Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
How to inspect factory-built fireplaces & fireplace inserts. This article provides a checklist useful for building or home inspectors who need to examine a factory-built fireplace and chimney. Zero-clearance fireplaces are typically steel constructed fireplaces to burn wood or perhaps other fuels such as LP or natural gas in modern homes, usually connected to a metal chimney. Our photo (left) shows a zero-clearance gas fireplace. Other zero clearance fireplaces burn wood or perhaps other fuels.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Following this example of hard-to-spot but unsafe factory-built fireplace installation fire hazards we provide a checklist for the inspection of factory-built fireplaces.
Watch out: we have found a few zero-clearance fireplaces improperly installed too close to combustibles.
[Click to enlarge any image]
The clearance to combustibles is not "zero" but one or more inches, depending on the materials, construction, and manufacturers' instructions.
The installer did not understand the purpose of steel clearance-assuring projections welded to the zero-clearance fireplace, and s/he had hammered them flat to "shoe-horn" the zero clearance fireplace into a too-small wood-framed rough opening. The result was a serious building fire hazard and a building code violation as well.
Our photo of a zero-clearance fireplace from inside the framed opening (left) shows the clearance guards intact next to our ruler. But inspection showed chimney leaks onto this unit - evidenced by the rust and white stains that can ultimately damage the flue (at upper right) and the fireplace unit, making it unsafe.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about using a checklist to inspect factor-built fireplaces
Questions & answers or comments about the installation, code compliance, safety & inspection of factory-built fireplaces, fireplace inserts, & zero-clearance fireplaces.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.