Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ACCURACY vs PRECISION of MEASUREMENTS
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM SECs & WIRING
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS & VOLTS DETERMINATION
AMPACITY - the LIMITING FACTOR
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
BUILDING SAFETY HAZARDS GUIDE
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CORROSION & MOISTURE SOURCES in PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FEDERAL PACIFIC FPE HAZARDS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
This article answers basic questions about installing electrical conduit. Electrical conduit is metal or plastic rigid or flexible tubing used to route electrical wires in a building. Electrical conduit for wiring has some advantages in protecting wires and also in running multiple wires to a location.
But the proper selection of electrical conduit materials, fittings, and installation are important for safe electrical wiring. This website provides information about a variety of electrical hazards in buildings, with articles focused on the inspection, detection, and reporting of electrical hazards and on proper electrical repair methods for unsafe electrical conditions. Critique and content suggestions are invited. Page top photo courtesy of Tim Hemm.
Credit is given to content editors and contributors.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
How to Make a Map of the Electrical Circuits in a Building
Each circuit breaker or fuse on your electrical service panel in a building should be identified to show the area of the building whose circuits it protects. This can be done by putting adhesive-backed paper or plastic stickers next to each circuit breaker or fuse.
Or you can make a sketch of the panel layout with circuits identified, and attach it to or keep it near the service panel. In addition to this, however, a map of your house showing exactly which lights, outlets, appliances, etc., are on each circuit can be a great help in planning electrical work and in tracking down troubles.
If the building is a new home, the builder or electrical contractor may be able to supply you with a copy of his wiring diagram. If you cannot get a circuit map ready-made, you can make your own. The map you make will probably provide a few surprises. Circuits are often split between rooms-and outlets within a room are split between circuits-in ways you could never have guessed.
Prepare a Building Floor Plan
To start with, draw a floor plan of the building whose circuits you need to trace. Make your floor plan drawing floor-by-floor or room-by-room, whichever is more convenient, but be sure to include every area that has electric service. Include porches, garages, outbuildings, etc. Use some system of symbols to identify every fixture, wall outlet, and switch. Don't forget outside outlets, entrance lights, outdoor floodlights, etc.
Find the Main Electrical Panel and Find any Sub Panels
Electrical Emergency Response: One of the most important safety measures to take in a building is to make sure that the adult building occupants know where to shut off electrical power in an emergency. If sparks are flying from a toaster or someone is being shocked, we don't want to waste time looking for the electrical panel, nor do we want to waste time figuring out which breaker or fuse to turn off.
In an electrical emergency, go to the main electrical shutoff switch and turn it off. If touching the main switch is unsafe, for example because the floor is wet, you may use a dry non-conductive wooden handle such as a broom to push off or down the power switch.
Find and Label All Main Electrical Shutoff Switches First
But some buildings, especially older ones, may have no single main power shutoff, and may be powered by multiple electrical panels.
If the main electrical panel serving a building has more than six switches and has no main shutoff switch, we recommend that one be installed.
All main electrical switches (if more than one is present) must be labeled "MAIN" in any building.
In our photo at left the main switch is plainly visible at the top of the electrical panel; an owner has added an arrow and a sign which helped assure that asian occupants of the building would also understand how to turn off all electrical power in an emergency.
How to Find Remote Fuse or Circuit Breaker Panels in a Building
What if you don't know if there are any remote electrical panels or not in a building? Sub panels should be easily found and identified but often they're hidden away such as in this odd panel photo courtesy of Timothy Hemm.
Most simple buildings receive their electrical power through a single electric meter from which the electrical service enters a single main electrical panel.
If this is the case for your building, then if there are additional electrical sub-panels located throughout the building or in outbuildings, most likely each sub panel receives its electrical power from the main panel and there will be a switch in the main panel that controls power to the sub panel.
There are exceptions however: at some buildings electrical power may come from the electric meter into a single main building shutoff which in turn may feed a metal chase or tray to which multiple electrical panels have been connected.
Here are some tips that home inspectors use to guess that a remote electrical panel is present and then to go looking for it:
Finding Special Power Switches for Major Equipment
In many buildings, for safety as well as service convenience, certain equipment is required to have its own shutoff switch. You should find an electrical shutoff outside at the central air conditioning system compressor/condenser unit, for example, and you may find a separate electrical shutoff switch at an electric water heater.
These shutoff switches may be little electrical sub panels, but normally each of them is simply serving as a local electrical switch - that is, they should not be also powering other electrical circuits.
We don't count these switches as "sub panels" but rather as switches, and the purpose of each will be obvious since it's next to and is connected to the device it serves.
But if you see that someone has added smaller diameter wires coming out of one of these switches, say to add a local electrical outlet or lighting circuit, there's a good chance that the addition is improper and un-safe. That's because we don't want to power a 15-Amp 14-gauge wire receptacle circuit out of a fuse or circuit breaker box that permits 40 or 50 Amps of current to flow (intended for a water heater or electric range).
The result could be a fire. If you suspect that a high-amperage power switch such as we describe has been used to power other electrical circuits you should ask your electrician to check it out promptly.
List the Circuit Breakers or Fuses in Each Electrical Panel
Then number each circuit breaker or fuse on your service panel. If the electrical power in your building is distributed by more than one electrical panel or fuse box, that is, if electrical power is distributed by both a main panel and one or more sub-panels, you'll need to follow this procedure at each electrical panel.
Many homes are served by a single main electrical panel, in which case this task is simple. Find the main electrical panel, open its hinged cover, and look inside at the fuses or circuit breakers.
Most electrical panels have a number embossed on the cover plate next to each circuit breaker. Fuse panels may lack this detail. If your electrical panel face does not have a number by each breaker or fuse, or if they are hard to read, you can use a fine-tipped felt-tipped marker to simply write an identifying number neatly next to each breaker or fuse.
Turn on Lights in the Building
Next, turn on all the ceiling and wall fixtures and lamps in your house. It is not necessary to turn on major appliances at this time.
Turn Off Individual Circuit Breakers or Fuses, One at a Time to Identify Lighting Circuits
The procedure is to turn off each circuit breaker or remove each fuse individually. Then determine which lights are off. Mark the number of the circuit breaker or fuse just turned off or removed next to the fixture and switch symbol on your diagram.
How to Map Electrical Receptacle (Wall Outlet) Circuits
Next check all the wall outlets in the rooms in which lights went out. Plug a small lamp or work light in each outlet. If the lamp does not light, mark the number of the circuit breaker or fuse next to the outlet symbol on your diagram.
Repeat the procedure for each circuit breaker or fuse on your panel. When you finish, every symbol on your floor plan should have a circuit number next to it. If any symbol has been missed, recheck the area by turning on the light or plugging your work light into the outlet. Next, turn off, one at a time, each circuit that your diagram shows on nearby fixtures and outlets until you find the one that applies.
Identifying Appliance Circuits
These are circuit breakers or fuses that protect large appliance circuits (such as a refrigerator or dishwasher).
Tim Hemm's photo at left shows a poorly labeled electrical panel, and an unsafe-brand (FPE Stab-Lok) that should be replaced. But we can see that someone has thoughtfully labeled some of the circuit breakers as Oven and Addition.
The "Addition" breaker may power a sub panel. But this electrical panel should be replaced, as you can learn in our separate article about Federal Pacific Electric Stab-Lok panels.
Turn off these remaining circuit breakers or remove these fuses one at a time and check your appliances to find out which one does not work.
Remember that furnaces and air conditioners may appear to be off because of temperature-control settings.
Complete the Identifying Notes on the Circuit Map
Be sure to note on your diagram any circuit uses that are not covered by symbols and may be useful to you. For example, two circuit breakers or fuses are used in electric range circuits. Note on your diagrams which device protects the oven and which protects the surface burners. When you finish your diagram, store it near your service panel in a protective envelope.
Tip: You can save some time and frustration by using a small plug in radio instead of a work light to check the wall outlets. Plug the radio into the outlet you want to check. Tune to a strong station and turn the volume up. Back at the service panel, turn off the circuit breakers or remove fuses one by one. When the sound goes off, you have found the circuit.
Do not attempt to work on your electrical wiring, switches, or outlets unless you are properly trained and equipped to do so. Electrical components in a building can easily cause an electrical shock, burn, or even death.
Even when a hot line switch is off, one terminal on the switch is still connected to the power source. Before doing any work on the switch, the power source must be turned off by setting a circuit breaker to OFF or removing a fuse.
Also see ELECTRICAL CODE BASICS.
Green link shows where you are in this article series.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about how to identify or map individual electrical circuits in buildings
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.