POST a QUESTION or READ FAQs about the purchase of replacement FPE Stab Lok circuit breakers: where they are obtained, where they are made, are they tested, how they may be expected to perform, whether or not you should use them
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
UBI-brand FPE Circuit Breaker Replacement test results:
Current results of overcurrent tests performed on UBI circuit breakers sold as replacements for FPE Stab-Lok circuit breakers: as of April 2017, testing of 420 UBI circuit breakers show overall a high failure rate of about 42% - higher than FPE circuit breakers, and significantly-higher than the performance of most other brands and designs of circuit breakers. In addtion, two-pole UBI breakers frequently jam after which they will not trip at any level of overcurrent.
This article series gives expert advice about replacing FPE Stab-Lok® circuit breakers - Federal Pacific Electric Stab-Lok® breakers and
discusses how to repair FPE StabLok Panels and circuit breakers for actual improvements in electrical safety.
Replacement FPE Stab-Lok® circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok® electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture. We do not sell circuit breakers nor any other products.
UBI Replacement Circuit Breaker Independent Test Results - 2017 Update
UBI replacement circuit breakers like the equipment shown at the top of this page are sold as replacement units for FPE Stab-Lok or Federal Pacific Electric or Federal Electric or Federal Pioneer circuit breakers, and for other electrical panel brands including for Zinsco circuit breakers.
The photo of gray 15, 20 and 50A circuit breakers shown just above/left illustrates UBI-brand replacement circuit breakers, provided by reader E.K. (2014) who included the image in an FPE UBI breaker field failure report described at FPE FAILURE FIELD REPORTS.
Page top photo of smoking UBI - FPE circuit breaker: The FPE-replacement UBI circuit breaker shown at the top of this page smokes without tripping off when subjected to 60A or 400% of rated current.
Smoke (red arrows) is coming out of the toggle slot at the top of the breaker and out of the arc chute (lower right). The orange arrow points to a burn spot near the breaker bottom where internal parts are overheating.
[Click to enlarge any image]
The test conditions that led to this smoking breaker that did not trip in response to an overcurrent are explained by Dr. Jess Aronstein:
One of the 15-amp 2-pole breakers [among a group of UBI breakers undergoing independent testing] went to 200% of rated current without tripping. Typically, when a circuit breaker does not trip at 200% it is not a calibration error, but is most likely due to jamming of the mechanism. It happens most often on the 2-pole breakers.
I ran the jammed 15-amp breaker up to 60 amps, 400% of rated current. It still did not trip. The photo below was taken just before I shut it down. - J.A. by private email to editor 2017/03/04
Results of Independent UBI-FPE Circuit Breaker Tests
A reader E.K. corresponded with us beginning in 2014 that in 2004 his condominium association replaced all of the old original FPE circuit breakers in the condominium complex with UBI replacement breakers. The reader explained that he discovered that the new replacement UBI circuit breakers were faulty.
The reader quoted below, a resident of Northgate Gardens, a large condominium complex in Waltham MA, subsequently provided a collection of UBI circuit breakers to Dr. Jess Aronstein for independent testing. Results are reported below.
The same person who sent these UBI circuit breakers to Aronstein for testing is an electrical engineer (EE) who had one circuit breaker passing about 200% of rated current without tripping. He had his panel changed and the condo board is considering making it a mandatory change in all other units. (They "upgraded" from the original FPE breakers some years ago.)
In a letter to the condominium board the reader's comments included this remark:
In my other condo we also had the same type of electrical panels; back in 2003 we had a fire inside a wall of one of the units which caused extensive damage, we were fortunate that no one was injured. - Anon [by private email]
[Editor's note: the 2003 fire referred to by the reader's comment took place at a different facility, not at Northgate Gardens in Waltham. However that distinction does not preclude the occurrence a fire or other loss involving an FPE electrical panel wherever that equipment remains installed.]
Below we provide two tables of independent test results for UBI-Brand replacement circuit breakers for FPE panels. The first table is a summary of test results to date while the second table provides more details of some of the tests.
Table I Summary of FPE UBI-Brand Replacement Circuit Breaker Failure Test Results
Table II - Example Subset of Table I Above: FPE UBI-Brand Replacement Circuit Breaker Failure Detailed Test Results1
Breaker ID & Ampacity
Breaker Type: Poles
UBI - FPE Replacement Circuit Breaker Tests: 2016-2017
9 failures @ 135% - 45% failure rate
Failure = failed to trip at 135% of rated current - the UL Standard requirement
2 failures @ 135% - 67% failure rate
Small sample size.
3 failures @ 135% - 50% failure rate
2 failures @ 200% - 33% failure rate
The 2 that failed to trip at 200% of rated current jammed, making them unlikely to trip at any current level.
UBI - FPE Replacement Circuit Breaker Tests: 2014
2 failures @ 135% - 67% failure rate
2 failures @ 135% - 100% failure rate
1 failure @ 135% - 100% failure rate
Notes to the table:
FPE-UBI Breaker Test data as of 2 January 2017
UBI FPE Replacement Breaker Test Comments from Dr. Aronstein:
Overall, half of the UBI breakers so far tested from Northgate Gardens failed to meet the industry (and therefore the NEC) safety standard requirement. The safety exposure due to these failures ranges from mild to severe (the 50-amp jammed breakers).
The test procedure that I use encompasses the UL 100% (should not trip), 135% (must trip within one hour), and the 200% (must trip) requirements. Breakers that fail to trip properly are on the test stand for more than two hours. A failing double pole breaker can take more than 6 hours to test. Based on the UBI circuit breaker failure rate experienced to date, I expect it to take about three weeks to complete testing of the first batch that you have sent.
The more breakers that are tested, the more certain the conclusion will be -- from a statistical standpoint -- and the more likely it will be that corrective action will be taken by other homeowners and by responsible government agencies.
So, all readers are encouraged to collect and send samples of FPE replacement-type circuit breakers.
Older FPE-UBI Breaker Test Data: 3 December 2014:
Included in the lower portion of the table above are the December 2014 results of the tests on the UBI "Stab-Lok" (FPE replacement) circuit breakers that you sent. The breakers were tested at 135%, which is the required UL "must trip" level. Those that failed to trip at 135% (sustained for one hour minimum) were subjected to higher current until they tripped or reached 200% of rated current.
Five of the seven UBI breakers that the reader sent failed to trip as required at 135% of rated current. The sample size is small, but it may properly reflect the state of UBI's quality control at the time your breakers were purchased.
Overall, [J.A. had as of 12/14 ] tested 23 UBI Stab-Lok type breakers, with 8 failures. I have also tested 3 UBI Zinsco replacement type breakers, and all 3 failed to trip as required at 135%. [See ZINSCO CIRCUIT BREAKER TEST REPORT] That totals 11 failures out of 26 UBI breakers tested [in 2014].
William Tinker, licensed Master Electrician, Gilbertville MA, contributor of the UBI FPE circuit breakers whose test reports are described as of 2 January 2017. Contact: William Tinker, Master Electrician, 233 Upper Church Street, Gilbertville MA 01031 USA, Tel: 1-774-230-3837 Email WFTEC@aol.com
Jesse Aronstein, Ph.D., P.E., 2 January 2017, private email to E.K. and to D Friedman.
Jesse Aronstein, Ph.D., P.E., 3 Dec 2014, private email to E.K., B.G. and to D Friedman.
EK to J.A. & to the Editor, 2017/01/02: Thank you Dr. Aronstein, This gloomy initial result should prove to anyone who still believe it is a mistake to replace the FPE panels on the complex that all panels must be replaced.
I will do my very best to convince other electricians who work on the complex to donate the old breakers to this important study. So, stay tune, many more breakers will be shipped to you for testing. It will be helpful that when the final report will be published the names of the electricians who agreed to donate their old breakers will be mentioned.
EK to J.A. & to the editor: 2015/08/13 Thank you Dr. Aronstein, the failure rate is alarming (above 70%). These breakers have a sticker date of 2004. Did the breakers that failed the 135% test did eventually trip at higher current below 200% of the rated current? -Anon to J Aronstein & D Friedman, 12/3/2014, updated 13 August 2015
Kelly, Timothy P., "[FPE] ELECTRICAL PANEL [REPLACEMENT] CLARIFICATION" [PDF], letter, Kelly to Northgate Board of Trustees / Condo Association, Jacqueline Road, Waltham MA 02452, 21 November 2016. This letter recommends replacement of the FPE Federal Pacific Electrical panels and notes that the Northgate Garden's Board of Trustees had at that time decided to mandate that the panels be replaced.
EK to Editor, by private email 2017/03/14: All electricians who helped in this study by donating the old breakers to be mentioned and thanked. Here are more electricians to thank:
Chad Garvey, Burlington, MA. 781 983-5630, Email: Chad@bfgarveyandsons.com
David Palmieri, Randolph, MA. 781 961-7400, Palmieri Electric, Email: email@example.com
UBI (or other brand) Replacement FPE or FP Stab-Lok Circuit Breakers for Testing
Updated, 2017/04/18: The sample size of Northgate UBI circuit breakers is considered sufficient to prove the defect level.
Readers who are replacing a Federal Pioneer (FP) circuit breaker or an FP breaker sold in the U.S. by ACBC, or an FPE Stab-Lok electrical panel in which UBI (or other brand) replacement circuit breakers were installed, and who are willing to contribute their old circuit breakers for independent testing are invited to CONTACT us by email or contact Dr. Jess Aronstein directly by email to: firstname.lastname@example.org
Homeowners and renovators who encounter these panels should replace the entire panel and circuit breaker set with new equipment. Panel replacement, can involve significant expense, typically $800 to $1800 depending on service size and other factors.
FPE - UBI Replacement Circuit Breaker Discussion [with a vendor of replacement breakers]
Below is a description of the UL (and probably ETL) follow-up service for breakers listed under UL489. Note that the only testing required is at the factory, "observed" by the UL inspector.
Certification tests to the UL 489 Standard are witnessed by UL engineering
representatives. At the successful completion of the test program, UL permits
circuit breakers to bear a UL Listing mark combined with the product identity
of “CIRCUIT BREAKER” or “CIRCUIT BREAKER FRAME.”
breakers are then required to undergo subsequent follow-up testing on a
regular basis: quarterly, semiannually or biannually depending on the circuit
breaker size and quantities produced. All follow-up tests are witnessed by UL
Watch out: In our opinion there is a big hole in the electrical safety net. Nobody is sampling replacement circuit breakers from the market chain to check their quality level, and there is no test data available to the public to serve as guidance in selecting a brand of breaker.
Molded-Case Circuit Breakers, Molded-Case Switches, and Circuit-Breaker Enclosures", UL (Underwriters Laboratories), UL Headquarters
333 Pfingsten Road
Northbrook, IL 60062
Customer Service: 877.UL.HELPS (877.854.3577)
Email:CustomerExperienceCenter@ul.com, Edition 13, 10/24/2016, ANSI approved 10/24/2016, DOD approved 01/18/1985, Original source for this standard: http://ulstandards.ul.com/standard/?id=489_12
Excerpts from UL-489: 1.1 The requirements of this standard cover molded-case circuit breakers, circuit breaker and ground-fault circuit-interrupters, fused circuit breakers, high-fault protectors, and high-fault modules. These circuit breakers are specifically intended to provide service entrance, feeder, and branch circuit protection in accordance with the National Installation Codes in Annex B, Ref. No.1. ...
1.2 This standard covers molded-case switches and fused molded-case switches.
Excerpt from UL Web Page for this Standard: UL is a global independent safety science company offering expertise across three strategic businesses: Commercial & Industrial, Consumer and UL Ventures. Our breadth, established objectivity and proven history mean we are a symbol of trust, enabling us to help provide peace of mind to all.
InspectAPedia is an independent publisher of building, environmental, and forensic inspection, diagnosis, and repair information provided free to the public - we have no business nor financial connection with any manufacturer or service provider discussed at our website.
We are dedicated to making our information as accurate, complete, useful, and unbiased as possible: we very much welcome critique, questions, or content suggestions for our web articles. Working together and exchanging information makes us better informed than any individual can be working alone.
Continue reading at FPE REPLACEMENT BREAKERS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about the purchase of replacement FPE Stab Lok circuit breakers: where they are obtained, where they are made, are they tested, how they may be expected to perform, whether or not you should use them.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Note: as we didn't add this reviewers list until 2007, this list of technical reviewers is incomplete; we have received comments and suggestions regarding this topic, edits and remarks included, from engineers and management from the US CPSC, electricians (many listed at our page on field reports of FPE failures), home inspectors, licensed electricians, and electrical engineers, and even a few attorneys and real estate agents, since 1986. Technical review, critique, content suggestions, questions, or clarifications are invited and where a contributor wishes, credit and links will be provided to that source. Contact us to provide feedback.
Dr. Jess Aronstein, electrical engineer, Poughkeepsie, NY, forensic engineering services, independent laboratory testing for various agencies email@example.com (independent electrical panel testing, including FPE Stab-Lok® panels, to April 2010)
David Carrier, electrical engineer, 53 Henmond Blvd., Poughkeepsie, NY 12603 845-430-7527 firstname.lastname@example.org (independent electrical panel testing, including FPE Stab-Lok® panels, beginning 2010)
Alan Carson, Carson Dunlop, Associates, Toronto, Ontario. Mr. Carson is a home inspection professional, educator, researcher, writer, and a principal of Carson Dunlop Associates, a Toronto home inspection and education firm. Mr. Carson is a past president of ASHI, the American Society of Home Inspectors
Carl Grasso, Esq., Herzfeld & Rubin, New York, NY. Mr. Grasso is an attorney who managed a plaintiff's class action litigation against Federal Pacific Electric in New Jersey.
Licensed Electricians: FPE FAILURE FIRE PHOTOS includes electricians who have provided cases and photographs of field failures of FPE equipment at this website.
Private opinion: from an electrical engineer involved in government testing of FPE Stab-Lok® equipment, speaking anonymously because he was not authorized to speak for the agency with whom he was employed.
Homeowners, Home Inspectors, Electricians: FPE FAILURE FIELD REPORTS includes anecdotal field reports provided by a range of contributors including electricians (and some home owners or home inspectors) who have provided cases and photographs of field failures of FPE equipment at this website
William King, US CPSC Director of Electrical Engineering (Ret).
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Aluminum Wiring Information WebsiteAluminum Electrical Wiring Hazards and Repairs: in-depth authoritative info, photos, documents including selection of proper vs. ineffective repair methods. E.g.: Ideal 65 "Twister" purple connector fails in field and lab testing with aluminum wire.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones