Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
Fireplace safety & structural inspections - indoor procedures: this article describes Fireplace Inspections performed from indoors, listing a professional chimney sweep's fireplace and chimney hazard checklist for problems that can be found by visual inspection at the fireplace or chimney cleanout.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
In the 1980's Bill Murphy, Hudson Valley Chimney Sweeps, met with New York Metro ASHI home inspectors to list his biggest safety worries when inspecting a fireplace or fireplace chimney flue from indoors.
Here is the list of concerns Bill provided, in alphabetic order, not in order of level of risk. From a variety of fire safety inspection sources we have added a few items beyond what Murphy originally listed, and readers are welcome to us to add other inspection suggestions.
Visible fireplace chimney flue condition
At FIREPLACE INSERTS we detail the exploration of the condition of a cast-iron "fireplace" or fireplace grate that was originally intended for burning large chunks of coal, probably soft coal. This installation was found in a home built in Poughkeepsie NY ca 1900 and restored by the author.
This installation is particularly interesting. If you click to enlarge the photo you can see light colored bricks at the right of the fireplace insert: the installer appears to have bricked the original fireplace opening to better fit the new insert.
Watch out: adding a fireplace insert that moves the fire doors closer to the edge of the hearth reduces fire clearance (for heat or if the doors are open, sparks and coals) between the appliance opening and nearby combustibles or flooring.
The owners have placed a "fireproof rug" in front of this unit - that semi-circular carpet observed on the floor. Is this adequate? Be sure to consult your local fire inspector when installing or converting a fireplace or fuel burning appliance.
By "fireplace insert" we refer to a wood or coal-burning stove designed to be inserted into an existing masonry fireplace opening.
The wood-stove installed in the fireplace at left may work in such a location, but it was not designed as an "insert" - and does not fit the opening of this odd fireplace. In fact not much would fit in this angled firebox.
Placing the feet of the woodstove past the hearth and onto a rug, as well as less than 3' from combustibles, are further fire hazards - this is an unsafe installation.
Details are at FIREPLACE DAMAGE & UNSAFE HEARTHS.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.