Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ACCURACY vs PRECISION of MEASUREMENTS
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM SECs & WIRING
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS & VOLTS DETERMINATION
AMPACITY - the LIMITING FACTOR
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
BUILDING SAFETY HAZARDS GUIDE
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CORROSION & MOISTURE SOURCES in PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FEDERAL PACIFIC FPE HAZARDS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
How to install, diagnose, and repair of low voltage wiring controlling home lighting and fixtures: low voltage electrical wiring repair, parts substitution, parts replacement, and repair warnings. We describe the properties of low-voltage-controlled switches that operate 120V lights and receptacles in homes dating from the 1960's to the present. We compare that low-voltage-switching electrical system and its wiring and fusing requirements to contemporary low-voltage circuits used in buildings to power low-voltage devices such as downlights. The wiring sizes, lengths, and fusing requirements differ among these. We include a table of low voltage circuit wire sizes for different run lengths and circuit amperage load.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
A Homeowner's Guide to Inspection, Repair, and Replacement of Low-Voltage GE, Remcon, or Other Low-Voltage Building Electrical Wiring & Switches
Readers should see LOW VOLTAGE BUILDING WIRING our main article on low voltage home wiring inspection, diagnosis, repair parts, repair options.
Low voltage electrical wiring was installed in some homes beginning in about 1946's. This system was popular and was installed in many homes between 1960 a nd 1985, and it continues in use today, often in the form of 12-V low-voltage lighting and downlight fixtures. For an example of currently popular low-voltage wiring used in contemporary construction and retrofit installations, see LIGHTING, EXTERIOR GUIDE.
The low-voltage wiring system uses small-gauge copper wires connected to low-voltage switches to switch on and off relays which in turn control the operation of lights and where desired, electrical receptacles, and other 120-Volt equipment in homes.
A power supply or transformer, often called a "transverter" is fed 120V and outputs 28V to the switching system. Pressing the low-voltage switch operates a relay which in turn switches on or off a 120V light or other device in the home.
The low-voltage electrical wiring system popularized in the United States by GE® and Remcon permits the use of less-costly and easier-to-install wiring between the relays and the switches in the home. The switching relay, or a group of them, is often located in an electrical box in the building's attic, garage, or basement.
At least one supplier continues to design, sell, and service low-voltage home wiring systems: Touch-Plate Lighting Controls, in Fort Wayne IN. Some of the suggestions and opinions in this article are quoted from or paraphrase advice offered by that company. We provide contact information for Touch-Plate® Lighting Controls below.
Many original GE® or Remcon® low voltage lighting systems are still in use today. But owners of buildings with the original systems installed may find themselves faced with low-voltage switches, relays, or transformers that no longer operate.
Owners of such buildings should be careful to perform any repairs or replacements of components in low-voltage
electrical systems using only the proper devices. Installing a conventional 120-V switch or an arbitrary
push switch, or a conventional transformer/voltage converter may not work, and worse, it could be unsafe,
causing a risk of fire or shock.
This component feeds electrical power to operate the low voltage switches and relays in the system. The transverter is step-down transformer which is itself powered by a 120V circuit in the building converts its incoming 120-volt alternating current (120 VAC) to a 28-volt direct current (28 VDC). This is the operating voltage and current type used to power the switches and the relays that they turn on and off.
See LOW VOLTAGE TRANSFORMER TEST for details.
The switching relays in a low-voltage electrical system
are turned on or off by low voltage wires coming from the switch.
Low-voltage electrical switches, mounted at the normal height and location in rooms in the building are used
Normal Voltage (120V) wiring: "normal" building electrical wires, typically #14 gauge (for 15-Amp circuits), is used to carry electrical power into and then out of the low-voltage relay and on to the light, electrical receptacle, or other device that the switch and relay are intended to control.
Don't confuse the wiring requirements for low-voltage-operated switches that operate 120V devices (lights, receptacles etc) with the electrical wiring that powers low-voltage (12-V) devices (such as low-voltage downlights described at LIGHTING, EXTERIOR GUIDE.
For controlling the low-voltage-operated switching relays that in turn operate 120V devices in buildings (lights, receptacles), very thin copper wires, typically #22 gauge, is used to connect the low-voltage switches to the relays that each switch controls.
In contrast, Lucifer Lighting and others point out that when selecting an electrical wire (conductor) size for the low-voltage devices such as downlights used indoors or outside, the wire needs to be chosen based also on the distance between the light fixture and the low voltage transformer. Lucifer's installation instructions for downlights provides this helpful table of wire lengths and size requirements for low voltage wiring based on distance between the fixture and the transformer:
Comparison of Requirements for 120V Device Wiring Fusing, Low-Voltage Device/Wiring Fusing & Low Voltage Switching-Relay Fusing
Don't confuse these three types of devices, their wiring, and their fusing requirements:
Lights, receptacles, other: these are the same conventional electrical lights or electrical receptacles
found in buildings.
Diagnosing & Repairing Low Voltage Switch Problems
Low-voltage electrical system switches originally made by GE® or Remcon can be replaced with newer ones from Touch Plate but with some provisos which we explain below.
Low-voltage system relays originally made by GE® or Remcon cannot be replaced individually with newer ones from Touch Plate - there are electrical design differences that mean the products are not interchangeable.
A home or an entire circuit can, however, be converted over to the new Touch-Plate® product line. This offers the advantage of permitting the building to continue to use the existing low-voltage wiring that is already in place between the transformers and switches.
This approach should be substantially less costly and troublesome than attempting to convert all of the switches in the home to 120V design - that would require re-wiring those areas in the home with new 120V wires.
An old GE® or Remcon® system will work with the Touch-Plate® replacement switches. The GE® and Remcon® systems operate on a three-wire system. One wire is common, one wire is for turning the relay on, and the last wire is for turning the relay off.
Touch-Plate® switches only have two wires. One being the common wire and the other being the switch wire, and because of our single coil relay, the same button is used to turn the relay on and off.
You can use Touch-Plate® switches in place of three-wire switches, but you will need two Touch-Plate® buttons for every one three-wire switch. See Three-wire to Touch-Plate® Wiring Diagram.
Other Low Voltage Switching Notes
Multi-way switching is supported since multiple switches can all connect to a single relay that controls a single 120V device.
Touch-Plate® says that 3-Way, 4-Way and even 5-Way switching is a standard feature of low voltage control systems and almost all old Touch-Plate® installations have multiple switches that control the same relay.
Watch out: Do NOT ever attempt to replace a momentary action, low voltage Touch-Plate® switch with an off-the-shelf high voltage toggle switch (maintain / latching style). This will definitely cause an immediate failure of the system.
Painted switch plate covers, cracked covers, and wall-papered covers all are likely sources of producing a stuck switch.
Guide to Diagnosing & Repairing Low Voltage Wiring Relays
Switching Relays that work intermittently?
If sometimes when you operate the switch to control a light or receptacle or other device it works just fine, but at other times it fails to operate, giving difficulty in turning the light or receptacle "on" or "off" we could have a problem with the switch itself, or the problem may be with the relay that the switch controls.
Check the building first for for sticking low-voltage switches. If all of the switches appear to be working normally, then find the switching relays that are misbehaving, and check for temperature exposure problems. Switching relays that are too hot or too cold may not work properly. Low voltage relays may not operate reliably if exposed to below freezing temperatures, or to temperatures above 120 degrees. Depending on where the building is located, these conditions can certainly be encountered in an attic, and cold conditions may be encountered in a garage or crawl space.
Touch-Plate offers a trivial fix for the cold temperature problem: place a light bulb close to the relay panel. Turning the light bulb on during the cold period will usually produce sufficient warmth to keep the switching relays working. Touch-Plate® also advises "The best solution is to contact the factory for assistance in upgrading the whole system to current technology and relocating the panels to a garage, a basement, a mechanical room, or closet that will avoid this altogether."
Low Voltage Electrical Wiring Switching Relay Burn-up?
This can happen with age and use. But if the relays are burning up after replacement or other repairs to the system, check the low voltage transformer.
The voltage transformer must be one designed for this application. Some generic voltage transformers do not sense that a switch is stuck (or being held depressed for some reason) and lack a limiting function to protect the relay from burn-up.
Replacement relays for existing Touch-Plate® installations can be installed
without this worry. But this is not the case if your relays are the older GE® or Remcon® brand. First, for Touch-Plate® installations,
If the relay you are replacing has two wires coming out of the cylinder the relay is a 1550 series and it can be replaced by the Touch-Plate® 2500-B.
But what about homes using older GE® or Remcon® relays? Touch-Plate® relays cannot be used to replace individual GE® or Remcon® relays. The switching relays made by these manufacturers work differently from those designed and sold today by Touch-Plate lighting. For example, Touch-Plate informs us that he Touch-Plate® relay (2500-B) is a single coil, 28VDC latching relay, whereas the the GE® relay (RR-7) is a dual coil, 24VAC latching relay, and the Remcon® relays (depending on the style) are a single or dual coil relay with an internal power supply for each relay.
Also, two switching relays will not operate from a single button press in older systems prior to 1986, they were designed to operate one at a time.
But you can forget the details of just how your relays work if you just remember that you cannot substitute a Touch-Plate® relay for either GE® or Remcon® relays.
So what to do with a GE® or Remcon® relays that no longer work?
You can either re-wire that entire individual circuit to use Touch-Plate® components, or, as Touch-Plate Lighting recommends, replace all of the older GE® or Remcon® relays in the home with Touch-Plate® relays. This may not be as horrible as it sounds: you're not replacing wiring, just devices. themselves.
An electrical "transformer" converts voltage from one level to another, say from 120Volts down to 28Volts in order to supply the lower voltage to devices that are designed to operate at that level. A "converter" changes alternating current to direct current. Electrical power entering buildings in the U.S. and in most of the world operates at 60-cycle alternating current (or 50 cycle AC).
Alternating current: If you measured the voltage level on an AC circuit, you'd see the voltage level varying between +120V down through 0 volts and continuing down to -120V and then cycling back up again 60 times a second. That's what 60-cycle AC means.
Direct current: if you measure the voltage level on a DC circuit, you'll see the level staying roughly constant at whatever voltage level the circuit is supplying. For example, most automobiles operate most of their electrical components at 12-volts direct current or 12-V DC.
The switches and the relays they control in a building low-voltage wiring system are designed to operate at 28-volts of direct current.
So in building low-voltage wiring systems a "transverter" is used to transform 120V down to 28V and also to convert the voltage from alternating to direct current. We only need one of these transverters. Old low-voltage wiring electrical systems use a single transverter to accept incoming 120V AC current and change it to 28V direct current. The switching relays in older low-voltage wiring systems are operated individually, that is, one at a time.
Intermittent Failure of Lights or other Relay-controlled Devices
Intermittent operation of lights or other relay-controlled devices in a home usually is due to a failing power supply transverter. The voltage output of the Transverter should be 28 - 31 VDC. If voltage is not in that range, the transverter should be replaced.
Low Voltage Output at the Transverter
Low voltage at a transformer/transverter may mean that it needs to
be replaced, or it may simply mean that a switch in the home is stuck.
Check the Transverter voltage output.
In a normal low-voltage electrical system the output voltage at the
If the voltage is 0 VDC, or a really low 2 - 4 VDC, this is indicates of a stuck low-voltage switch. Touch-Plate Lighting informs us that the transverter drops in voltage output down to 3 volts after operating the relay coil in order to protect against burning up the coil.
If you read a voltage higher than 3 volts and lower than 26 VDC from the Transverter, then the transverter should be replaced.
If you are reading 28 - 30 VDC and still nothing is working then you have a wiring problem: something is not connected (as in a wire coming loose from under a wire nut) or something incorrectly wired (as in when changing a component in the system and not re-connecting to the proper wire).
Black wire and the Red wire are the On and Off lines between the low-voltage switch and the relay. Unlike a conventional 120-V electrical light circuit switch, the low voltage switch is talking not to the light, but to the relay. The low-voltage relay is also referred to as a "latching relay". A "latching relay" is a switch that "latches" into whatever position it is told to enter. So such a relay needs to receive a separate signal to tell to it to "Make" (turn on) or "Break" (turn off) the household current which the relay is passing on to the light or other device it controls.
If an older low voltage transverter still has the labels by the output wires, you may see labels reading "switch" and "relay". When wiring such a transverter, connect the wire from your low-voltage switch to the terminal marked "Switch". Similarly, connect the wire from the relay to the transverter terminal marked "Relay".
If the older Transverter connections are not labeled we're in more trouble but it's still simple to determine which wire to connect to which terminal.
Watch out: Before disconnecting the old transverter, follow the wires from the old Transverter to what it is connected to. Touch-Plate Lighting says the easiest way to do this is by locating the wire of the Transverter that connects to one wire of every relay inside the relay enclosure. This wire will be the "relay" wire. Therefore the other wire will be the "switch" wire.
How to Choose the Right Transformer for Home Low Voltage Wiring Systems
Touch-Plate's TPS-0120 120V Transverter power supply operates relays from every Touch-Plate®
Other power supplies are used to transform 120V to 6.3 V A. C. offering from .150A (150 milliamps) up to 4 Amps (400 mva) depending on the application such as for pilot lights (incandescent lamps explained just above), or other power supplies.
Other power supplies may be found installed for for pilot lights. These are simply little lights at switches that indicate if the device controlled by the switch has been turned "on" or "off". If you see a silver box labeled "PL-6" mounted above or below each relay this is a transformer for pilot lights. Touch-Plate Lighting says that the the pilot light transformers for the master switch stations are usually located in the master bedroom and/or some other main living area.
Touch-Plate also points out that these transformers are not necessary to operate electrical lights or receptacles in the building. If the pilot lights were to malfunction or stop working, you would lose the indicator light for the specific relay it is connected to, nothing more. That is, a PL-6 power supply has nothing to do with operating the relay itself, only the indicator light that shows if a relay (and the device it controls) is switched "on" or "off".
Upgrading an Older Low Voltage Switching System in a Home
(Naturally) Touch-Plate® recommends a complete upgrade for older homes having a GE® or Remcon® low voltage system, citing cleanup of confusing (modified over the years) wiring and malfunctioning relays or switches. Above we already pointed out that the chief reason for such an upgrade is that an owner can leave in place and continue to use the existing low voltage wiring between switches and relay stations.
Otherwise we'd have to install new, much heavier gauge #14 or #12
electrical wires to support 120V switching directly. If a home has already been wired to
have an electrical control center or many-way switching of lights or outlets (say 4 or 5 way
For help in planning an upgrade from an old system to a current system
it is necessary to make a count of all the loads controlled by Touch-Plate® relays.
It is also necessary to know how many different locations there are with relay panels.
Two Improvements May be Made when Upgrading Low Voltage Electrical Systems
Touchplate.com supplies switches, transformers, and relays
Touch-Plate® Lighting Controls
rocker switches that may fit or can be made to fit in the GE® triple-rocker-switch gangs:
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about low-voltage wiring, relays, switches, transformers, transverters & devices.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.