Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCT SYSTEM & DUCT DEFECTS
GAS LP & NATURAL GAS SAFETY HAZARDS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL TANKS
HEATING SYSTEM TYPES
MANUALS & PARTS GUIDES - HVAC
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL SPILL CLEANUP / PREVENTION
SOLAR HEATING SYSTEM DESIGNS
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: HEATING SYSTEMS
WOOD-OIL COMBINATION HEATERS
WOOD STOVE OPERATION & SAFETY
Heating boiler gauge replacement: this article describes the steps in replacing a pressure or temperature gauge on a hot water (hydronic) boiler or on a steam boiler.
We give two different approaches to boiler gauge replacement, a wet process that is done without draining the boiler and a dry gauge replacement process that requires draining water out of the heating equipment.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
My pressure temperature gauge is leaking on my Mclain p-wtgo-3 oil fired boiler. It seems like an easy fix.
How to I safely drain and refill the water in the boiler to effect this repair? By the way, the boiler is only about 3 years old. It doesn't speak well for Mclain products. - J. Wojciechowski
Reply: Basic outline of how to replace a heating boiler pressure/temperature gauge
J. Wojciechowski, You're right that just replacing the pressure/temperature gauge itself is usually mechanically simple - as long as you buy an OEM part you'll have exactly the same item as before.
At left we illustrate a standard hydronic heating boiler replacement gauge that reads pressure and temperature. This replacement boiler gauge is produced by the Watts Regulator Company - in the U.S. see www.wattsreg.com or in Canada see www.wattsca.com for details.
Basically to replace a heating pressure/temperature gauge one would:
Wet process vs draindown process for boiler gauge replacement
At this point there are 2 choices:
The "wet" process for changing a heating boiler gauge (this process can avoid having to purge air from the heating system)
The "dry" drain-down process for changing out a heating boiler gauge (this procedure will require purging air from the heating system)
How to Return the boiler to service after Boiler Gauge Replacement
With new boiler pressure/temperature gauge in place, you will need to:
Continue reading at GAUGES, HYDRONIC BOILER or select a topic from the More Reading links shown below.
Suggested citation for this web page
BOILER GAUGE REPLACEMENT at InspectApedia.com - online encyclopedia of building & environmental inspection, testing, diagnosis, repair, & problem prevention advice.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References