Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
BOOKSTORE - ELECTRICAL
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
FEDERAL PACIFIC FPE HAZARDS
GFCI PROTECTION,Testing GFCIs AFCIs
Hertz - Definitions of KHz MHz GHz THz
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LOW VOLTAGE BUILDING WIRING
MAIN ELECTRICAL DISCONNECT
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
ZINSCO SYLVANIA ELECTRICAL PANELS
This document provides photographs and descriptions of FPE Stab-Lok® circuit breakers of various types and ages in order to assist in their identification. Page top photo of an FPE Stab-Lok® circuit breaker is provided courtesy of electrical panel researcher David Carrier.
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Watch out: Safety warning - while opening the hinged door provided for consumer use to access and reset the breakers is permitted, because there is risk of dangerous or even fatal electric shock in any electrical panel interior, only an expert should actually remove the front cover.
See our complete list of Federal Pacific Electric (and its various name forms) electrical panels and circuit breakers found at FPE Stab Lok IDENTIFICATION. The molded-case FPE Stab-Lok® patent numbers seen on the FEP circuit breaker sides and FPE Stab-Lok® circuit breaker label close ups are at FPE BREAKER LABELS.
Stab-Lok® Circuit Breaker Photographs
Jeff Weissman contributed the photo below-left of a gray FPE Stab-Lok® circuit breaker. While the most common molded case circuit breaker is black in color, FPE Stab-Lok® breakers have been obseved in this gray color, an odd camoflage color mix that may have been a "one-off" fooling around on the production line.
On occasion a Federal Pacific Stab-Lok® Electrical Panel or Breaker manufacturing factory worker might experiment with a mix of plastics in the circuit breaker case molding machine, photo courtesy of J. Bolton. Older FPE Stab-loks may have a brown molded case (see photos further below).
Below we show two sides of another "camouflage" multi-colored plastic case FPE Stab-Lok® circuit breaker provided by researcher David Carrier (May 2010). Notice that the two sides of the case were produced in different processes and most likely at different times. This mix-and-match product might be an indicator of frequent adjustments and experiments on the FPE Stab-Lok® equipment production line.
The FPE Stab-Lok® GFCI breaker at above left was for sale on eBay. FPE NB type breakers (above right) use a screw connection at the bus.
Below are photographs of a 40-Amp FPE Stab-Lok® breaker that help identify FPE Stab-Lok® equipment. Provided courtesy of electrical panel researcher David Carrier .
Pre-1970 FPE Stab-Lok® Circuit Breakers
Below are photographs, courtesy of electrical panel researcher David Carrier, that help identify older pre-1970 FPE Stab-Lok® circuit breakers that have the properties we have described at FPE Pre-1970 STAB-LOKS OK?
Below, two views of a 50-Amp double pole pre-1970 FPE Stab-Lok® circuit breaker. Below-left, the breaker bus-bar connectors; Below right, the FPE Stab-Lok® breaker wire connectors.
You'll notice that these older FPE Stab-Lok® models have copper parts and a hexagonal toggle switch.
At left our photo provides a side view of a similar-vintage 15-Amp single pole FPE Stab-Lok® circuit breaker discussed at FPE Pre-1970 STAB-LOKS OK?
The molded-case FPE Stab-Lok® patent numbers seen on the breaker sides and FPE Stab-Lok® circuit breaker label close ups are at FPE BREAKER LABELS.
At left: internal parts of an older, hexagonal toggle-switch FPE Stab-Lok® circuit breaker, courtesy of researcher David Carrier.
Below left and right, photos of a pre-1970 FPE Stab-Lok® 40-Amp double pole circuit breaker.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers on how to identify Federal Pacific Electric Stab Lok or FPE Stab Lok circuit breakers.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References