Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BOOKSTORE - ELECTRICAL
CADET & ENCORE HEATER RECALL
CHALLENGER ELECTRIC PANELS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
False electrical ground inspection & detection: this article answers basic questions about false grounds and their related safety concerns. Page top photo is courtesy of Jim P. Simmons - Mr. Electric.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Our photo at left shows a home wired with knob-and-tube circuitry. A knob and tube circuit does not include a grounding conductor or "ground wire" so any receptacles or other devices powered by such a circuit will normally lack the added safety of electrical grounding.
But electrical wiring errors combined with hasty inspection and testing may lead an inspector or homeowner to think that a device such as an electrical receptacle on such a circuit is "grounded" when it is not. Here we provide photos and discussion of such a case.
Older homes often have electrical receptacles and fixtures that are ungrounded, and many local codes do not require that they be rewired so they're grounded. Still, grounding is worth adding to your system because it adds protection against electrical shock. Grounding provides a third path for electricity to travel along, so if there is a leak of any sort, it will flow into the earth rather than into the body of a person who touches a defective fixture, appliance, or tool.
An electrical system is grounded with a local grounding rod driven at least 8 feet into the ground outside the house or by connecting to a cold water pipe. Each individual branch circuit must be grounded as well, either with a separate wire that leads to the neutral bar of the service panel or with metal sheathing that runs without a break from each outlet to the panel. (In theory, electrical outlets can be grounded individually, but this is impractical.)
In some older homes we find incorrectly installed "grounded" electrical outlets that have the opening for the grounded plug ground connector, but the electrical system has no ground path present. If you are replacing an electrical receptacle on an ungrounded circuit you should use two-slot non-grounded electrical receptacles.
But worse than installing a "grounded-type" electrical receptacle on an electrical circuit where no ground is present, is the dangerous step that a few amateurs take of connecting the receptacle's ground screw to the neutral or white wire in the circuit.
Jim Simmons is a professional and licensed electrician who studies electrical field failures and unsafe electrical wiring.
His photos at left and below show an improperly wired electrical circuit that provides a "false ground" by making a connection from the neutral wire to the ground screw. This connection may make it appear that the circuit is "grounded" since a test that connects the hot side of the receptacle to the ground port will show current flowing, but this is incorrect.
Not only does a "false ground" electrical receptacle lack an actual safe alternative path to earth through a separate ground path or grounding conductor, but worse, the "ground" connection, by being wired to the neutral side of the circuit, can cause dangerous electrical shock as well as damage to equipment plugged into such an electrical outlet.
A safer repair would be to install new electrical wiring that provided a ground path along with grounded electrical receptacles.
Mr. Simmons wrote "A simple $7 tester will test this outlet as OK. The Ideal tester I use clearly shows FG on the display, or False Ground. I have seen it many times over the years but this is the first time I got good pictures of it. You can see the copper jumper from the ground terminal to the neutral."
See ELECTRICAL GROUND SYSTEM INSPECTION for details about how to inspect the electrical grounding system at a building.
Ungrounded "two prong" Electrical Outlets - Two Slot Electrical Receptacles with No Ground
Our photo (left) shows a polarized electrical outlet that does not provide a ground connection for a grounded plug. You can see that the two slots are of different sizes. This is an un-grounded outlet.
If your outlets have two slots that are the same size, then they are neither polarized nor grounded. These are non-polarized or un-polarized, un-grounded electrical receptacles. You should not install grounded electrical outlets on circuits where no ground path is actually present (such as knob and tube wiring). To provide a grounded outlet where no ground is present is dangerous.
Some locations in your house- especially where the outlet and/or appliances may become wet- require ground-fault circuit-interrupter (GFCI) receptacles. Older, ungrounded circuits usually are protected by polarization, which is less effective than grounding but better than nothing. Grounded and polarized receptacles work only if they are wired correctly.
If you look closely at bottom connecting strap below the face the electrical outlet show above, just above our red (C) notice, you'll see a white-painted wire wrapped around the metal strap used to mount this connector in the electrical box.
Unlike the earlier "False Ground" case, this electrical receptacle was wired with a "false neutral" using bell wire or telephone wire.
The receptacle was mounted in a metal junction box and wired with two-wire armored cable (BX) that contained a hot and neutral wire. But a fault in the neutral wiring in this building caused the receptacle to stop working.
A previous owner or handyman "fixed" this problem by making a flimsy connection between the neutral screw on the receptacle and the receptacle's mounting ("ground") strap.
Since the circuit wire was armored cable, a path to ground was provided by the metal jacket of the wire itself. But when the amateur electrician wired the receptacle as we found it, plugging anything into the receptacle completes a circuit from the hot side of the receptacle through the powered device (say a vacuum cleaner), back to the neutral side of the receptacle, and through that telephone wire off to the mounting strap which connects to the metal junction box and the BX metal jacket that completes a circuit to earth, rather than through the proper neutral wire.
What happens when you use this unsafe electrical receptacle? Well when that vacuum cleaner is running the return current is traveling on the armored cable jacket - the metal "BX" exterior as well as other components in the electrical system become live. Just touching the "BX" wire jacket and grounding yourself, say to a radiator, can give a nasty shock - which is how the author discovered this erroneously wired device.
Readers of this article should also be sure to see ELECTRICAL GROUND SYSTEM INSPECTION where we describe the more broad topic of electrical grounding.
Aso review SAFETY HAZARDS & SAFE ELECTRICAL INSPECTION PROCEDURES for Inspectors examining Residential Electrical Systems.
See Local Electrical Grounding for safety procedures during inspection of the grounding system.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about false electrical grounds in buildings: detection, hazards, repair procedures
Questions & answers or comments about false electrical grounds: definition, detection, hazards, repair methods
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References