InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Forced air heating or cooling air handler troubleshooting: blower fan won't shut off:
This article describes what to check if the furnace or forced air blower fan does not stop when you expect it to do so
. These same diagnostics also aid in air conditioning blower assembly diagnosis when an A/C blower continues running. We explain what switches or controls may be set improperly or what else, such as a shorted wire, can cause continuous HVAC fan operation.
Blower Fan Won't Stop: What to Check if your Furnace Fan Runs Continuously - (the fan won't shut off on its own)
First, confirm that the room thermostat is not calling for heating or cooling. In the heating season, just set the thermostat(s) to the lowest setting and confirm that room temperature is above that point. In the cooling season do the opposite - set the thermostat to its highest setting and confirm that room temperature is below that point. You have told the thermostat to turn off the HVAC equipment.
If the equipment was running give it three to four minutes to shut down.
Next: If the blower just keeps running no matter what, there are two places to check switch settings before calling your heating or air conditioning service company in response to a furnace fan or air conditioning fan that just keeps running without stopping:
1. At the room thermostat: the FAN-AUTO-OFF or FAN ON/OFF switch on the room thermostat should be checked. The fan control should be set to AUTO. You can try turning the switch to OFF too.
Details of checking the thermostat's FAN-AUTO-OFF or FAN-ON switch position when the furnace (or air conditioning) fan won't stop running are
at FAN WONT STOP - THERMOSTAT SWITCH
Other snafus such as a shorted thermostat wire can also cause the A/C or warm air furnace fan to run continuously.
2. At the furnace or air conditioner air handler or blower unit: the FAN LIMIT SWITCH may include a switch that manually keeps the fan running. We discuss this switch here.
Take a look at the fan limit control switch. Before pulling the cover off of the switch, just see if the switch includes a control such as the white push-pull switch like the white device shown at the lower left in our photo.
Depending on the position of this switch (pushed-in or pulled out) the fan may be on manual override - causing the fan motor to run continuously.
Check the printing on the switch face to see if you should push the switch in or pull it out to leave the blower on "Auto". ("Man" or "Manual" would be forcing the fan to run.)
Which way to set the manual furnace or air conditioner blower fan switch:
Usually: "Push-in" position on this (Honeywell) fan limit switch is for continuous fan operation and "Pull out" position is for automatic fan operation.
There are some reasons (explained
at BLOWER FAN CONTINUOUS OPERATION) to leave the blower fan on continuously for long periods, such as to use an air filtering system to improve indoor air quality. And in some buildings we may run the blower continuously for more even or better conditioned (heated or cooled) air distribution.
What Else to Check if the Blower or Furnace Fan Won't Stop
On the off chance that someone has inadvertently mis-connected or shorted fan control wires at the fan limit switch, also check out FAN LIMIT SWITCH INSTALLATION.
On the chance that there is a shorted thermostat wire, a problem that can also cause the A/C or warm air furnace fan to run continuously
see THERMOSTAT WON'T TURN OFF.
This article series answers most questions about central heating system troubleshooting, inspection, diagnosis, and repairs. We describe how to inspect, troubleshoot and repair heating and air conditioning systems to inform home owners, buyers, and home inspectors of common heating system defects.
Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Reader Question: Furnace fan keeps running with no heat coming from the furnace
2015/10/22 Anonymous said:
My fan keeps running with no heat on furnace. What can I do?
Reply: 6 steps to getting heat on when the fan runs but the furnace does not
If the furnace does not even try to run, that is if it never even starts, then follow these steps:
Check the thermostat settings to be sure that you are calling for heat (set-temperature is above room temperature).
See THERMOSTATS, HEATING / COOLING - home
Check for voltage at the oil burner primary control. Watch out: if you are not expert in safe use of electrical test tools you could be electrocuted - killed. Call an expert.
See VOLTS MEASUREMENT METHODS
Check for a bad primary control: If there is voltage to the primary control, no reset buttons are popped, and the thermostat is calling for heat (check that right at the primary control thermostat wires) then I suspect a bad primary control unit itself. At that point your heating service tech will perform her own tests and then if needed repair wiring or replace the furnace control.
Oil heat: see CAD CELL RELAY SWITCH
Gas heat: see the gas furnace controls cited above at step 4.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Support InspectApedia.com & See Fewer Advertisements
From Google's Contributor website: Contribute a few dollars each month. See fewer ads. The money you contribute helps fund the sites you visit.