Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO SYLVANIA ELECTRICAL PANELS
FPE Stab-Lok® identification from electrical panel door labels: this article describes how to identify Federal Pacific Stab-Lok® Electric Panels and circuit breakers in buildings by information printed on labels affixed to the electrical panel cover, door, or interior. It is information for building inspectors, home buyers, home owners, electricians concerned with hazards of Federal Pacific Electric Stab-Lok® circuit breakers and service panels.
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Look for the words "Stab-Lok® " However some panel labels such as the one shown here will not, at the label top, contain the words "Federal Pacific" or "Stab-Lok® ".
On those labels look at the bottom of the label for the words "Federal Pacific".
[Click to enlarge any image]
What if there are no labels on my electrical panel?
If an electrical panel has no exterior markings at all, it still may have labels inside - data that can be discovered by your electrician if the panel cover is removed. See IF NO LABELS for the procedure to follow where no electrical panels are present and there are no other identification marks on the panel.
Additional photographs of FPE Stab-Lok® Electrical Panel Identifying Labels
Photo of a Stab-Lok® Electric 150A panel door label FPE Model# C1410-14-150N1
Photo of a typical Stab-Lok® hinged panel door label - bottom section
Red-Centered FPE Stab-Lok® Cover Labels
Red Center Stab-Lok® panel upper red label on panel interior face FPE Model# RHM108M - California
Red Center Stab-Lok® panel lower paper label on panel interior face FPE Model# RHM108M panel label - California
Stab-Lok® Load Center panel label - California Federal Pacific Electric
FPE Model# L120-40 - Texas - M. DeMuth
Here is John Spencer's photo of the interior label of a Federal Electric panel catalog No. 116 showing that this early model electrical panel used the "Stab-Lok® " "E" bus and "F" bus designs in this product.
Look at the bottom of the label just above our red (C) notice and you will see that the "F" and "E" Stab-Lok® bus layout was used.
See FEDERAL ELECTRIC PANELS for more identifying photographs of Federal Electric Panels.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about FPE Stab-Lok electrical panel door labels
Questions & answers or comments about how to identify Federal Pacific Electric equipment from equipment labels.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References