Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
COAL STOVE OPERATION & SAFETY
DIRECT VENTS / SIDE WALL VENTS
DRAFT HOOD, GAS HEATER
DRAFT REGULATOR, DAMPER, BOOSTER
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD-OIL COMBINATION HEATERS
This article describes fire clearances for chimney cleanout doors. We also explain some of the other hazards associated with chimney cleanout doors.
These articles on chimneys and chimney safety provide detailed suggestions describing how to perform a thorough visual inspection of chimneys for safety and other defects. Chimney inspection methods and chimney repair methods are also discussed.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
A missing chimney cleanout door or a cleanout door left open means that there is a fire safety hazard (sparks or ashes falling out onto the basement floor) and also that it is impossible to control the draft in the flue.
[Click to enlarge any image]
we have found heating boilers with draft problems and "repair attempts" like removing the boiler's barometric damper, when all the while the root problem of bad chimney draft was that the cleanout door was open or missing.
A missing chimney cleanout door is most serious because it is unsafe.
But a missing cleanout door or simply a cleanout door that is left ajar makes it very difficult for the chimney to develop adequate draft.
In turn this means that a fireplace or an oil or gas fired heating appliance may be both unsafe (carbon monoxide gas, fire hazards) and also in poor operating state.
For example on oil fired heating systems and some fireplace chimneys we've found a draft inducer installed on a chimney to cope with inadequate draft when the root problem was a basement cleanout door that had fallen off. (DRAFT INDUCER FANS)
On gas fired appliances, inadequate draft from a missing chimney door could lead to dangerous or even fatal carbon monoxide poisoning in a building. (CARBON MONOXIDE)
Continue reading at CHIMNEY CLEANING PROCEDURE or select a topic from the index of chimney articles listed above.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References