Steam Radiator Vent Disassembly & Repair
Steps in taking a steam radiator vent apart to repair or adjust it before throwing it away and installing a new one
STEAM RADIATOR VENT REPAIR - CONTENTS: how to clean or repair a steam vent; taking apart a steam vent to see how it works and to maybe try cleaning or adjusting it. Recommendations for steam vent replacement vs. repair.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Steam radiator vent repair or parts replacement, disassembly, inspection, repair or replacement:
Using annotated photographs we disassemble an adjustable Vent-Rite NO. 51 one pipe steam radiator vent to see what's inside, to look for repairable or clean-able components, and to decide if the vent should be repaired or just replaced.
Let's be clear: the least troublesome and fastest repair is to just replace a bad-behaving steam vent. But if you are determined to try cleaning a steam radiator vent or if you just want an up close look at what's inside, this article will be fun.
Taking Apart an Adjustable Steam Vent from Vent-Rite - the Vent-Rite No 51
When this Vent-Rite steam vent, No. 51 (that you'll have trouble even finding online) stopped working the owner had tried adjusting the vent rate using the adjustable nut on the vent bottom. But the vent no longer worked, probably because its float had developed a leak.
We disassembled the unit to show the hidden parts and thus the secrets of the Vent-Rite steam radiator vent in a series of images given here.
[Click to enlarge any image]
Watch out: it may be possible to get a bad steam radiator vent or steam main line vent working again by simple cleaning without disassembly. To try that approach see STEAM RADIATOR VENT CLEAN & TEST
At above left you see the Vent-Rite No. 51 adjustable steam radiator valve before I destroyed it. At above right you can see the vent opening in the valve top. This opening vents air when the radiator is cold, and as the radiator heats and the vent closes, things should get quiet and the valve stops venting.
Thanks to reader Paul Ruud for discussing improved steam heat controls and thermostatically operated steam radiator valves and air vents and for providing the steam radiator vent that we disassembled for these photographs.
Some steam may vent before the valve closes. But if the vent never closes and keeps blowing steam or perhaps a mix of steam and condensate ("steam vent spitting") something's wrong.
Most likely the internal valve seat is dirty or damaged and won't seal or the internal thermostatic float in the valve is defective - it's time replace the steam vent.
Watch out: steam can cause serious burns and steam condensate can be burning hot as well as a source of building water damage. Do not try to work on live steam or hot steam heating radiators and vents. Turn off and cool down the system before touching anything.
These notes and photographs are for purpose of illustration. While swapping out a steam vent for a new one is simple enough that with some caution a homeowner can attempt the task, in most cases repairs on steam heating systems are best performed by a trained service technician.
At below left I give a close-up of the Vent-Rite adjustment nut that we thought might change the vent operation - but it didn't. We decided to look inside, figuring if the vent is broken and is going to be replace anyway there's nothing to lose in tearing an old one apart for the sake of science.
Start by holding the vent bottom with a wrench and using a larger wrench to turn the nut I'm pinching with my fingers (below right).
Now we're getting someplace. At below left you can see the Vent-Rite top and bottom sections have been separated; a copper gasket is used at this mating joint and I've slipped the nut half-way up the vent body. If you are indulging in the fantasy that you can clean and restore this valve to service, press on, but remember I told you to just go ahead and buy and install a new one on the radiator before messing with the old valve.
At above right I'm holding the vent adjustment nut with pliers and you can see that if it did anything, that nut would move the plunger in or out to press more or less against the bottom of the Vent-Rite's internal float. At below left you can see the plunger working end. At below right I'm showing how the adjustable plunger, by moving in or out of the vent body, would make the vent's internal float start at a higher or lower position inside the vent body. Why we care about the float position will be shown next.
OK so here's how this vent works to open or close the steam vent on a radiator. If the float rises its tapered point pushes against an opening in the top of the valve body to stop steam from escaping. If the float falls it opens the vent. The vent will close either thermostatically (it gets hot and the float pushes up and closes the opening in the vent top) or by floating upwards should actual condensate (water) fill the float body. Just follow the yellow arrow.
Now we know why a steam vent might "spit" water: its top opening is not closing fully AND the radiator has a lot of condensate inside.
At below left we show a close-up of the actual steam radiator vent float and its tapered tip.
At above right we show the steam radiator vent disassembled but with its parts in order - more or less. From the bottom up is the adjustment nut, the valve base containing its internal plunger, gasket, vent float, vent top body that includes a vent orifice at its top, and a large ring nut that secures the vent body top to its base.
Steam radiator vent repair versus replacement
If you are a tinkerer or if you are desperate to try to get a recalcitrant steam vent working and don't have a replacement at hand (replacement is still our best advice), you might want to try disassembling the steam vent and then cleaning the valve seat or float pin in a steam radiator vent.
But really for most repair technicians or building occupants or owners you'd be better off just replacing the steam valve if simple cleaning (described in a separate article at STEAM RADIATOR VENT CLEAN & TEST did not work) didn't work: it's often not worth the time and trouble to actually disassemble the steam vent, especially since there's a good chance that if the valve no longer opens or closes when it should it's the float itself that's at fault.
Given the trouble of cleaning and reassembling and reinstalling the valve, then bringing up the heat to watch the valve to see if it works, the disappointment when it doesn't, and the muttering, to me it makes sense to just go ahead and replace the steam vent with a new unit.
Continue reading at STEAM VENTS, AUTOMATIC or select a topic from the More Reading links or topic ARTICLE INDEX shown below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"Rv-4 One-Pipe Steam Radiator Valve", available from Armstrong International,
816 Maple Street, Three Rivers, MI 49093 USA, Tel: (269) 273-1415, Armstrong has offices in Beijing, China, Belgium, India and Mexico. Web search 12/27/2010, original source:
Report 95-14, PB96-198163 Thermostatic Radiator Valve (TRV) Demonstration Project, contact NYSERDA. 17 Columbia Circle, Albany, NY 12203-6399 Toll-Free: 1-866-NYSERDA, Tel:(518)465-6252, Ext. 241. Web Search 12/27/2010, original source: http://www.homeenergy.org/archive/hem.dis.anl.gov/eehem/96/960509.html
VariValve® Quick-Vent from Heat Timer, adjustable radiator and main line vent valves for one pipe steam systems, web search 12/27/2010, original source: http://www.heat-timer.com/enFiles/ProductDocument/literature/VariV056082C.pdf
"Care & Feeding of Air Vents", Dan Holohan, Old House Journal Online, November 2004
The Steam Book, 1984, Training and Education Department, Fluid Handling Division, ITT [probably out of print, possibly available from several home inspection supply companies] Fuel Oil and Oil Heat Magazine, October 1990, offers an update, (see next item in this list). ITT Fluid Technology,
1133 Westchester Avenue
White Plains, NY 10604,
tel +1 914 304 1700 fax +1 914 696 2950 www.ittfluidbusiness.com
Principles of Steam Heating, $13.25 includes postage. Fuel oil & Oil Heat Magazine, 389 Passaic Ave., Fairfield, NJ 07004.
Domestic and Commercial Oil Burners, Charles H. Burkhardt, McGraw Hill Book Company, New York 3rd Ed 1969.
National Fuel Gas Code (Z223.1) $16.00 and National Fuel Gas Code Handbook (Z223.2) $47.00 American Gas Association (A.G.A.), 1515 Wilson Boulevard, Arlington, VA 22209 also available from National Fire Protection Association, Batterymarch Park, Quincy, MA 02269. Fundamentals of Gas Appliance Venting and Ventilation, 1985, American Gas Association Laboratories, Engineering Services Department. American Gas Association, 1515 Wilson Boulevard, Arlington, VA 22209. Catalog #XHO585. Reprinted 1989.
The Steam Book, 1984, Training and Education Department, Fluid Handling Division, ITT [probably out of print, possibly available from several home inspection supply companies] Fuel Oil and Oil Heat Magazine, October 1990, offers an update,
Principles of Steam Heating, $13.25 includes postage. Fuel oil & Oil Heat Magazine, 389 Passaic Ave., Fairfield, NJ 07004.
The Lost Art of Steam Heating, Dan Holohan, 516-579-3046 FAX
Principles of Steam Heating, Dan Holohan, technical editor of Fuel Oil and Oil Heat magazine, 389 Passaic Ave., Fairfield, NJ 07004 ($12.+1.25 postage/handling).
Boilers, Boiler Conversions, James E. Brumbaugh, ISBN 0-672-23389-4 (v. 1) Volume II, Oil, Gas, and Coal Burners, Controls, Ducts, Piping, Valves, James E. Brumbaugh, ISBN 0-672-23390-7 (v. 2) Volume III, Radiant Heating, Water Heaters, Ventilation, Air Conditioning, Heat Pumps, Air Cleaners, James E. Brumbaugh, ISBN 0-672-23383-5 (v. 3) or ISBN 0-672-23380-0 (set) Special Sales Director, Macmillan Publishing Co., 866 Third Ave., New York, NY 10022. Macmillan Publishing Co., NY
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The ILLUSTRATED HOME illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The HOME REFERENCE BOOK - the ENCYCLOPEDIA of HOMES, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The HORIZON SOFTWARE SYSTEM manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones