Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
INSPECTION CHECKLIST - OUTDOOR UNIT
LOST COOLING CAPACITY
MOTOR OVERLOAD RESET SWITCH
NOISE / SOUND DIAGNOSIS & CURE
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
Air conditioner or heat pump noise diagnosis & cure: this air conditioning repair article discusses the diagnosis and repair of air conditioning compressor noises which range in importance from normal (if annoying squeaks and squeals, to rattling loose bolts and hardware, to costly compressor damage indicating air conditioning compressor or A/C compressors at or near end of their life.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Index to Text Descriptions of A/C or heat pump sounds & possible causes / cures
Index to Recordings of A/C or Heat Pump Sounds & Noises: Submit, Listen-to, or Comment on These Sounds
Banging Sounds from A/C Compressor or Heat Pump, Frequent Compressor Replacements?
Reader Question: banging sounds from the compressor
OK. I just reread the instructions and it looks like I can ask a question. In the past 5 years we have replaced 4 compressors. We just replaced the last one and the fan motor. Every once in a while, the unit would make a repeated really loud banging sound as though some metal piece in the fan was whacking another piece over and over. Today I watched the clock
It is almost at every hour, but not at the same time. Each time the noise lasts 3-4 minutes. The A/C company and their electrician have no clue what this is. Also, the unit often trips the circuit breaker. Not necessarily when this noise comes on. We are incredibly frustrated. Any ideas as what could be causing this? Thank you. - Dina
Reply: common sources of loud BANG noises in air conditioning or heat pump equipment
Dina, my OPINION is that if you are replacing compressors 4 times in 5 years something is drastically wrong. I can't guess whether the problem is an innate system design pressure, poor or damaged equipment being installed, or installation errors.
But I share your frustration. I think it's time to talk candidly (but without threats or screaming) with the A/C company's service manager and to ask that they send someone who is trained and experienced to help diagnose this problem. And when you're told what problem was diagnosed, if you don't understand the explanation, ask for more help with understanding it until it makes sense.
Thank you so much. Here's the problem. We just changed service companies , because we were not satisfied that the old one was doing a good job. This one decided that the compressor and then the fan needed replacing. They've had two sets of technicians out here and neither could figure out the problem. There is nothing hitting the fan (so they say). The problem is that they are never here when the sound happens, though
I did record the sound for them. They said it was nothing like anything they've heard before. They are coming out this morning again and we will see what they can find. Thank you for your "opinion". - Dina
The tech was here again. He noticed that the last guy had installed a booster. He disconnected it to see if it helps. Meanwhile, I'm wondering if the noise has something to do with the unit working harder in the hot weather because I hadn't noticed the noise at all today and it's much more comfortable outside. I guess I won't know until it turns really hot again. - Dina
Even with the booster disconnected, it's still making that banging metal sound. - Dina
Dina if the banging clanging is a compressor noise see the article titled NOISES, COMPRESSOR CONDENSER
Sounds like very loud bering noise on start up and shut down from a 1 year old heat pump compressor - Ray 12/5/11
Ray, a bearing noise, often a horrible clanking, banging, or rattling, is generated by a wobbling of a rotating shaft that is no longer evenly supported by bearings that are intended to permit it to rotate with minimal friction. If you hear bearing noises from an A/C compressor motor I suspect that the motor is failing, or that a similar noise is being made by damaged refrigerant valves in the compressor head. But first check that the motor mounts are secure. Sometimes a motor can make a clank or thunk at startup because one or more of its mounts has come loose.
Buzzing Sounds at Air Conditioner or Heat Pump & Buzzing noises after A/C cooling coil change-out, Diagnosis, Repair
Reader Question: loud buzzing noise from compressor unit
I had problems with my central unit freezing up and dripping water on my fan motor.. decided to have a technician change out my coil inside.. when he left my central unit outside starting making noises i never heard before.. my air conditioner kicks on inside first then after a couple of minutes it tries to kick on outside , it makes a loud noise then it runs finally and quiet like a central unit should run outside.. what is causing this all of a sudden, never had problems until he changed my coils out..not calling him back to my house. Bruce McCann
HVAC compressor buzzing video: the HVAC noise diagnosis introduction near the top of this page includes a video example of brief buzzing at the fan/compressor outdoor unit along with some possible explanations. Below we discuss several A/C or heat pump compressor noise observations and possible explanations.
Bruce, I am not clear on why a coil freeze-up indoors would lead to changing the outside coil - maybe low refrigerant or improper high side vs low side pressures? In any case, I would indeed give the service tech a call, tell him or her what you are observing, and give the technician an opportunity to return, see what's wrong, and fix it. Most technicians want their work to be correct and successful. Let us know what you're told - it will surely help other readers.
Question: can you tell us what the attached air conditioner buzzing clanking sound recording means?
Attached is a few seconds of the noise made by our Kenmore air conditioner/heat pump, when the propellers start turning, about 10 seconds into the recording. It was much worse in the winter with the heat pump, so we heated with oil only.
It was so bad, the house rattled inside. The compressor and motor were replaced a few months ago, but the noise persisted and the maintenance company gave up after eight visits. When the weather got hot, we decided to give the air conditioner a try.
The air conditioner was working without us noticing any noise but now we can hear it, as you can tell from the recording. What can we do? Your help would be greatly appreciated. - L.G.
Recording of Kenmore Air Conditioner Noise - buzz, rattle, hard-start
Honestly, I'm not sure , but the sound we heard in your recording sounded like a mix of buzzing and rattling. I've heard sounds similar to this from both a failing crankshaft in a motor and from an air conditioner compressor that was liquid slugged with refrigerant due either to an improper charge or a malfunctioning refrigerant metering device.
If that's right we may be hearing a hard-starting compressor.
I have two suggestions: a technician, using a mechanic's stethoscope, ought to be able to pinpoint this noise to the offending part or motor. If the noise is traced to the compressor motor I suspect my guess above is not far off. It is possible that once the system has been running for enough time the noise may fade as the compressor has pushed the refrigerant out to the high side of the system.
Watch out: liquid refrigerant slugging of a compressor motor is a problem that occurs on the low pressure side of the system where the equipment is designed only to move refrigerant as a gas, not a liquid - liquid slugging of refrigerant at the compressor motor is likely to destroy it.
I hope you've already eliminated more obvious external rattles such as a bad bearing or motor shaft or fan blade ticking against screen or internal component.
At Recordings of A/C or heat pump sounds & noises we have introduced a new HVAC diagnostic feature (thanks to you) where we posted this air conditioner sound recording to permit other readers or experts to offer comments.
Question: Buzzing sounds from air conditioner
My outside fan motor is running but the unit makes a loud buzzing noise every few minutes or so, the motor was replaced last spring. I sprayed the motor shaft with wd40 just to get me by till I can get another fan motor if that is needed. I do not know if the capacitor was replaced or not. the loud buzz only lasts for a few seconds then stops, I just turned the unit back on, Any ideas on what I can do or a place to find a motor?- Rodney Looney
Compressor started producing a buzzer noise which lasted about 4 seconds then stopped and repeated again. The time between buzzes varied from a 10 to 20 seconds. The noise reminded me of the sound you hear on the radio when they do there check of the emergency broadcast system. - Jim
I have a Trane 4 ton gas pack that is making a intermittent buzzing noise when the compressor operates. We are located in Phoenix, AZ and the noise seems to have started this season when temps heated to 100 and above. Naturally, I'm concerned that this might be compressor noise since the unit was manufactured and installed before the AC season in 1994. Thanks for any suggestions you can offer. Doug
The noise pattern may be different from when I first noticed it. I checked the pressures, for the first time since we got the house 8 years ago and and added 4 lbs of R-22 to get it back to normal operating conditions at 95F. The performance isn't noticeably different, but the noise pattern may have changed somewhat, while the sound is about the same, when it does occur.
Reply: Buzzing Sounds at an A/C or Heat Pump System May Mean Failing Electrical Parts
Rodney: if you need a new condenser fan motor you should be able to match the original by taking the old one to your local HVAC supplier, or you can probably find a replacement online. I'd be sure you note the motor information and specs from it's data tags or just bring in the old motor to your supplier. Watch out - don't keep replacing motors unnecessarily. A bad fan motor contactor relay or even a loose wire could also cause buzzing in the condenser/compressor unit outdoors. .
Jim: sounds like your compressor is having trouble starting up? Or does it buzz but run ok otherwise?
buzzing sounds from an air conditioning component might be a failing electrical component and could involve even a fire risk; I'd try to track down more carefully where the buzzing is occurring. A burned compressor contactor relay, for example, might buzz.
I was looking around another site and the owner mentioned that the compressor suspension mechanism can break and cause noise that sounds like a bad bearing.
A friend of mine knows a person in the refrigeration business and after my friend described the problem, he said it sounded like a broken spring in the compressor suspension.
I guess I am going to have to replace the compressor before the start of the next season, if I make it through this one.
The compressor has rotolock connections, and I would like to avoid any cutting/sweating operation if I can reasonably-safely avoid it. Thanks for your help. - Doug
I found a video on You Tube that shows disassembly of a compressor like mine. I don't think there is a broken suspension, but I would believe bearing noise. I don't understand how it can be so intermittent. Under certain conditions, something resonates and makes a real racket.
Doug we see filter dryers installed at both sides of the compressor. It depends ... if a system is thought to be contaminated there are advantages of having a filter at both ends of the compressor motor, and it certainly doesn't hurt. - DF
Question: A/C System Buzzing noises for 2 seconds, bad start/run capacitor?
Outdoor unit makes a buzzing noise for about 2 seconds & stops. Fan never starts turning. I was standing by unit when this happened for the third time & manually started fan turning.
We seem to have traced this A/C buzzing noise to a bad start/run capacitor - Hill
Continue Reading more Noise Descriptions at noise group 2 beginning with CLANKS CLUNKS from air conditioner or heat pump system
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.