Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Need & requirements for electrical grounding systems: this document discusses the details of why we need grounding, and definitions of electrical grounding and electrical bonding (what's the difference between these two terms.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Bud - Master Electrician, State of Minnesota
Electrical “Grounding” has two jobs in a building: an “earthing” and a “bonding” function.
What is Electrical Grounding? "Earthing"
A major purpose of “grounding” is to provide a path so a “short” will trip a breaker. That requires a low resistance path back to the power source, which is the utility transformer. The path relies on a neutral-ground connection required at all [not entirely true] services.
The second "grounding" function is actually a collection of three safety functions:
The 2nd grounding function described above is accomplished by connecting the power neutral (the neutral wire entering from the utility company's service) at the service to an earthing electrode (ground rod). Provided it's a real earthing electrode not a fake one as we found in our photo (left).
The 3rd grounding function described above is accomplished by both of the above.
Practically, all three grounding functions are accomplished by a required neutral-ground connection at the power service, with the combined neutral-ground connected to an earthing electrode or electrodes. This function might best be called “earthing”.
What is Electrical Bonding?
The path is from a ground conductor [which is not necessarily a wire] to the service panel, through the neutral-ground connection, and back to the transformer via the service neutral. To provide high current to trip a breaker this must be a metal path.
The earth is far too high in electrical resistance and is not allowed to be the path. In fact this function will work if the service is not connected to earth. This function might best be called “bonding”.
Connecting exposed metal together to minimize voltage between surfaces is also a “bonding” function.
There might be some virtues to showing the Neutral-to-Ground bond (called the main bonding jumper). As I wrote previously, it is barely visible in the Carson Dunlap diagram (above) with “Electrical path for ground and neutral wires”.
When a professional examines the interior of a main electrical panel, she looks to see if there has a strap for the bond between neutral and ground buses and to the grounding conductor leading to the earthing rod (ground rod). In some panels such as SquareD the bond is a screw (and very hard to identify if you don’t know what to look for - some home inspectors have trouble finding Neutral-Ground bonds.)
See Definitions of Electrical Ground, Grounding Electrode, Grounding Conductor, Grounded Conductor, Ground Wire, Neutral Wire, Ground Rod, for definitions of these confusing electrical terms.
Frequently Asked Questions (FAQs) about the requirements for electrical grounding at buildings
Questions & answers or comments about the requirement for electrical grounding & electrical ground system definitions.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.