Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
ANALOG VOMs & MULTIMETERS
APPLIANCE EFFICIENCY RATINGS
BOOKSTORE - ELECTRICAL
CADET & ENCORE HEATER RECALL
CHALLENGER ELECTRIC PANELS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
ELECTRICAL SPLICES, HOW TO MAKE
ELECTRICAL WIRING COLOR CODES
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Need & requirements for electrical grounding systems: this document discusses the details of why we need grounding, and definitions of electrical grounding and electrical bonding (what's the difference between these two terms.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
“Grounding”, article 250 in the NEC, is probably one of the most difficult of the often used articles. In 2005 article 250 became “Grounding and bonding”.
In the 2008 NEC there has been a major revision in language, and phrases like “shall be grounded” have changed to “shall be connected to an equipment grounding conductor.” - Sketch courtesy of Carson Dunlop Associates.
Here we define electrical ground, grounding, bonding, and earthing terms and explain why there are important differences among these words.
. Sketch courtesy of Carson Dunlop Associates.
See Definitions of Electrical Ground, Grounding Electrode, Grounding Conductor, Grounded Conductor, Ground Wire, Neutral Wire, Ground Rod, for definitions of these confusing electrical terms.
Why we need electrical grounding
Speaking first a bit loosely (we'll get careful and detailed in a minute) the grounding system at a building provides an easy path for electricity to flow to earth should certain problems occur (a power surge, lightning strike).
Bonding or connection in the electrical panel between the neutral wires, ground wires, and the utility company's incoming neutral wire allowing current to flow to the utility company's wiring, assuring that a circuit breaker will trip or fuse will blow should a problem occur such as a short circuit or overloaded circuit.
Properly operating these overcurrent devices help prevent fire and shock.
Should an electrical fault occur where no neutral connection to the utility company or no local ground path is present, the electrical potential is just sitting there waiting for a person to come along, touch some component of the system, and by accidentally providing a path to earth through their body, receive a burn or potentially fatal shock.
Details of why we need grounding, and definitions of electrical grounding and electrical bonding (what's the difference between these two terms) can be read at Why Grounding is Needed.
Bud, a master electrician from Minnesota has offered these important clarifications:
Carson Dunlop's sketch shows how the electrical current in a building can find its way to earth by way of the electrical grounding system.
But as you may want to read in our case study of loss of all ground connections at a building, don't assume that the current will always find its way to earth.
Loss of electrical ground at a building is extremely dangerous and risks electrocution.
Some discussion points about electrical grounding are listed just below.
Bud - Master Electrician, State of Minnesota
Electrical “Grounding” has two jobs in a building: an “earthing” and a “bonding” function.
What is Electrical Grounding? "Earthing"
A major purpose of “grounding” is to provide a path so a “short” will trip a breaker. That requires a low resistance path back to the power source, which is the utility transformer. The path relies on a neutral-ground connection required at all [not entirely true] services.
The second "grounding" function is actually a collection of three safety functions:
The 2nd grounding function described above is accomplished by connecting the power neutral (the neutral wire entering from the utility company's service) at the service to an earthing electrode (ground rod). Provided it's a real earthing electrode not a fake one as we found in our photo (left).
The 3rd grounding function described above is accomplished by both of the above.
Practically, all three grounding functions are accomplished by a required neutral-ground connection at the power service, with the combined neutral-ground connected to an earthing electrode or electrodes. This function might best be called “earthing”.
What is Electrical Bonding? Why is it Important?
The path is from a ground conductor [which is not necessarily a wire] to the service panel, through the neutral-ground connection, and back to the transformer via the service neutral. To provide high current to trip a breaker this must be a metal path.
The earth is far too high in electrical resistance and is not allowed to be the path. In fact this function will work if the service is not connected to earth. This function might best be called “bonding”.
Connecting exposed metal together to minimize voltage between surfaces is also a “bonding” function.
There might be some virtues to showing the Neutral-to-Ground bond (called the main bonding jumper). As I wrote previously, it is barely visible in the Carson Dunlap diagram (above) with “Electrical path for ground and neutral wires”.
When a professional examines the interior of a main electrical panel, she looks to see if there has a strap for the bond between neutral and ground buses and to the grounding conductor leading to the earthing rod (ground rod). In some panels such as SquareD the bond is a screw (and very hard to identify if you don’t know what to look for - some home inspectors have trouble finding Neutral-Ground bonds.)
Reader Questions Requirement for Bonding the Electrical Ground System to the UFER or Re-Bar in a Foundation
4/26/2014 My electrician said he installed two grounding lines outside new house but inspector is making him connect 3rd rebar to basement electrical box. The problem is the rebar that was supposed to be installed with foundation wall is nowhere to be found.
Electrician says he never saw it and feels the outside is sufficient.
The [electrical] inspector assumes it was installed and must have gotten cut by framers. So he told electrician to hammer basement until he can find the rebar and connect pipe to it, then connect to electrical box. Wouldn't it be safer to drill a hole and insert new rebar rather than smash the entire basement?
Do you have any options for this disaster that is preventing passing electrical inspection that is needed ASAP. Who would be able to fix this, anyway and how? Do you know any workarounds?
Reply: approaches to finding re-bar in concrete footings or foundations
OPINION: A competent onsite inspection by an expert usually finds additional clues that would permit a more accurate, complete, and authoritative answer than we can give by email alone and such an inspection or a conversation with your electrical inspector may clarify why the demand you describe is being made - if it is being made really in the way stated. That said I offer these comments:
This sounds as if the electrcial inspector has something in mind that we may be missing. The National Electical code provides several approaches to grounding, some are alternatives.
So if you must proceed to find the re-bar, instead of tearing up all of the concrete I can think of other approaches that may be much less disruptive:
1. Look at the building plans and specifications for the re-bar placement schedule. Making a test cut, possibly even from outside at the footings or inside at the footings or edge of slab one ought not have to go more than inches, certainly less than a foot in a direction that crosses the re-bar placement to find it by cutting an opening.
The idea that you'd have to tear up the whole structure sounds both exaggerated and unnecessary. If in fact you ended up tearing up more feet of concrete than the plans would suggest necessary, you've discovered that the builder omitted the steel reinforcement called for by plans - which itself would be a significant concern.
[Some non-structural slabs use fiber reinforced concrete and not re-bar, others use wire mesh, not re-bar, but re-bar would be expected to be in footings and piers regardless]
2. Hire an expert who has or rent a metal detecting machine that an locate steel in concrete to find the re-bar location closest to the required connection.
By "Ufer" we refer to the UFER ground (concrete encased grounding electrode) cited at DEFECTS LIST - ELECTRICAL SYSTEM and explained at ELECTRICAL DEFINITIONS. "Ufer" in my book refers to underground ferrous rod. This approach to electrical grounding improves the ground connection to earth in areas where soils are so dry that otherwise grounding may be ineffective.
You didin't indicate your location, but perhaps the electrical inspector knows that in your area it may be particularly important that the UFER grounding approach is used.
While we have frequently updated and added to the material, in its original form this information was presented by Daniel Friedman - InspectAPedia.com, at the Hudson Valley chapter of the American Society of Home Inspectors - HVASHI Seminar 12 Sept 2002, Updated April 2006. Sketch at page top courtesy of Carson Dunlop Associates.
Continue reading at FALSE GROUND at RECEPTACLES or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
(Jan 28, 2013) eleCtriCian123 said:
I have one leg of my a feeder that reads 120 and the other is reading 50v....I have a grounding or a neutral issue CorreCt?
I don't assume that Ele. A bad connection, a transformer problem or other snafus could also explain your voltage reading. But I'd certainly start at the local wiring at and in the building, at the SEC and at the meter.
(Feb 15, 2013) Anonymous said:
hi have overhead supply so no ground cable assuming i can get a good earth (on bed rock )is that all i need to pull down the house earth which is at moment unconnected at fuse board and floating at live(hot) voltage but hopefully with very little current available
An overhead supply normally incldes a neutral wire that also is ultimately grounded by the electrical supplier.
I'm not sure it's correct to assume that all "bedrock" gives a good electrical ground. On the contrary it may be necessary to find enough soil at a high enough moisture level to give good electrical grounding, or it may be necessary to use multiple grounding electrodes or ground points.
We agree that leaving the home with no ground is extremely dangerous.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References