Routing, Securing & Protecting Electrical Wires for a New Receptacle
[Click to enlarge any image]
The electrical circuit wire must be properly routed and secured between the electrical panel and the receptacle location, and must be properly secured at the junction box that is to hold the electrical receptacle.
We secure wires at intervals specified by the electrical code so that it doesn't sag, hang, pull on itself, and become damaged or unsafe. The two sketches below, courtesy of Carson Dunlop, show examples of routing electrical circuit wires through a wood stud wall and through a wall supported by metal studs.
The electrical circuit wire must be protected from damage. We don't route electrical wires where they can be punctured by someone driving a nail into a wall to hang a picture.
Using Nail Stops to Protect Wiring & Pipes in Walls
Wires running in walls anywhere from floor level to seven feet above the floor (U.S.) or five feet above the floor (Canada) must be protected from nails driven through walls. Our photo (left) illustrates a 6-inch NS-2 Nail Stop produced by Simpson Strong-Tie. Simpson Strong-Tie describes these as Protecting Shield Plate Nail Stoppers.
We are showing the side of the nail-stop that will be in contact with the stud surface when it it tapped into place, providing 5 3/8" of 16-gauge steel that will protect electrical wiring (or plumbing pipes) from punctures by nails or screws driven into the wall when this nail stop has been placed on a wall stud over the point through which an electrical wire (or pipe - see CONDENSATE DRAINS) has been passed.
Nail stops by Simpson Strong-Tie are made of 16-gauge steel, include sharpened protrusions that allow the plate to be tapped into place on stud surfaces, and are sold in 1 1/2" or 5-inch widths and in lengths ranging from 2 1'2" to 16 5/16". The most commonly-seen nail stop we encounter is the NS1 3-inch model.
Nail stops prevent penetration of fasteners into wiring or piping.
They are 16 gauge steel to meet the protection requirements of
the code and feature a galvanized coating. Install with prongs or
8d common nails.
Simpson Strong-Tie provides a Code Compliant Repair and Protection Guide that describes the company's range of protective and reinforcing steel devices to comply with the various building code requirements to protect wiring and plumbing from nail and screw fastener damage.
Electrical Wire Clearances from Ducts & Pipes
We also don't route wires too close to places where the wires can be damaged by heat from a heating appliance or chimney, flooded, etc. as you'll see depicted in the two Carson Dunlop sketches below. Thanks to Steve for pointing out erroneous illustration link details, now fixed.
The illustration at left shows the typical wiring of an electrical outlet or "receptacle", courtesy of Carson Dunlop Associates.
Watch out: Electrical components in a building can easily cause an electrical shock, burn, or even death.
Even when a hot line switch is off, one terminal on the switch is still connected to the power source.
Before doing any work on the switch, the power source must be turned off by setting a circuit breaker to OFF or removing a fuse.
Reader Question: NMC cable pulled through metal studs without proper protection
Having a hard time with seller who framed the basement with metal studs, and pulled ROMEX through with no grommets or bushings. Tried to explain that that Metal studs are SHARP and will eventually cut through the romex and short it (POW !), or make the studs live (ouch)
I will trade pictures with you if you have some that will go with these.
These photographs (below) are from the inspection. - B.S., Professional home inspector, 7/27/2014
You are correct that wiring passing through metal studs require protection against damage.
There are simple plastic snap-in wiring grommets or "bushings" that offer that protection and that would have been easy to install at the time of wiring and that can doubtless be retrofit now though if the installer has to cut the bushings to insert them around the existing wiring s/he will need to check with the acceptability of that bushing modification by callling the local electrical inspector for the jurisdiction.
The photo at left, courtesy Greenlee Corporation (www.greenlee.com) illustrates a plastic bushing PN 712A-1000 designed to protect wiring where it passes through metal studs.
Wiring through metal studs is a very common procedure as we know. In addition to using the larger holes shown in your photos, there is a punching tool (a metal stud punch) and plastic grommets to fit the punched holes so that wires can be run exactly where needed.
I'll post your photos along with images of the proper plastic bushings and send you the link.
U.S. Electrical Code for Wiring NMC through Metal Studs
Meanwhile, if we are reduced to having to cite code to tell some goofus what she or he ought to have known and done in the first place, see these NEC sections:
NEC 334.17 Through or Parallel to Framing Members.
Types NM, NMC, or NMS cable shall be protected in accordance with 300.4 where installed through or parallel to framing members. Grommets used as required in 300.4(B)(1) shall remain in place and be listed for the purpose of cable protection.
NEC 300.4(B) Nonmetallic-Sheathed Cables and Electrical Nonmetallic Tubing Through Metal Framing Members.
(1) Nonmetallic-Sheathed Cable. In both exposed and concealed locations where nonmetallic-sheathed cables pass through either factory- or field-punched, cut, or drilled slots or holes in metal members, the cable shall be protected by listed bushings or listed grommets covering all metal edges that are securely fastened in the opening prior to installation of the cable.
Canadian Electrical Code for Wiring NMC through Metal Studs
Canadian Inspectors needing code citations for protection of non-metallic-sheathed wiring will want to see the 12-19-11 Ontario Electrical Safety Code Bulletin
"Bulletin 12-19-11 Non-Metallic-Sheathed Cables (NMSC) wiring methods, [PDF] Rules 2-034, 2-200, 4-004, 12-500 to 12-526, 12-3012 and 12-3022(3)", May 2012, - retrieved 7/27/4, original source http://www.esasafe.com/assets/files/esasafe/pdf/Sample_Bulletins/12-19-11.pdf. It is interesting that Rule 12-520 does not permit cables to be fished where metal joists, metal top or bottom plates, or metal studs are used.
Rule 12-516(2) permits the use of non-metallic-sheathed cable with metal stud construction. Where NMSC is used in metal stud construction the following are installation requirements:
• Approved inserts (grommets) to protect the cable where it passes through the metal stud. The inserts referred to in Rule 12-516(2)(b) must be approved for the purpose and adequately secured in place.
• Round inserts are approved for a given size opening in a steel stud. If inserts are loose fitting or can be easily removed, they are not adequate for that installation and shall be replaced or installed in properly sized holes.
• The improperly installed inserts can lead to cable insulation failures. Installation of NMSC in steel stud construction will not be accepted where the standards of workmanship or the type of inserts used results in the inserts not staying in place.
• The cable must have adequate mechanical protection. Protection plates are required in all loca- tions where NMSC is within 32 mm from the edge of steel studs in accordance with Rule 12-516(1).
Thanks to Mike Holt for help with this topic.
Sources of wiring protection for metal studs
Greenlee 712A100 Bushing for Metal Stud Punch, sold in bags of 1000, shown above, Website: http://www.greenlee.com, Email: firstname.lastname@example.org
email@example.com, Tel: Canada: 800-435-0786, U.S.: 800-435-0786
example sources: http://www.electriduct.com/ or http://www.cableorganizer.com, quoting:
GREENLEE GL-712A100 Bushings for Metal Studs are constructed of PVC (Poly Vinyl Chloride) which is fire and water resistant. The PVC bushings have a smooth finish all around allowing for quick and easy installation of all your cables without inflicting any damage.
Not only does the triple lock mechanism keep these bushings locked to 12 or 24 gauge metal studs but also prevents damage or abrasion from happening when bundling up to 10 electrical cables at once. These insulation rings are UL listed, CSA Certified and come with a 1 year warranty.
Tyco Electronics Corporation, TE Connectivity, Metal Stud Bushings Part # CPGI-ETD-RSS-BG-25 (bag of25 stud bushings) shown at left, also sold in other quantities and packaging.
Metal Stud Bushings fit existing round or square shaped holes in metal studs. Website: http://www.te.com, Tyco Quoting:
Can be used with any type of wire. Use these bushings to comply with paragraph 300-4b(1) of the 2005 NEC code.
Unsafe & Improper Electrical Wire Material & Routing - Zip Cord or Extension Cord
Here is an example of improper and unsafe electrical wiring: lamp cord or "zip cord" has been routed through the building wall.
Our photo (left) shows an electrical receptacle mounted just about 2" above the finished floor - which is ok except for the ADA requirements, but that zip cord wiring that is run into the wall is improper, unsafe, and a fire hazard.
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Timothy Hemm has provided photographs of various electrical defects used at the InspectAPedia TM Website. Mr. Hemm is a professional electrical inspector in Yucala, CA.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: firstname.lastname@example.org
Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program. Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference Book, a reference & inspection report product for building owners & inspectors. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones.
 The 2008 NEC National Electrical Code (ISBN 978-0877657903) Online Access LINK (you'll need to sign in as a professional or as a visitor)
 Special thanks to our reader Steve who pointed out prior errors in our illustrations.
 Simpson Strong-Tie, "Code Compliant Repair and Protection Guide for the Installation of Utilities in Wood Frame Construction", web search 5/21/12, original source strongtie.com/ftp/fliers/F-REPRPROTECT09.pdf, [copy on file as /Structures/Framing/Simpson_Framing_Protectors.pdf ]. "The information in this guide is a summary of requirements
from the 2003, 2006 and 2009 International Residential Code
(IRC), International Building Code (IBC), International Plumbing
Code (IPC), International Mechanical Code (IMC), 2006 Uniform
Plumbing Code (UPC) and the 2005 National Electrical Code."
"Electrical System Inspection Basics," Richard C. Wolcott, ASHI 8th Annual Education Conference, Boston 1985.
"Simplified Electrical Wiring," Sears, Roebuck and Co., 15705 (F5428) Rev. 4-77 1977 [Lots of sketches of older-type service panels.]
"How to plan and install electric wiring for homes, farms, garages, shops," Montgomery Ward Co., 83-850.
"Simplified Electrical Wiring," Sears, Roebuck and Co., 15705 (F5428) Rev. 4-77 1977 [Lots of sketches of older-type service panels.]
"Home Wiring Inspection," Roswell W. Ard, Rodale's New Shelter, July/August, 1985 p. 35-40.
"Evaluating Wiring in Older Minnesota Homes," Agricultural Extension Service, University of Minnesota, St. Paul, Minnesota 55108.
"Electrical Systems," A Training Manual for Home Inspectors, Alfred L. Alk, American Society of Home Inspectors (ASHI), 1987, available from ASHI. [DF NOTE: I do NOT recommend this obsolete publication, though it was cited in the original Journal article as it contains unsafe inaccuracies]
"Basic Housing Inspection," US DHEW, S352.75 U48, p.144, out of print, but is available in most state libraries.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.
Recommended books on electrical inspection, electrical wiring, electrical problem diagnosis, and electrical repair can be found in the Electrical Books section of the InspectAPedia Bookstore. (courtesy of Amazon.com)