Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATOR, DAMPER, BOOSTER
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
Chimney inspection procedures for the building interior: this article describes procedures for inspecting the condition of chimneys and flues from inside of a building. We begin in the building attic (or on the building's highest floor) and continue downwards through the building with text and photographs describing chimney damage or chimney hazards for which the building owner, inspector, or service technician should be alert.
These articles on chimneys and chimney safety provide detailed suggestions describing how to perform a thorough visual inspection of chimneys for safety and other defects. Chimney inspection methods and chimney repair methods are also discussed.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Interior basement and attic inspections will reveal corrosion at the cleanout door, connector problems and flashing leaks. And close inspection of chimney surfaces or walls covering chimneys will often disclose evidence of dangerous chimney conditions such as holes, gaps, and cracks in the chimney structure.
Indoors inspect any visible areas of the exterior of the chimney while you are inside the building. Attic access to a chimney or basement access, may provide key inspection points since there the chimney is likely to be directly accessible and there may be cleanout or other access ports to check the condition of the chimney interior.
In this photo the exterior of this chimney, visible in an attic, was in very poor condition, with soft spalling bricks.
Worse, there was an immediate fire and gas hazard since there were actual openings at the base of this chimney where it passes through the attic floor framing. This is a serious fire hazard and a flue gas leak hazard. This flue is unsafe.
Inspect the entire route of the chimney through all building areas. Even if the chimney is not directly visible you may find evidence of leaks, movement, or old chimney penetrations, say for a woodstove, that may not have been safely closed.
Missing chimney bricks: this photo shows a homeowner "repair" involving putting aluminum sheet metal over a hole in their chimney to make it "safe" - removing the metal disclosed a nice hole where bricks were missing. We asked the homeowner where s/he thought those bricks had gone?
This was a very unsafe chimney. The second photo shows the chimney hole with the sheet metal removed. The bricks had fallen down and blocked this flue, creating a potentially fatal carbon monoxide (CO Gas) hazard which was first noticed by the homeowners as a basement water problem - water was condensing and running down basement walls.
Also be sure to read FLUE VENT CONNECTORS, HEATING EQUIPMENT and our Fire Clearances articles (links at the "More Reading" links at the bottom of this article ).
This article series also includes articles on CHIMNEY INSPECTION, FLUE INTERIOR and on additional hazards at chimney cleanout doors, fireplaces, and woodstoves (links at the "More Reading" links at the bottom of this article ).
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about chimney inspection procedures for indoors - key steps.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References