Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC Plexvent / Ultravent RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Single function boiler limit control switches, strap-on aquastats or limit controls on heating equipment: here we explain the functions and typical settings single function limit controls and for strap-on limit controls or aquastats used on both hot water heating boilers and on water heaters
This article series answers most questions about Heating System Boiler Controls on central heating systems to aid in troubleshooting, inspection, diagnosis, and repairs. The photo above shows a Honeywell R8182D combination heating control, also called an "aquastat". Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Use of a single function limit switch on boilers & tankless coils
Here (above left) is a photo of a more traditional single-function heating boiler limit controls. In this example the aquastat or limit switch is being used on a tankless coil that happens to be on steam boiler. If you click the image to enlarge the photo, you'll see that the temperature limit on the control is set to about 140 °F.
[Click to enlarge any image]
Our second photo (above right) shows a limit switch used on direct vent Energy Kinetics System 2000 boiler installed in 2004. Click to enlarge the right hand photo and you'll see that this limit control is set to keep the boiler temperature between 96 °F. and 102 °F. A dab of red paint show at the 5'o-clock position on the dial enables the service technician to detect if someone has adjusted the control off of its factory setting.
When a heating boiler uses a tankless coil to produce domestic hot water, a third single-function control may be installed for that purpose. In this photo a Honeywell limit control switch is being used to monitor hot water temperature at the tankless coil which is in turn mounted on a steam boiler of an older home in Portland, Maine. You can see the black-handled mixing valve in the lower right of this photo.
Cold water from the building is entering the tankless coil via the bottom pipe (green corrosion) and hot water, heated by the coil is leaving at the upper part of the tankless coil, where it turns downwards to enter the left side of the mixing valve.
Additional cold water is permitted to enter the bottom of the mixing valve, and tempered (non-scalding) hot water then leaves at the right side of the mixing valve in this photo.
More information about tankless coils, how they work, what goes wrong, and their controls, is at TANKLESS COILS.
Use of Two Individual Single Limit Control Switches to Control Heating Boiler Hi and Low temperature settings
On heating boilers where individual limit controls are installed, you will find two similar devices, but mounted at different locations on the boiler, controlling the boiler's HIGH limit, or cut-off on a call for heat, and the boiler's LOW limit or cut-on point as the boiler water temperature falls.
We noticed three individual limit controls on this steam boiler in a photo contributed by reader H.H. who was discussing expansion tank draining. There are two strap-on limit switches on the riser pipe at right, and an immersion-type limit switch that has been added over a plumbing tee atop the boiler behind and to the left of the steam gauge. I'm not sure that that immersion limit switch is installed according to the manufacturer's instructions. They may want the switch mounted directly on the boiler not on a tee and riser above the boiler - just speculating.
An older type of aquastat used to set boiler temperature limits was strapped to the hot water riser pipe close to the top of the heating boiler. This device is shown in Carson Dunlop's sketch and in our photograph above. [Click any image to see an enlarged version.]
Rather than a temperature probe inserted directly into the heating boiler's water (as used by modern aquastats) the strap-on type aquastat relies on metal-to-metal contact between the control and the boiler water riser pipe.
If your heating system is controlled by a strap-on aquastat such as shown here in Carson Dunlop's, you'll want to check that it has remained securely in place.
If the aquastat becomes loose its contact with the hot water pipe is lost and the system is unsafe.
How to test the limit control switch
Reader question: How do I test my Operator Limit Control.on my Lochinvar boiler to see if it is bad? - Kelley 12/15/2012
Most single function limit controls do not have owner-accessible test functions, buttons, or devices. Here are some simple tests that a trained heating service technician might do with a single function limit switch:
Reader question: where to buy a Klixon replacement limit control for an American Standard heating boiler
Reply: Klixon - Sensata Snap-Action thermostatic sensors for HVAC/R applications
Todd, I don't know if the original Klixon limit controls you describe are still available, but the company is certainly around. You can contact the manufacturer at:
Sensata is a huge company, with offices world-wide, so you'll want to make clear what you want so as to be directed to the proper supply outlet without a lot of arm waving. The Klixon type limit controls rely on a snap-action temperature sensitive electronic switch that may be replaceable if that's all that's failed.
Send me sharp photos of the parts you seek and I may be able to comment further - use the CONTACT link found at page bottom or top.
For forced air furnaces the company describes their HIGH TEMPERATURE LIMIT THERMOSTATS - 1NT Series “Stat-on-Stilts”™ Extended Airstream Mount for Gas and Electric Furnaces . I found this by searching the company's site for "furnace limit control". Designed as a safety switch for gas and electric furnaces the Sensata “Stat-on-Stilts”™ may be used anywhere a temperature switch must be mounted remotely from electrical terminations. The most common application is as the primary temperature limit in gas furnaces and unit heaters.
At below left you can see Sensata's Klixon snap action thermostat switch examples and at below right their intresting "Stat-on-Stilts" sensors. But to choose the correct product you'll need to consult the limit switch manufacturer directly.
For hydronic boilers the company describes Thermal cutouts includine the MA10, TH10, TH11, & TH21 and heating line break thermostats include the 20600 Series and 20490 series. Also see FURNACE FAN CYCLES DURING HEAT where we discuss an example of using a snap-action heat sensing switch in furnaces, the Termo-o-Disc fan limit control. In that article we list sources of snap action type thermostat switches and controls for HVACR equipment.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.