Electrical Code Advice for Homeowners & DIY Repairs
This website provides information about a variety of electrical hazards in buildings, with articles focused on the inspection, detection, and reporting of electrical hazards and on proper electrical repair methods for unsafe
electrical conditions. Critique and content suggestions are invited. Credit is given to content editors and contributors.
Watch out: Do not attempt to work on your electrical wiring, switches, or outlets unless you are properly trained and equipped to do so. Electrical components in a building can easily cause an electrical shock, burn, or even death.
Even when a hot line switch is off, one terminal on the switch is still connected to the power source.
Why we Must Follow the National Electrical Code When Performing Electrical Work
Building code enforcement authorities and local laws in many communities require that electrical work be performed only by a licensed electrician. In some communities local laws permit certain electrical work to be done by the homeowner without a permit and without conflict with local codes. Contact your city or village building department for a copy of local regulations.
In any case, any electrical work, new wiring, repairs, replacements of parts, must comply with the requirements of both local laws and the National Electrical Code. Since the electrical code is written by experts and since the "code" is intended to assure that electrical wiring in a building is functional, adequate, and most of all, safe, not only should electrical work comply with the code to be legal, it should comply with the code to be safe.
Electrical work by the homeowner might affect not only safety but also fire insurance coverage. If a fire loss claim results from wiring you installed, the company may classify you in a higher risk category or in some cases your insurance company may fail to honor your claim entirely.
The NEC - National Electric Code
The National Electrical Code Book provides thorough, very detailed instructions for determining the adequacy of an electrical wiring system and is written intending to guide a professional electrician (not a homeowner) in the safe repair and modification of electrical systems such as lighting, receptacles, and electrical wiring.
The chances are your house wiring was safe and adequate when your house was built. It is probable, too, that your house wiring was originally done in accordance with the National Electrical code. This code was developed by the National Fire Protection Association and is revised from time to time. The code itself has legal status only insofar as it has been adopted by cities, towns, counties, and other governmental units as part of local building ordinances. The status of the code in your locality can be determined by contacting the building inspection department of your local government.
The NEC does not give step by step instructions
The National Electrical Code does not provide step-by-step instruction. Rather, the code specifies the preferred method of performing electrical wiring tasks and the proper materials to use in various in various applications. Incidentally, the code does not limit or prohibit electrical work by a homeowner, but as we explained above, local laws may require that you hire a licensed electrician.
Beware: understanding the electrical code requires some expertise. Even licensed electricians often buy a version of the National Electric Code which includes explanations, interpretations, and sketches to help clarify the details of safe electrical wiring practices.
Most home electrical work is surprisingly easy to do; the system is logical; replacement parts are standardized so they will fit anywhere in the U.S.
Copies of the electrical code are probably also available at your local library. Copes are often on sale in electrical supply stores and in some book stores. A somewhat simplified version of the electrical code, known as the "One- and Two-Family Residential Occupancy Electrical Code," less costly than purchasing the entire NEC. The simplified edition covers the most popular and widely used wiring methods.
The Canadian Electrical Code
The Canadian Standards Association (CSA) has been publishing the Canadian Safety Standard for Electrical Installations since 1927. This document forms the basis for electrical codes adopted in the individual Canadian provinces. The U.S. and Canadian electrical codes differ in some technical details but are slowly merging.
The 2006 Canadian Electrical Code draws from the International Electrotechnical Commission (IEC) Standard 60364, the European standard for electrical wiring.
The United Kingdom Electrical Code
In the U.K., electrical wiring is specified by the UK Institution of Engineering and Technology (IET) in IEE Wiring Regulations BS 7671 which, like the CSA code, draw on IEC 60634.
In Australia and New Zealand, electrical wiring is specified by the wiring rules in AS/NZS 3000.
Examples of Electrical Code Requirements that Homeowners Should Know
How to select the proper electrical junction box
Electrical codes require that all wire connections or cable splices be inside an approved metal or plastic box. You cannot bury a box inside a wall - that is, you cannot hide or cover over a junction box with a finished surf race like drywall or paneling. The junction boxes in a home must all must be accessible. This protects your home from the danger of fire and makes it easier to inspect and upgrade your wiring in the future.
The size, shape, and type of electrical junction box you need to choose depends on what it's for. Boxes vary in size, depth, and material. The junction box you need to use to join wires together in an attic for a splice is not the same shape as a box you need to use to install a single electrical outlet. Even the choice of a single junction box to install a single electrical outlet on an existing electrical circuit will be affected by the number of electrical wires that have to enter the box (more wires need more cubic inches of space to be wired safely).
These details are spelled out in the National Electrical code as well as in subsets of the code written and amplified to guide installers of residential electrical wiring.
Adding or Wiring an Electrical Outlet
A very common homeowner task that some people tackle is replacing a worn electrical outlet, or more complicated, adding a new electrical outlet in a building. While this task is not difficult, if it is not done properly there can be a real risk of fire or shock or even a fatality.
How & Why It is Important to Assure Safe Electrical Grounding at a Property
Home inspector Arlene Puentes summarizes distinctions important in understanding the function of electrical grounding at a building:
Grounding to trip the circuit breaker or blow the fuse: Electrical grounding is necessary to protect people from electric shock by providing a good electrical path to route a faulty electrical connection (such as a short circuit) to ground (literally, to the earth) so that current will flow through and thus trip the circuit breaker or blow the fuse, safely and quickly turning off the electrical circuit. (A short circuit is one of the two ways that a fuse or circuit breaker will blow. The second is the drawing of more current (amps) than the circuit is intended to carry.)
Grounding to route stray electricity from static electricity, electrical power surges, lightning, etc. to ground. This can protect the insulation on electrical wires from damage due to high voltage. The protection against static electricity helps reduce the chances of an un-wanted spark that can cause damage to electronic components or cause an explosion of nearby combustible gases.
Grounding to provide a normal path for electricity to flow: energy flows in an building's electrical circuit from a power source (the utility pole through electrical panel, though building circuits and electrical devices connected to them) to the ground, to earth. If there is no good connection to earth, electricity does not flow, though it might if you stand on wet ground and touch a live electrical wire - an action that could be fatal. Ground and neutral are related electrical terms. Neutral is used to describe the "return path" from in an electrical circuit to the electrical panel. Inside of the main electrical panel the neutral wires are bonded to the ground wires and to a grounding conductor that connects that assembly to earth (typically through a grounding electrode or "ground rod")
See ELECTRICAL GROUND SYSTEM INSPECTION for a detailed example of the importance of proper electrical ground connections and of what can go wrong if the electrical ground wiring is faulty.
See DEFINITIONS of ELECTRICAL TERMS for more explanation of electrical potential or volts. In that section, see Definitions of Electrical Equipment Ground, Grounded Electrical Conductor, Ground, Ground Rod & Ground Bond for details.
What Authorities or Certifications Make Electrical Components Legal for Use ?
Listed Electrical Equipment: as defined in the U.S. National Electrical Code (NEC) (CSA provides similar terms) as: equipment, materials, or services included in a list published by an organization that is acceptable to the authority having jurisdiction and concerned with evaluation of products or services, that maintains periodic inspection of production or listed equipment or materials or periodic evaluation of services, and whose listing states that the equipment, material, or services either meets appropriate designated standards or has been tested and found suitable for a specific purpose.
In simpler terms this means that listed electrical equipment (circuit breakers, wires, connectors, switches, receptacles, and more) has been tested by someone whose procedures are acceptable to your state, provincial, or city or town electrical inspectors. By implication, an electrical part that has not been listed may not be approved for use in a building, and by implication, may be unsafe.
Labeled Electrical Equipment is equipment or materials to which has been attached a label, symbol, or other identifying mark of an organization that is acceptable to the authority having jurisdiction and concerned with product evaluation, that maintains periodic inspection of production of labeled equipment or materials, and by whose labeling the manufacturer indicates a compliance with appropriate standards or performance in a specified manner.
In practice we've seen a range of care in the application of standards, testing, listing, and supervision, in the listing and labeling of electrical products, extending from serious, responsible, and proper, to improper and downright dangerous over the history of electrical products. An example of improper labeling practices was documented in the history of the FPE Stab-Lok electrical panels and circuit breakers: the manufacturer lost their UL label for a time after getting caught placing labels on equipment where they did not belong. See FEDERAL PACIFIC FPE HAZARDS for details.
The UL Seal provided by Underwriters Laboratories for electrical parts
An example of a long-established listing organization for electrical products is Underwriters Laboratories, founded in 1894 by William H. Merrill, an electrical engineer who supported the development of electrical standards, testing, and protection from electrical hazards. Originating in the United States, UL has facilities in more than 100 countries.
Underwriters' Laboratories Inc. is a nonprofit organization that performs tests on electrical products. If an item meets minimum safety standards avoidance of fire and shock, it is listed with the Underwriters' Laboratories. Listed items display the UL seal on the item or on its package.
This indicates minimum compliance standards. Products having a wide variety of prices may all have the UL seal. Higher priced items will generally have additional features for convenience or longer life.
Green link shows where you are in this article series.
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: email@example.com
Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program. Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference Book, a reference & inspection report product for building owners & inspectors. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones.
Arlene Puentes, an ASHI home inspector in Kingston, NY, suggested text on the importance of safe electrical grounding. Ms. Puentes has served as Hudson Valley ASHI (American Society of Home Inspectors) chapter president, and is active in professional education in the home inspection field. She can be contacted at firstname.lastname@example.org
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.
Recommended books on electrical inspection, electrical wiring, electrical problem diagnosis, and electrical repair can be found in the Electrical Books section of the InspectAPedia Bookstore. (courtesy of Amazon.com)
"Electrical System Inspection Basics," Richard C. Wolcott, ASHI 8th Annual Education Conference, Boston 1985.
"Simplified Electrical Wiring," Sears, Roebuck and Co., 15705 (F5428) Rev. 4-77 1977 [Lots of sketches of older-type service panels.]
"How to plan and install electric wiring for homes, farms, garages, shops," Montgomery Ward Co., 83-850.
"Simplified Electrical Wiring," Sears, Roebuck and Co., 15705 (F5428) Rev. 4-77 1977 [Lots of sketches of older-type service panels.]
"Home Wiring Inspection," Roswell W. Ard, Rodale's New Shelter, July/August, 1985 p. 35-40.
"Evaluating Wiring in Older Minnesota Homes," Agricultural Extension Service, University of Minnesota, St. Paul, Minnesota 55108.
"Electrical Systems," A Training Manual for Home Inspectors, Alfred L. Alk, American Society of Home Inspectors (ASHI), 1987, available from ASHI. [DF NOTE: I do NOT recommend this obsolete publication, though it was cited in the original Journal article as it contains unsafe inaccuracies]
"Basic Housing Inspection," US DHEW, S352.75 U48, p.144, out of print, but is available in most state libraries.