Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATOR, DAMPER, BOOSTER
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER FLAME & NOISE DEFECTS
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC PLEXVENT ULTRAVENT RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
RESET SWITCH, HEATER PRIMARY CONTROL
RESET SWITCH, ELECTRIC MOTOR
RESET SWITCH, STACK RELAY
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: HEATING SYSTEMS
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
Heating zone circulator pump won't start or seems stuck: how to diagnose & fix a heating zone circulator that will not run when it should.
This article series describes how to diagnose & fix circulator pump problems on hot water or hydronic heating systems.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Reader question: My heating zone circulator won't start-up
(Oct 29, 2011) Mark said:
I have a Weil-McLain furnace/boiler model no. CGM-5-PI. I just turned on the heat system two days ago and I noticed the circulator pump is not spinning its motor. I bleed all the valves on all the radiators.
The two upper levels get heat on the radiators, but the one on the entrance level is not getting heat. Is this caused by the pump not working? Is there any danger/risk of running the heat with the circulatory pump not working?
How much would it cost to replace the circulatory pump? Any information would be helpful. Thanks.
(Nov 24, 2012) annonymous said:
circulator pump goes on when heat called, runs thru cycle, but doesn't come again.....burners come on,but not circulator which in turn system goes off
Mark if the circulator pump won't start when the boiler temperature is sufficently high that it should, you would check:
1. the thermostat is calling for heat and the room temperature is below the thermostat set temperature
2. the boiler temperature is above the circulator cut-in temperature controlled by the aquastat
3. the circulator pump has power
4. the circulator relay has power and is switched "in" or callling for the circulator to run
5. the circulator pump itself is not damaged, jammed, frozen
In answer to your cost question, Grundfoss & Bell & Gossett heating zone circulator pumps are typically in the range of $100. to $300. depending on the pump model.
Question: should the circulator pump come on right away?
(Oct 27, 2011) Steve said:
My daughter bought a house with hot water heat. I bled the radiators, oiled the circulator pump and turned up the thermastat in order to check the operation. The circulator pump did not start to opereate until the boiler temp read 150 degrees.
The pump is hooked up to an aquastat (the thermastat located against the pipe exiting the boiler) which is set at 140 degrees. The radiators do heat up. Shouldn't the pump come on right away?
Steve, on a very common hot water heating system installation the aquastat is a combination control that includes a HI LO and DIFF setting - the LO and DIFF settings control the boiler when no heat is being called for and maintain heat in the boiler to provide domestic hot water through a tankless coil - that might not even be present or not in use on some installations.
If that general control and approach are in use on your system and if your system is hooked up in the manner typically used in the U.S. (not in Canada) the circulator won't turn on until the temperature is sufficiently high in the boiler.
Continue reading at CIRCULATOR OPERATION CHECKS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References