InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Low refrigerant or refrigerant undercharge effects on air conditioners & heat pumps or other HVACR equipment:
This article explains the symptoms of and problems caused by not enough refrigerant in cooling equpment.
Refrigerant charge quantity for air conditioners & heat pumps: This air conditioning repair article series discusses the the diagnosis and correction of abnormal air conditioner refrigerant line pressures as a means
for evaluating the condition of the air conditioner compressor motor, which in turn, is a step in how we evaluate
and correct lost or reduced air conditioner cooling capacity.
We explain how overcharging or undercharging of refrigerant in an air conditioner or heat pump is detected and we list the effects of overcharged or undercharged refrigerant. We also explain the various causes of liquid slugging a compressor motor.
We also provide a MASTER INDEX to this topic, or you can try the page top or bottom SEARCH BOX as a quick way to find information you need.
Effects of Undercharging the Refrigerant Level in an Air Conditioner, Heat Pump, or other refrigeration equipment
Effect of too little refrigerant in the system
When we undercharge an air conditioner, heat pump, or other refrigeration equipment
Improper operating refrigerant pressures, too low: surprisingly to the novice, too little refrigerant in the system can actually drop the temperature in the cooling coil below its normal operating range; that's why we mention at FROST BUILD-UP on AIR CONDITIONER COILS that a cause of coil frosting in the air handler might be an early sign of a refrigerant leak.
Loss of cooling capability: eventually when enough refrigerant leaks out of the system temperatures rise again because we no longer have any heat exchange between the condenser coil and the outdoor air nor between the then empty cooling coil and the indoor air.
More expensive operation: There is not enough refrigerant in the system, for example to properly fill the cooling coil - then we remove less heat (per unit of time operation of the equipment) so we are decreasing the operating efficiency of the system.
Cooling Coil Frosting: Too-low refrigerant levels in some systems also can cause frosting and freezing at the cooling coil.
Compressor motor damage: Too little refrigerant in an air conditioner, heat pump, refrigerator, or even a dehumidifier is likely to cause overheating of the compressor motor. That is because in a properly-charged refrigeration system, the refrigerant is cooling the electric motor that is sealed inside the compressor unit. An overheated A/C motor may trip a circuit breaker, may have trouble starting, and eventually will fail to run at all.
Watch out: when an air conditioner or heat pump motor "burns out" the result is a costly contamination of the entire refrigeration system as burned lubricants and even shellac or coatings on motor windings will have been circulated through the refrigerant piping system.
That's why an experienced HVAC repair person will insist on cleaing the entire system and installing one or more "burnout" refrigerant filter/driers (REFRIGERANT DRIERS & FILTERS) on the refrigerant lines when the compressor is replaced.
Bottom line about undercharging refrigerants: For residential equipment such as air conditioners, heat pumps, refrigerators, freezers, to work properly you must have exactly the correct charge in the system.
at FROST BUILD-UP on AIR CONDITIONER COILS we also explain that in a properly tuned and adjusted refrigeration system there will be liquid refrigerant found all the way to just at the end of the evaporator coil - this gives us maximum cooling efficiency of the equipment.
Effects of Overcharging the Refrigerant Level in an Air Conditioner, Heat Pump, or other refrigeration equipment
See COOLING CAPACITY, RATED of air conditioning equipment if the system seems to be working but is inadequate to cool your building. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Continue reading at TEV INSTALL & REPAIR or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"Air Conditioning & Refrigeration I & II", BOCES Education, Warren Hilliard (instructor), Poughkeepsie, New York, May - July 1982, [classroom notes from air conditioning and refrigeration maintenance and repair course attended by the website author]
Fiberglass: Indoor Air Quality Investigations: Fiberglass in Indoor Air, HVAC ducts, and Building Insulation
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones