Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY FIRE ACTION / PREVENTION
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
FLAME COLOR, BLUE vs YELLOW COMBUSTION
HEATING SYSTEM INSPECTION
HOME HEATING SAFETY
ODORS & SMELLS DIAGNOSIS & CURE
SAFETY RECALLS CHIMNEYS VENTS HEATERS
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
Chimney shoulder construction, flashing, and sealing: this article defines chimney shoulders and explains the construction and sealing difficulties peculiar to this portion of masonry chimneys. We describe different masonry chimney side & shoulder treatments used on brick chimneys, how people try to seal this surface against leaks and water damage, and how the chimney shoulder may be sealed against the building side wall. We include photographs of different chimney shoulder designs and flashing or sealing details along with comments about the leak or damage risks at each approach.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Examples of Chimney Shoulder Finishes & Treatments to Avoid Leaks & Damage
Smooth-Brick Closure of Sloped Chimney Shoulders
At below left the chimney shoulder was constructed with a steep-angled shoulder of smooth brick facing. This chimney did not suffer frost damage at its shoulders nor water entry at the building wall - but wait! What about that wide flashing extending out over the chimney shoulder. That's odd isn't it? You betcha. Now notice the iron band around the base of the chimney shoulder. This chimney shoulder was not leaking, but the entire chimney had been moving away from the house at a substantial distance - a costly chimney footing problem. Inspecting at the chimney shoulder for construction type and leaks led to discovery of an important and dangerous and costly issue. Details are at Chimney Movement, Ongoing vs Static.
At above right is a second version of "smooth brick" treatment of a chimney shoulder. But this chimney shoulder is less steeply-sloped and happens to be on a shaded side of the home. The combination of lower slope on this shoulder and perhaps shade have conspired to promote moss growth in the mortar joints. Moss, in turn, holds water and moisture in the mortar joint, accelerating wear and in a freezing climate, frost damage. The use of J-channel at the wall to chimney surface joint (blue arrow) is itself not a reliable seal against water entry into the wall. Our photo is a bit askew so it's hard to say if this shoulder drains towards or away from the building wall.
Concrete or Mortar Seal at Stair-Stepped Chimney Shoulders
At below left, instead of capping the entire shoulder with concrete the mason tooled each stair-stepped chimney shoulder joint with a smaller quantity of sloped concrete. We were skeptical about the durability of this approach until we inspected this home located in Minneapolis Minnesota - an area exposed to severe winter conditions. The chimney on this older home was perfectly intact. The wall covering was stucco, however, a material difficult to seal against the chimney shoulder as our second photo (below right) illustrates. Incidentally, while the chimney shoulders were not a source of damage to the chimney at this home, the chimney had moved a bit away from the structure, a condition visible at upper sections of the chimney where the quantity of movement will generally be greater.
Caulking & Flashing Seals at Chimney Shoulders
Our chimney shoulder seal photo at below left illustrates a futile approach: sealing the chimney to the aluminum-sided building wall using caulk or other sealants. Differences in materials (brick, aluminum siding, wood framing) mean different rates of thermal expansion/contraction, and quite a bit of stress on the caulk joint, making this approach a bit unreliable. Watch out for leaks and insect damage in walls where you observe this detail. And notice that just below my pen the caulk-sealant is not really bonded to the (algae covered) brick surface. This is a leak point.
At above right a second chimney shoulder treatment method is illustrated on a New York home - the shoulder was sealed with a concrete cap and counter-flashing (but no flashing) was installed along the building wall.
Watch out: check closely for leaks into the building wall anyway - if that shoulder does not slope away from the building wall, water entry is difficult to prevent at this location.
Frequently Asked Questions (FAQs) about Chimney Shoulders
Questions & answers or comments about the construction, sealing, & inspection of chimney shoulders & sides for leaks & damage.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.