposits
• Rusting or dirty
Fan Limit Switch Defectson Gas Fired Space or Room Heaters
• Set wrong or defective
• Improperly wired
• Mechanical damage
• Missing cover
Cabinets: Gas fired space heaters
• Combustible clearances
• Mechanical damage
• Missing components
• Obstructed air intake
Inspection Defects Specific to Gas Fired Wall Furnaces
• Ducts added
• Not listed, certified or approved
• Unvented furnace in bedroom or bathroom
• Unvented furnace
Inspection Defects Specific to Floor Furnaces
• Cap missing or damaged
• Firebox cracked or rusted
• Not permitted
• Not listed, certified or approved
• Restricted airflow causing overheating
• Thermostat remote
Common Defects Observable at Room Thermostats Used with Gas Space Heaters or to Control Gas Fireplaces
• Not level
• Poor adjustment or calibration
• Poor location
Defects in Blower Assemblies Used on Gas Fired Space Heaters
• Fan belt loose, worn or damaged
Inspection Defects Specific to Gas Fired Room Heaters
• Fireplace damper not fixed open
• Not labeled for use in a fireplace
• Poorly secured
• Running continuously
• Too small
• Unbalanced or vibration
Inspection Defects Specific to Gas Fireplaces & Gas Logs
• Damper in existing fireplace not fixed open
• Glass door problem
• Not suitable for use in a bedroom or bathroom
• Unvented (may be acceptable ?)
• Asbestos-suspect based on age
Gas Supply Defects at Gas Fired Space Heaters, Room Heaters, Fireplaces
Improper gas piping material
Missing or improperly located gas shutoff valve
Indications of leaks (odors, deposits, complaints)
Readers should see HEATING SYSTEMS for our complete list of articles on this topic. Also see HOME & BUILDING INSPECTORS & INSPECTION METHODS. Use the Search Box at the top or bottom of these pages to find in-depth information about building, energy savings, and indoor environment inspection, diagnosis and repair at this website. Watch out: these inspection lists do not list all possible defects for the systems discussed, and not all home or building inspectors will examine all of the items listed here. CONTACT us to suggest corrections or additions to articles at this website.
These curriculae and building defect lists are based on smilar curriculum documents first prepared by Joe Scaduto, an ASHI member who prepared course material for Northeastern University's Building Inspection Certificate program in 1988, subsequently by DF, InspectApedia's editor, for New York University ca 1988 and later, with others, recommended to ASHI, the American Society of Home Inspectors. ASHI did not adopt this material though currently that association as well as others offer extensive HOME INSPECTOR EDUCATION material. The curriculum and lists of defects are informed by additional analysis of the process of home inspection that was developed beginning Calgary, AB for Canadian and U.S. home inspector education and certification examinations in 1997. Other early contributors to home inspection education in the U.S. and Canada include Dr. Jess Aronstein, Alan Carson, Mike Casey, Mark Cramer, John Cox, Dwight Barnett, Douglas Hansen, Rick Heyl, Larry Hoytt, Bill Merrill, Kevin O'Malley, Dennis Robitalille, Keith Peddie, Pat Porzio, Roger Robinson.
Frequently Asked Questions (FAQs) about LP or natural gas fired space heaters
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: email@example.comCarson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. (416) 964-9415 1-800-268-7070 firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides:
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com 11/06
Roger Hankey is principal of Hankey and Brown home inspectors, Eden Prairie, MN. Mr. Hankey is a past chairman of the ASHI Standards Committee. Mr. Hankey has served in other ASHI professional and leadership roles. Contact Roger Hankey at: 952 829-0044 - email@example.com. Mr. Hankey is a frequent contributor to InspectAPedia.com.
Arlene Puentes, an ASHI member and a licensed home inspector in Kingston, NY, and has served on ASHI national committees as well as HVASHI Chapter President. Ms. Puentes can be contacted at firstname.lastname@example.org
Wikipedia provided background information about some topics discussed at this website provided this citation is also found in the same article along with a " retrieved on" date. NOTE: because Wikipedia entries are fluid and can be amended in real time, we cite the retrieval date of Wikipedia citations and we do not assert that the information found there is necessarily authoritative.
Our recommended books about building & mechanical systems design, inspection, problem diagnosis, and repair, and about indoor environment and IAQ testing, diagnosis, and cleanup are at the InspectAPedia Bookstore. Also see our Book Reviews - InspectAPedia.
Home Inspection Reports - a Critique narrative vs. checklist type home inspection reports
ASHI Standards of Practice - Jan 2000 and ASHI Standards History - links to older and alternative versions of Home Inspection Standards
ASHI Code of Ethics 1993, and ASHI Ethics History - links to older versions; Note: newer may be found at ASHI
ASHI in 1996 ASHI History - association description from 1996
Basement Moisture Control, U.S. Department of Energy
Building Pathology, Deterioration, Diagnostics, and Intervention, Samuel Y. Harris, P.E., AIA, Esq., ISBN 0-471-33172-4, John Wiley & Sons, 2001 [General building science-DF] ISBN-10: 0471331724 ISBN-13: 978-0471331728
Building Pathology: Principles and Practice, David Watt, Wiley-Blackwell; 2 edition (March 7, 2008) ISBN-10: 1405161035 ISBN-13: 978-1405161039
Crawl Space Moisture Control, U.S. Department of Energy
Historic Preservation Technology: A Primer, Robert A. Young, Wiley (March 21, 2008) ISBN-10: 0471788368 ISBN-13: 978-0471788362