Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR HANDLER / BLOWER UNITS
AIRBOUND HEAT SYSTEM REPAIRS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
CIRCULATOR PUMPS & RELAYS
CONVECTOR HEATERS - HYDRONIC COILS
COOL OFF HEAT, Thermostat Switch
DEFINITION of Heating & Cooling Terms
DIAGNOSE & FIX AIR CONDITIONER / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC HEAT, DIAGNOSIS, REPAIR
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRICAL POWER SWITCH FOR HEAT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON Thermostat Switch
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN LIMIT SWITCH
FLOODED HEATING EQUIPMENT REPAIR
HEATING LOSS DIAGNOSIS-BOILERS
HEATING LOSS DIAGNOSIS-FURNACES
HEATING SYSTEM INSPECT DIAGNOSE REPAIR
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MANUALS & PARTS GUIDES - HVAC
NO HEAT - BOILER
NO HEAT - FURNACE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
PULSE COMBUSTION HEATERS
Reset Switch - Heater Primary Control
Reset Switch Broken - Quick Repair
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
THERMOSTATS, WATER HEATER
THERMOSTATIC EXPANSION VALVES
Heat won't turn off - troubleshooting & repair: this article explains where and how to turn off the heat if simply turning down the thermostat does not stop un-wanted heat coming from heating radiators or baseboards.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
I live in a rental property. It is a three floor house, which old school round honeywell thermostats on each floor. All three of these thermostats are turned down as low as they can go. It's nice out now, but our heaters still leak heat. The landlords have told us we need to turn the heat off, that there is a "slidey switch" on each of the three thermostats to turn them off.
I live in New York, they live in colorado and don't specifically remember how to do it, even when I sent them cell phone pictures of the unit with the lid off.
The only "slidey thing" I see is beneath the thermostat cover (I removed it to look) - it is what you describe at HEAT ANTICIPATOR Adjustment (Photo at left). The arrow is in the dead center of the scale. Should we adjust it? If not, do you perhaps have some idea how we may succeed in no longer wasting money on heating bills while we have three fans blazing per room? -- Johan J. Sheridan
Guide to Turning off the Heat in a Building - When the Radiators or Baseboards "won't turn off"
DO NOT try to turn the heat on or off by changing the adjustment shown in our photo and described by the question above. That's the heat anticipator not an on-off control for heat. The heat anticipator is a fine-tuning adjustment inside the thermostat and not something that a homeowner should change. The heat anticipator is explained at HEAT ANTICIPATOR Adjustment.
Just below we discuss several considerations in turning off un-wanted heat in a building. This article addresses problems with thermostat settings, non-working check valves or flo-control valves, and how to force the heat to "turn off". Separately at RADIATORS we discuss the problem of individual radiator valves that don't operate to allow turning a hot water or steam radiator on or off. Also see ENERGY SAVINGS in buildings.
Turning Off Heat at Thermostats that Set Temperature Only - Lack an "on-off" Switch
Thermostats contain an internal temperature sensor which compares the air temperature at the thermostat to the temperature called-for by the user, turning the cooling (or heating) equipment on or off as appropriate.
Because some controls are used in common on hot water heat, hot air heat, and steam boilers, readers should see these other articles: see BOILER CONTROLS & SWITCHES, and also see BOILER COMPONENTS & PARTS for a detailed list of heating boiler controls, other heating system components, parts such as circulator pumps & draft regulators. If your building uses warm air heat, see FURNACE CONTROLS & SWITCHES. If your building uses steam heat see STEAM HEATING SYSTEMS.
Readers needing to find and fix un-wanted air leaks, heat losses, or other energy wasters should see HEAT LOSS DETECTION TOOLS. Readers should see ENERGY SAVINGS RETROFIT CASE STUDY and also see HEAT LOSS DETECTION TOOLS and INSULATION INSPECTION & IMPROVEMENT for energy saving retrofit detailed guides. Also see GAS PIPING, VALVES, CONTROLS for more details on how to inspect and test LP and natural gas piping, controls, valves, and tanks.
Turning Off Heat at the Electrical Power Switch or Service Switch
Turning Off Heat at Thermostats that Include a Cool-Off-Heat Switch on the Thermostat
Why Are the Baseboards or Radiators Hot Even Though the Thermostat is Set Higher than Room Temperature? Un-wanted Gravity or Convection Circulation of Hot Water
If electrical power switch to a hot water heating boiler is in the on position (see ELECTRICAL POWER SWITCH FOR HEAT) and the room thermostat is set above room temperature, the heating system (hot water or steam) boiler or (warm air) furnace should not run.
But for hot water heating systems (baseboards, radiators), other defects could cause or permit hot water to circulate through the heating system by "gravity" (convection, warm water rising on its own through the heating piping) even though the thermostat is not calling for heat.
The problem, if this is occurring, is usually that a check valve (photo above-left) (found internal to some circulator pumps, or external as a physical device) intended to prevent hot water from circulating on its own - when the circulator pump is off - is either set to a "forced open" position, or it has become defective.
If that's the problem (diagnosed by a heating and service technician) then the valve or circulator needs to be replaced. While waiting for that repair to be made, you can still turn off the heat, by turning off electrical power to the boiler.
See CHECK VALVES, HEATING SYSTEM for more about these devices.
What if Our Heating Boiler Also Makes Hot Water for Washing?
Watch out: if your heating boiler is also used to make domestic hot water for washing and bathing, through a tankless coil (see Indirect-fired Water Heaters), then turning off the boiler will mean you'll also lose hot water for bathing.
If that's the case, but you're getting heat when you're not asking for it, then the check valve, flo-control valve, or similar problem (or a faulty thermostat itself) needs to be diagnosed and repaired.
How to Save Heating Cost & Air Conditioning Costs by Thermostat Adjustments
Substantial heating or air conditioning cost savings can be achieved by manually setting back your thermostat when the building is unoccupied or when occupants are asleep. The thermostat is set several degrees (or more) cooler during heating season or warmer during cooling season.
The settings of thermostat "mode" switches into "heating" or "cooling" and the use of other thermostat switches to control an air conditioning blower fan or heating system blower fan are discussed in detail at Other Switches on a Room Thermostat.
Lots of websites offer calculators that will tell you how much you'll probably save in energy costs for every degree you set back your heating or cooling thermostat. Just don't set the thermostat down so low that you suffer costly damage from freezing pipes in winter or mold from high humidity in summer.
Frequently Asked Questions (FAQs) about controlling building heat: when un-wanted heat is received or when heat just won't turnoff as it should
Question: how can I keep people from turning up the thermostat?
I have a question. I have a daughter. she is 45. she is a toddler mentally. i need to stop her from turning on the heat all the time. it runs the bill sky high. there are political problems that make certain known solutions not possible. too late for spanking, no known way to stop her from turning on the heat all the time, cannot shut the heat off with switches, cannot pay the bill, cannot shut off electricity to the heat, its definately an interesting concept.
I basically mentally in your mind picture this: i have a 4 year old toddler who can reach the heat, and like a deviant keeps turning the heat on, but it's not deviant behavior it's incorrect behavior, its happening because of her medical situation related to thyroid, because of politics there is no known way to stop my 4 year old from turning on the heat and stopping the bill from being sky high. i must stop the heat and the bill from happening from my point of view.
Also, i refuse to believe there is No way to stop this from happening; theres gotta be a way, but danged if i know or can think of it or a way to stop her or the heat. is this crazy? i refuse to believe there is no way to stop her or the heat. theres gotta be a way.........help me on this fellas what am i missing here. - Anonymous 10/24/2012
Maybe a password protected digital thermometer?
Reply: how to prevent thermostat tampering: install a locking thermostat cover
Check with your heating supplier and almost certainly they can provide you withnan inexpensive clear plastic cover that screws to the wall, has vents toilet the thermostat sense room air temperature, and can be opened to adjust the thermostat by using a lock and key. You see these locking thermostat cover set ups often in offices and commercial buildings. It's an easy add-on feature to prevent thermostat adjustments by people who should keep their mitts off.
For more about wall thermostats, take a look at THERMOSTATS, HEATING / COOLING
Question: how do I fix a thermostat that I have to set lower than the level of heat I want?
My traditional honeywell simple dial-type thermostat on the wall has two pointers and two temp. scales. However I have to set it on 60 degrees to get heat temp to 70 degrees. What can I do? It was working fine until my condo changed the air/heating system this summer. - Jeannette 1/23/2013
Reply: check these reasons for a room thermostat that keeps calling for heat
On most two-scale room thermostats, one scale reads the current or actual room temperature while the other scale is the set temperature - and is adjustable. When you move or adjust the thermostat to call for a different room temperature you will see the scale pointer move to your new setting on the "set" scale.
You are describing having to set the thermostat lower (60F) than the desired temperature (70F) to get the proper level of heat in your home. In other words, you say that the room gets too hot - hotter than you asked-for. Here are some things that would cause that problem:
Questions & answers or comments about troubleshooting too much heat or heat that won't turnoff in a building.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.