Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of HEATING & COOLING TERMS
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Goodman gray flex duct HVAC ductwork deterioration: this article discusses Goodman™ brand gray flex duct disintegration failures with references to product failures by manufacturers of similar flexible duct work products. We include photographs illustrating heat-damaged flex-duct covering materials and we explain the implications on home energy costs when this material is installed in buildings.
We include, for comparison, other gray plastic covered flex-duct materials that do not appear to disintegrate in hot attics, using Certainteed's Certaflex-G25 as an example.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Air conditioning duct system defects include a remarkably wide range of errors, from failure to supply cool air or failure to even circulate air in the building, to health hazards such as use of asbestos material in or on duct work, to very dangerous conditions such as drawing heating equipment combustion gases into the building cooling (or heating) air.
This article describes Owens Corning Valueflex™ brand gray flex duct failures that appear as loss of the gray plastic duct covering due to brittleness that appears to be caused by exposure to heat (such as in a hot attic), with references to product failures by several manufacturers of flexible duct work, , including ATCO™ Ruber Products, Alloy Systems™, Goodman™ flex duct, Owens Corning™ flex duct, Owl™ flex duct.
We believe that none of these defective flex duct products is currently sold (2010) but both may be found in older homes. Note: not all Owens Corning flex duct products share this defect and disintegration problem.
The loss of the protective plastic covering on flex duct poses several concerns including loss of the duct insulation, increased air conditioning system operating costs, and possibly air leaks out (if supply ducts are damaged) or un-wanted attic debris leaks in (if return ducts are damaged), and in-duct condensation in the HVAC system leading to mold and indoor air quality concerns.
This Goodman gray flex duct or "flex duct" air conditioning duct work material is a defective product.
In hot attic spaces or where exposed to UV light, the plastic of this flexible air conditioning duct material disintegrates leaving its fiberglass insulation exposed to also disintegrate, leak, or possibly blow into the building living space.
Replacement of the duct work is required - a significant expense. - Thanks to Jon Bolton for these photos. of Goodman gray flex duct disintegrating in an attic.
Where this duct is found in a building it should be replaced. When a heating or air conditioning flex-duct product has lost its exterior plastic covering the effects are these:
Below at Technical Reviewers & References we include Flexible Air Duct Installation Manuals, standards, guidelines, and contact information for several flexible air duct manufacturers as well as access to Flexible Duct Performance & Installation Standards provided by the Air Diffusion Council.
List of plastic-covered flexible HVAC duct products that appear to deteriorate in hot spaces like attics
Readers concerned with deteriorating plastic and fiberglass-covered flex duct in buildings should see the several HVAC duct failure reports listed just below.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about Goodman gray flexduct deterioration in building HVAC duct systems
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.