Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
EXTERIORS of BUILDINGS
ADHESIVES, EXTERIOR CONSTRUCTION
AGE of a BUILDING - how to determine
ALGAE, FUNGUS, LICHENS, MOSS
ANIMAL ENTRY POINTS in BUILDINGS
ARCHITECTURE & BUILDING COMPONENT ID
BASEMENT WALKOUTS & COVERS
BRICK VENEER WALL Loose, Bulged
BRICK WALL DRAINAGE WEEP HOLES
BOOKSTORE - EXTERIORS
CAULKS & SEALANTS, EXTERIOR
CHIMNEY INSPECTION DIAGNOSIS REPAIR
DECK & PORCH CONSTRUCTION
DECK FINISHES COATINGS PRESERVATIVES
DRYWELLS, FRENCH DRAINS for FLAT SITES
EIFS & STUCCO EXTERIORS
EXTERIOR WALL SIDING TRIM & FINISHES
EXTRACTIVE BLEEDING STAINS
FLASHING on BUILDINGS
GALVANIC SCALE & METAL CORROSION
GLUES ADHESIVES, EXTERIOR CONSTRUCTION
GRADING, DRAINAGE & SITE WORK
GUTTERS & DOWNSPOUTS
HOUSE PARTS, DEFINITIONS
HOUSEWRAP / SHEATHING WRAP
ROOF ICE DAM LEAKS
INSECT INFESTATION / DAMAGE
LEAD POISONING HAZARDS GUIDE
LOG HOME GUIDE
PAINT & STAIN GUIDE, EXTERIOR
PAINT FALURE, DIAGNOSIS, CURE, PREVENTION
PORCHES & Sunrooms
PORCH CONSTRUCTION & SCREENING
RAILINGS, DECK & PORCH
RETAINING WALL DESIGNS, TYPES, DAMAGE
ROOF CLEANING RECOMMENDATIONS
ROT RESISTANT LUMBER
SHEATHING, GYPSUM BOARD
FIBERBOARD SHEATHING, Celotex Homasote & Other
SHEATHING, FOIL FACED - VENTS
SIDING TYPES, INSTALLATION, DEFECTS
SINKHOLES, WARNING SIGNS
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIRS, RAILINGS, LANDINGS, RAMPS
STONE SURFACE CLEANING METHODS
STONE VENEER WALLS
STUCCO WALL METHODS & INSTALLATION
SURFACE GRADING, SITE DRAINAGE
THERMAL EXPANSION CRACKS in BRICK
TREES & SHRUBS, TRIM OFF BUILDING
TRIM, EXTERIOR CHOICES, INSTALLATION
VINYL SIDING or WINDOW PLASTIC ODORS
WATER BARRIERS, EXTERIOR BUILDING
WATER ENTRY in BUILDINGS
WINDOWS & DOORS
Fiber cement siding removal procedures to minimize dust & to permit possible salvage & re-use of the material.
This article describes why owners decided to remove fiber cement siding from their home and to replace it with James Hardie's HardiePlank fiber cement product.
The article details just how the old fiber cement siding was removed with minimum damage.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Why remove building fiber cement siding?
But if building siding is extensively damaged, or so badly installed that building wall leaks are widespread and damaging the building, one might consider removing and replacing all or more limited sections of the wall siding on the building.
At SIDING, FIBER CEMENT GAPS
When owners asked for advice from several building inspectors, industry consultants, and siding contractors, they learned that the product they thought they were buying, HardiePlank fiber cement siding, was not what their original contractor installed.
Watch out: this article describes the removal of fiber cement lap siding - horizontal "boards" such as shown in our photos. These procedures are not suitable for the removal of fiber cement shingles nor asbestos cement shingles. If you are working with those siding shingle materials and need to remove shingles for repair,
Why remove limited sections of fiber cement siding
But even if there is no sound reason for removal of all fiber cement siding from a building, it may be necessary to remove sections of damaged FC siding such as the impact-damaged siding shown in our photograph at left.
Note that that damaged FC siding was at a different property from the "counterfeit" bad siding job installation discussed here and illustrated just above.
The siding damage you see in this photo was caused by a vehicle or by an impact.
Mechanical damage to fiber cement siding is described in more detail at SIDING, FIBER CEMENT DEFECTS.
Visible & Hidden Trouble Points in & Behind the Original FC Siding Installation
Further close-up inspection by the repair contractor, Galow Homes, as well as by the author (DJF) found numerous other siding installation SNAFUS including:
And more FC siding installation snafus were discovered as we began pulling the old material off of the building, including
Photos of these SNAFUs are at SIDING, FIBER CEMENT DEFECTS.
It seemed likely that had the home been more than just ten years old, more extensive rot, insect damage, wall cavity mold contamination, and lost insulation values would all have accured.
The owners ultimately decided to remove the siding, thinking that either the material would be salvaged and re-installed correctly, or the "counterfeit" fiber cement siding woudl be replaced entirely with new product.
The contractor at the job we investigated considered the remove and salvage approach, though there would be some lost material due to damage during removal.
A second consideration during fiber cement siding material removal was the wish to avoid exposure to high levels of silica dust. Note the silica dust warning in the HardiePlank® product label shown at left.
Modern fiber cement products do not contain asbestos but silica dust from these products may be a hazard itself. Asbestos from older asbestos cement shingle siding and roofing products is a widely recognized hazards. For information about that different hazard, see ASBESTOS ROOFING / SIDING DUST.
How to Remove Fiber Cement Siding with Minimum Damage & Dust
Since the old counterfeit fiber cement siding was going to be removed anyway, the contractor chose to remove it with care, minimizing the damage, to give the owner the option of re-installing the orignial siding without gaps. (The owner later elected to toss the old siding and purchase new Hardieplank fiber cement siding - a step that was not without its own difficulties -
Removing and reinstalling building siding, especially over a cosmetic issue, is a very costly approach but makes sense in some installations such as the fiasco of a fiber-cement siding installation job shown at SIDING, FIBER CEMENT GAPS.
At above right you can see the material lost on the back-side of the fiber cement siding boards when nails are punched through.
Watch out: when carrying any long fibre cement lap siding board, be sure to keep the board in the vertical or "as it would be on the wall" position. If you carry the board on the flat and it's got any length to it you're inviting breakage.
After "punching" to set the siding nails in through the fiber cement lap siding board, for boards more than about 6 feet in length, two workers should cooperate to carefully lift the board off of the building surface and carry it or hand it down for flat stacking under cover for protection from the weather.
Storing Re-Claimed Fiber Cement Lap Siding
The contractor stored the reclaimed lap siding indoors in the client's garage, stacked flat, and placed on a tarp to avoid picking up moisture from the floor.
Any loose debris was swept or HEPA vacuumed to avoid a possible silica dust hazard indoors, and the stack was also covered.
If the siding were to be re-used the contractor would have a bit of clean-up to do as well, to remove any caulk left adhered to the siding faces or ends. (Photo below).
The contractor would probably not bother to try chipping away at caulk bonded to the siding board ends; rather when the boards are being cut to size for re-use the messy ends will simply be chopped off before the board is cut to the new required length.
Continue reading at SIDING, FIBER CEMENT REPAIRS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References