Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ACCURACY vs PRECISION of MEASUREMENTS
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM SECs & WIRING
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS & VOLTS DETERMINATION
AMPACITY - the LIMITING FACTOR
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
BUILDING SAFETY HAZARDS GUIDE
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CORROSION & MOISTURE SOURCES in PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FEDERAL PACIFIC FPE HAZARDS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
This page collects and reports on CPSC Notices Regarding two circuit breaker products: Recalled Square-D Circuit GFCI Breakers and Counterfeit Square-D Breakers. The counterfeit Square-D circuit breakers, shown at left and below, were made in China, and were sold through Scott Electric Co. The recall notice issued by Scott was reported by the US CPSC in November 2006. Scott offers a free replacement or refund where the counterfeit breakers are found to have been installed.
In a separate notice involving Square-D products, a Square D GFCI breaker recalled by the Square D company was recalled in June 2006. Square-D offers free replacements for that GFI circuit breaker product. The recalled equipment is in both cases a Fire and Electrical Shock Hazard.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
This Square-D circuit breaker, sold through Scott Electric, has been recalled by that company according to the US CPSC announcement below. The circuit breaker is "counterfeit" and is a fire hazard.
[Click to enlarge any image]
You may need assistance from a professional home inspector or better, a qualified, licensed electrician, to identify this product in your home but the letter below offers visual clues that a homeowner can see by examining the circuit breaker in the electric panel by simply opening the hinged electric panel door provided for homeowner use.
Since there are serious hazards of electrical shock, homeowners should not attempt to disassemble their electrical panel such as by removing the cover from the panel or trying to replace the circuit breaker themselves. Use a licensed electrician for that work.
This website includes photographs of these products, identification information, some basic safety advice, and the original US CPSC announcements. The CPSC announcements and photographs are public domain. I provide links to the original announcements herein.
NEWS from CPSC
Scott Electric Co. Inc. Recalls Counterfeit Circuit Breakers Due To Fire Hazard
WASHINGTON, D.C. - The U.S. Consumer Product Safety Commission, in cooperation with the firm named below, today announced a voluntary recall of the following consumer product. Consumers should stop using recalled products immediately unless otherwise instructed.
Name of Product: Counterfeit "Square D" Circuit Breakers
Units: About 30,000
Hazard: The recalled circuit breakers labeled "Square D" are counterfeit and might not trip when they are overloaded, posing a fire hazard to consumers.
Incidents/Injuries: Scott Electric Co. is not aware of any incidents or injuries associated with these counterfeit circuit breakers.
Description: The counterfeit circuit breakers include Square D QO-series models 115, 120, 130, 160, 215, 230, 260, 1515, and 1520. Actual Square D circuit breakers have
Counterfied Square-D Circuit Breakers Were Sold through: Scott Electric Co. distributor locations throughout Pennsylvania and Texas from May 2005 through May 2006 for between $4 and $25.
Consumers should contact Scott Electric Co. to arrange for a free inspection and if necessary, replacement or refund.
To arrange for a free inspection or for additional information, contact Scott Electric toll-free at (877) 222-0473 between 8 a.m. and 5 p.m. ET Monday through Friday or log on to www.scottelectricusa.com - consumers and contractors can also obtain additional information by e-mailing Scott Electric at firstname.lastname@example.org
Original CPSC Announcement Regarding the Counterfeit Square D Circuit Breaker
Original CPSC Announcement of Scott's Counterfeit Square D Breaker
NEWS from CPSC
WASHINGTON, DC -- In cooperation with the U.S. Consumer Product Safety Commission, Square D Company of Palatine, Illinois is voluntarily offering free replacement of its 15 through 30 ampere size Series 1 two-pole ground fault interrupting (GFCI) circuit breakers.
Ground fault circuit breakers are safety devices which provide protection against electrocution in addition to the normal circuit breaker overload protection function. Two-pole GFCI circuit breakers are often used on 240 volt circuits serving hot tubs/spas, swimming pool equipment, pumps and fountain equipment, and other applications where electrical failure of the protected equipment could pose a risk of electrocution.
Square D Company is taking this action because it has discovered that early failure of an electronic component may disable the electric shock protection provided by this product.
The involved Square D GFCI circuit breakers have a yellow "Push-To-Test" button and are two-pole units which are physically twice the size of most branch circuit breakers. Persons who believe they may have such a unit or who have questions should telephone Square D Company at (877) 202-9046 between 7:30 a.m. and 5 p.m. ET Monday through Friday for information concerning Square D's free replacement program.
Square D GFCI circuit breakers which display the Square D trademark near the circuit breaker handle are not subject to this problem. Also, circuit breakers without the yellow "Push-To-Test" button are not GFCI devices and are not subject to this problem.
Approximately 80,000 of the involved units have been sold and installed nationwide since 1982. Square D Company is not aware of any injuries resulting from the problem with its product. The normal circuit breaker function is not affected by this problem.
The Consumer Product Safety Commission believes GFCI's provide a significant level of electrical safety. The Commission recommends that all GFCI's, both circuit-breaker type and outlet type, be tested frequently, at least monthly, using the test button on each unit.
NOTE: Minor corrections to misspelling in the first sentence were made by DJF 11/06
Send the link for this page -http://InspectAPedia.com/electric/SquareDRecalls.htm to a friend! The U.S. Consumer Product Safety Commission is charged with protecting the public from unreasonable risks of serious injury or death from more than 15,000 types of consumer products under the agency's jurisdiction. Deaths, injuries and property damage from consumer product incidents cost the nation more than $700 billion annually.
The CPSC is committed to protecting consumers and families from products that pose a fire, electrical, chemical, or mechanical hazard or can injure children. The CPSC's work to ensure the safety of consumer products - such as toys, cribs, power tools, cigarette lighters, and household chemicals - contributed significantly to the 30 percent decline in the rate of deaths and injuries associated with consumer products over the past 30 years.
Dangerous Product Reports to the US CPSC: To report a dangerous product or a product-related injury, call CPSC's hotline at (800) 638-2772 or CPSC's teletypewriter at (800) 638-8270, or visit CPSC's web site at SaferProducts.gov.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about Square-D Circuit Breaker Recalls
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References