Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC Plexvent / Ultravent RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Forced air heating or cooling air handler troubleshooting: blower fan won't shut off: This article describes what to check if the furnace or forced air blower fan does not stop when you expect it to do so. These same diagnostics also aid in air conditioning blower assembly diagnosis when an A/C blower continues running. We explain what switches or controls may be set improperly or what else, such as a shorted wire, can cause continuous HVAC fan operation.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Blower Fan Won't Stop: What to Check if your Furnace Fan Runs Continuously - (the fan won't shut off on its own)
First, confirm that the room thermostat is not calling for heating or cooling. In the heating season, just set the thermostat(s) to the lowest setting and confirm that room temperature is above that point. In the cooling season do the opposite - set the thermostat to its highest setting and confirm that room temperature is below that point. You have told the thermostat to turn off the HVAC equipment.
If the equipment was running give it three to four minutes to shut down.
Next: If the blower just keeps running no matter what, there are two places to check switch settings before calling your heating or air conditioning service company in response to a furnace fan or air conditioning fan that just keeps running without stopping:
1. At the room thermostat: the FAN-AUTO-OFF or FAN ON/OFF switch on the room thermostat should be checked.
Those problems are explained at THERMOSTAT WON'T TURN OFF.
Take a look at the fan limit control switch. Before pulling the cover off of the switch, just see if the switch includes a control such as the white push-pull switch like the white device shown at the lower left in our photo.
Depending on the position of this switch (pushed-in or pulled out) the fan may be on manual override - causing the fan motor to run continuously.
Check the printing on the switch face to see if you should push the switch in or pull it out to leave the blower on "Auto". ("Man" or "Manual" would be forcing the fan to run.)
Which way to set the manual furnace or air conditioner blower fan switch:
Usually: "Push-in" position on this (Honeywell) fan limit switch is for continuous fan operation and "Pull out" position is for automatic fan operation.
There are some reasons (explained at BLOWER FAN CONTINUOUS OPERATION) to leave the blower fan on continuously for long periods, such as to use an air filtering system to improve indoor air quality. And in some buildings we may run the blower continuously for more even or better conditioned (heated or cooled) air distribution.
What Else to Check if the Blower or Furnace Fan Won't Stop
On the off chance that someone has inadvertently mis-connected or shorted fan control wires at the fan limit switch, also check out FAN LIMIT SWITCH INSTALLATION.
On the chance that there is a shorted thermostat wire, a problem that can also cause the A/C or warm air furnace fan to run continuously see THERMOSTAT WON'T TURN OFF.
Details about the manual FAN ON or FAN AUTO ON switch right at the furnace or air handler at the manual at BLOWER FAN CONTINUOUS OPERATION.
This article series answers most questions about central heating system troubleshooting, inspection, diagnosis, and repairs. We describe how to inspect, troubleshoot and repair heating and air conditioning systems to inform home owners, buyers, and home inspectors of common heating system defects.
Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.