Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC Plexvent / Ultravent RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Radiant floor or system heating zone troubleshooting: this article, using an actual case, describes the diagnosis and repair of a cool or cold zone in a multi-zone radiant floor heating system. The building owner describes the problem and provides photos of the radiant heating system controls. In discussing several diagnostic questions we pose possible explanations of the trouble.
After a power outage and power surges, apparent weird heating behavior (heating zone running backwards or water circulating when there is no heat call) are ultimately traced by the building owner to air in the heating zone tubing of this radiant-floor heating system.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Reader Question: radiant floor heating zone runs backwards after power surges - traced to Air-Bound radiant heat tubing loops
We recently had a “5 day power outage” in really cold weather. Since restarting my system (which has worked fine in the past) I have a three zone system but only two work fine. For the third (upper level), when not calling for heat, water circulates - when thermostat calls for heat, water stops flowing. What would cause that? - S.C. 1/21/2014
[Click to enlarge any image]
At above left we see three WarmRite radiant heat floor zone controls. Each has its own circulator, manifold, temperature gauges and related controls.
For the WarmRite Floor radiant heat control and manifold shown at above right, at the bottom or return manifold we see that this heating zone uses four tubing loops.
A = zone valve controlled by the room thermostat
B = Flow control for each heating zone or run
Let's get this figured out. A circulator that runs when NOT calling for heat and stops when you call for heat - if that's exactly what's happening, suggests to me a power surge or other-damaged relay, control or thermostat.
Our sketch at left shows a simple diagram, courtesy Entran radiant heating, illustrating the pressure test kit connections to a radiant heating circuit.
On occasion we also lose a capacitor on a motor or a motor can actually run backwards but this does not quite sound right from what you said so far.
1. Reassure me that nobody has touched or changed any wiring or controls.
2. What type of zone control are we using: multiple circulators or 1 circulator and multiple zone valves [this question was later answered by the photographs given above - Ed.]
3. Things to check right away - these snafus could explain why one of 3 radiant heat zones is not heating
Please refer to the pictures of my system [shown above], then see additional answers to your questions below.
When calling for heat, flow is indicated as "normal" in each tubing run - [B] in the photograph above.
When thermostat turned up in 3rd zone, I can see the change in A (lever moves down), but then the flow seems to stop and flow indicators B get “sucked” up to zero (= 0 liters/minute) - which indicates that something is blocking the flow once the zone is opened up to the hot water from the main heating system.
Working "backwards" - as far as we're sure that's what's happening - should be diagnostic.
It looks from the photos as if each heating zone has its own circulator pump and control and as if the circulator is a Grundfoss unit. But I can't make out the zone valve brand and model. That's item [A] in your photo at above-right.
Indeed for some heating controls, a power surge or lightning strike can damage the equipment and cause erratic operation. It's a little early yet but I suspect we're going to end up changing out that zone valve. But first we'll want to rule out a mechanical problem.
It almost looks as if your zone valve has gotten reversed. Normally on a call for heat by the thermostat, wires connected to the zone valve's low voltage motor cause the motor to rotate a mechanical valve to allow water to flow, and on end of the call for heat the motor rotates the valve closed. When the valve fully-opens, and end-switch in the valve turns on the circulator.
When the TT stops calling for heat the valve closes and turns off the circulator.
Radiant Heat Floor Resources for your system:
Reader follow-up: radiant heat "no-heat" problem solved - automatic air purging fixed the air-bound system
I have good news though. After reading my own notes on the symptoms, it appeared that opening the zone to the supply system created a vacuum. Therefore it would have to be something somewhere on the supply side that is causing the “blockage”.
Although I was timid when in previous tests (turning the thermostat up, making it call for heat) as I feared the vacuum created may damage the circulating pump for the zone.
This time I got more adventurous and left the zone calling for heat, and once the vacuum was created, I closed and opened the supply valve several times and noticed it seem to alleviate the vacuum scenario longer each time. Eventually, the vacuum was not created at all and there was plenty of air (which the system is bleeding out now).
After the power outages, the other two zones had air as well, but worked themselves out after a while and were never “blocked”. I suspect the 3rd zone’s supply from the main system had the air-lock - most likely due to water being frozen for the week of -30 degree temperatures - the 3rd zone’s supply and return to the main system runs closest to the outside wall of the basement (exposed to the colder temperatures).
All seems to be working fine now, and I appreciate the effort you put into trying to determine the problem and resolving my “issue”.
Thanks again - it is appreciated.
Thanks for the follow-up. The lesson we learned is that depending on where you observe or measure hydronic heating, radiant or not, an air bound system may show up as a "vacuum" on the inlet side of the circulator pump. Nice to know!
The air eliminator, typically part of an expansion tank and air purge kit, is a device used to vent air from the radiant heat tubing and piping system.
Without this device it is easy for water flow through the heating tubing to become blocked or air-bound.
The problem of air-bound heating systems is not unique to radiant heating, nor are its solutions.
In our photo (above left) (1) marks the air scoop/air purge device, (2) marks the automatic air bleed valve that removes air collected in (1), and (3) marks pressure and temperature gauges installed on the system.
While these components are found on other hydronic heating systems, often a factory-packaged radiant heating system installation will include a factory-designed plumbing package that includes all of the necessary fill and drain valves, expansion tank, air purge or air eliminator valve.
Our photo (left) shows a Spirovent air purger eliminator installed on a radiant heat floor system.
Details about types of air purging devices are at
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.