Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AFUE DEFINITION, RATINGS
AGE of HEATERS, BOILERS, FURNACES
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BANGING HEATING PIPES RADIATORS
BOILER CONTROLS & SWITCHES
BOILER LEAKS CORROSION STAINS
BOILER NOISE SMOKE ODORS
BOILER OPERATING PROBLEMS
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CHEMICAL TREATMENTS for BOILERS
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CIRCULATOR PUMPS & RELAYS
DEFINITION of HEATING & COOLING TERMS
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DRAFT MEASUREMENT, CHIMNEYS & FLUES
DRAFT REGULATORS, DAMPERS, BOOSTERS
FILTERS, OIL on HEATING EQUIPMENT
FIRE SAFETY CONTROLS
FLOODED HEATING EQUIPMENT REPAIR
FLUE VENT CONNECTORS
FREEZE-PROOF A BUILDING
FUEL OIL TYPES & CHARACTERISTICS
FUEL UNIT, HEATING OIL PUMPS
GAS BURNER Flame & Noise Defects
GAS PIPING, VALVES, CONTROLS
GAUGES ON HEATING EQUIPMENT
HEATING COST SAVINGS METHODS
HEATING LOSS DIAGNOSIS-BOILERS
HEATING OIL PIPING TROUBLES
HEATING SYSTEM INSPECTION GUIDE
HEATING SYSTEM NOISES
HIGH EFFICIENCY BOILERS/FURNACES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MOTOR OVERLOAD RESET SWITCH
NO HEAT - BOILER
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL PUMP FUEL UNIT
PUFFBACKS, OIL BURNER
RELIEF VALVES - STEAM TP VALVES
Reset Switch - Heater Primary Control
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCHES - Flue Gas Detection S
STACK RELAY SWITCHES
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: Heating System Videos
ZONE VALVES, HEATING
Heating zone circulator pump wont' stop running: this article explains how to diagnose & fix a heating circulator pump that runs even when we are not asking for heat. We explain that in some heating system designs, as long as the boiler has power the zone circulator is wired to run constantly - which can give some advantages in comfort and freeze proofing. But in areas where the heating system is not normally installed with an always-on circulator, if the circulator won't shut off something's wrong and we want it fixed. Here we discuss troubleshooting and fixing forever-on circulator pumps.
This article series describes how to diagnose & fix circulator pump problems on hot water or hydronic heating systems.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Question: un-wanted heat: why do zones get hot when we're not calling for heat?
(Mar 2, 2014) Jared said:
Why does heat come out of zones where thermostats are not calling for heat?
Jared, usually the problem you describe is traced to a check valve malfunction at the heating boiler or at the circulator pump (depending on what equipment is installed). Hot water can circulate by natural convection (warm water rises in pipes, cold water falls) even when the circulator is off.
Reader Question: circulator pump won't stop: the circulator pump stays on all the time
(Oct 23, 2011) Mary said:
Is it normal for a pump to stay on all the time? We have a new system installed and the pump wont go off at all. Thermostat set to 70 and burning smokeless egss.
(June 5, 2012) Greg said:
Didn't see anything listed above for this but it seems our hear came on last night and went off, but apparently the circulator was still running 2 hours later. So, we decided to turn it off at the switch. Any ideas what could cause this to happen? Before I left for work, i turned the switch back on, i heard the vent open on the pipe leading to the chimney then the furnace kicked on. In less than 5 minutes the furnace turned off but the circulator kept running.
4/23/2014 Chris said:
When the day's are warm and I turn off the heat do I shut the circulator pump off also?
Chris, when you turn off the heating system at its power switch your circulator pump should shut off on its own. If it does not then there is a wiring or control SNAFU that we need to discuss.
Normally you shouldn't have to do even that. If house temperatures are above the thermostat set temperature the thermostat will not call for heat and the heating system as well as its circulator should not run. If you are seeing something else happening let's figure that out. Tell me.
4/21/2014 Dan, the heat was turned off this past Saturday. The circulator pump would still turn on though the heat was switched off on the thermostat. My centralized air and heat are on the one thermostat so I need to turn off heat to power on the central air unit.
Chris, you don't say where you are located; in some areas including much of Canada the hydronic heating system practice is to run the circulators continuously and allow the thermostat to simply turn the boiler on and off - an approach that tends to give more even heat and reduces the risk of heating line freeze-up in a colder climate. In the U.S. installers usually wire the thermostat to turn on the circulator and allow the boiler temperature to turn the burner on and off.
When you switch from HEAT to COOL mode on your system it would make sense for the circulator to turn off as well as your boiler. If it's not doing that we need to look at how your thermostat and circulator are wired and controlled. If you're one of the Canadian type installations you will want to find the power switch to the circulator pump and just flip that off as well, remembering that in the fall you'll need to turn it back on.
Part of the answer to this question depends on what heating system installation practices are common in your area. In the U.S. some areas a hydronic heating system is wired so that the thermostat simply turns the circulator pump on - ostensibly to move hot water from the boiler to the heated area.
In turn it's the temperature of the water in the system that, monitored by the boilers aquastat, turns the burner on and off.
If a problem at the heating boiler prevents its operation (such as no oil, or off on safety reset), the circulator may just keep spinnining away but no heat arrives in the heated area.
Take a look at the boiler to see why it's not running, starting at DIAGNOSE & FIX HEATING PROBLEMS-BOILER
Dan, I live in Hudsonville,Michigan.
Chris it's possible that the circulator relay on your boiler's aquastat or primary control (or circulator relay if you have multiple circulators) is stuck "on" and needs repair or replacement. Meanwhile just flip off power to the boiler - that should turn off the circulator. If it doesn't then look for an additional electrical switch.
Dan, my furnance is a Burnham Holiday. It's natural gas. It's an old unit. There is one circulating pump with five Honeywell zone valves and five Honeywell thermostats. These thermostats are the old round types.
Chris in a single circulator system the circulator is usually turned on via a relay that is found inside the primary control or aquastat.
If your thermostat is not calling for heat the circulator ought not be running.
It might run if the thermostat wires are shorted together on any of the circulators controlling any of the zones.
The circulator might also run if any of the zone valves has a failed end-switch. When the thermostat calls for heat it activates a small motor in the zone valve that causes the valve to open. Once the valve reaches its full-open position, the valve closes an "end switch" that in turn activates the circulator pump itself.
Temporarily you can turn off the circulator by turning off power to the boiler - that should turn off the boiler motor and primary control and circulator pump.
To debug the problem I would check that all of our five thermostats (controlling each of the five zone valves) is OFF - NOT calling for heat (room temp is above thermostat set temp - or the thermostat is simply disconnected)
As needed I'd disconnect thermostat wires at the zone valve, and I'd check the primary control relay condition.
Keep me posted
Dan, I'm curious as to why the the furnance and pump are even operating. I have the five thermostats set at sixty-four and the room temperature on every thermostat reads at seventy. Right now as I write the pump is working and the furnance is on but the burners are firing. The room temps on every thermostat still read seventy. Only one of the thermostats has a on,off switch.
Chris I have said too much and thus not been clear.
Let's diagnose just what's wrong by disconnecting things, one at a time.
I suspect a bad relay, bad zone valve control, or thermostat wires shorted together somewhere. Shorting TT wires together is the same as a thermostat calling for heat.
Watch out: one can also be fooled, especially on hot water heating systems that use very quiet circulators such as some Taco brand units: the circulator may not be running at all. Hot water could be circulating by convection, thus also causing the boiler to run as cooler water returns to the boiler by convection.
It's easy to check this. Turn off power to the circulator pump (but not the boiler). If baseboards or radiators still are getyting hot AND the thermostat is not calling for heat (or has been disconnected entirely) then see CHECK VALVES, HEATING SYSTEM
Keep me posted
Circulator Pump Diagnostic Q&A
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References