Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of HEATING & COOLING TERMS
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
FAN NOISES, HVAC
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Diagnose & fix ice or frost blockage of the cooling coil or evaporator coil in an air conditioning / heat pump system. We explain the causes of cooling coil ice formation and blockage. Some of these causes can be repaired by something as simple as changing a dirty air filter or cleaning a dirty coil or blower fan.
We discuss simple checks you can make that may avoid a costly service call if your air conditioner is not working. . This article forms part of our series on how to diagnose an air conditioner or heat pump that is not cooling: this article explains how to diagnose and correct air conditioning problems like lost or reduced air conditioner cooling capacity, reduced or no cool air flow, reduced or no actual lowering of the air temperaturer, or an air conditioner that won't start.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Cooling Coil Ice-Up on the air conditioner air handler or evaporator coil: A second result of the reduced air flow due to a dirty air conditioning filter can cause
the evaporator coil (the cooling coil) in the
air handler to become blocked by ice, stopping or significantly reducing cool air output from the system.
Cooling Coil (Evaporator Coil) Leaks, Condensing Coil Leaks: if your A/C system used to work fine but now is blowing only warm air, it is possible that you have lost refrigerant in the system. A refrigerant leak can occur anywhere in the refrigerant piping system, in the cooling coil, or in the condensing coil.
You'll need an HVAC technician to find and repair the leak problem. If the leak is in a refrigerant line it can usually be soldered and sealed and the system re-charged. If the leak is in a cooling coil or condensing coil, the coil probably needs to be replaced. We explain this topic in more detail below at Air Conditioner Refrigerant Problems - Refrigerant Leaks, Low Refrigerant, Wrong Temperatures.
Watch out: something as simple as a blocked or dirty air filter or dirty cooling coil can lead to frost build-up on the cooling coil. That's because the reduced airflow over the cooling coil may permit it to run colder than normal.
Clogged Air Conditioner filters can lead to lost cooling capacity first, because the clogged filter reduces the air flow
through the system, meaning that you'll feel less air flow at the supply registers than was previously present, and second because the low air flow may lead to partial or completed frost blockage of the cooling or evaporator coil in the air handler.
Air Filter problems: not enough air coming out of air conditioning ducts?
Continue reading at A/C COOLING COIL ICE FROST for complete diagnosis & repair procedures for coil frosting or icing troubles
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) on How to Diagnose & Fix Cooling or Evaporator Coil Ice Blockage
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Question: My Air Conditioner won't turn off - what to do?
Carla said: My outside air unit will not turn off on its own. I have to manually turn the breaker off to turn it off. Does anyone know why or how I can fix it?
Carla if your A/C won't turn off it could be that the thermostat is set to a temperature that the system cannot reach - due to lost cooling or due to a setting below the capability of the system. If your A/C won't turn off even if you set the thermostat to a temperature that is above the current room temp, then the thermostat or an A/C control board or switch is bad and needs replacement - in that case you need a service call from a trained HVAC Technician. See OPERATING TEMPERATURES HVAC and also CONTROLS & SWITCHES, A/C - HEAT PUMP
Question: My Air Conditioner (or heat pump) keeps cycling on and off too rapidly - what might be wrong? short A/C on-cycle problems
Joe said: short cycling air conditioner compressor diagnosis: I have the same problem as Mathew: my A/C compressor cycles on and of every ~10 seconds. I is about 5yr old. What can we do to fix this system. Please help. Thanks!
Matthew said: short cycling air conditioner problems: Our air conditioning compressor cycles on and of every few seconds or minutes. What can we do to fix this systems not even a year old
Five causes of a home air conditioner compressor short cycling on and off too rapidly - Short Cycling Air Conditioner Diagnosis & Repair
DanJoeFriedman (mod) said to Joe and Matthew (re questions just above):
In sum, you need a service call from a professional to correctly diagnose and repair the problem. Ask the service tech what she/he found and let us know - what you find will help other readers.
If your air conditioner or heat pump has the opposite problem, staying on too long, see LONG-ON CYCLING AC COMPRESSOR.
Question: Why is my A/C not producing enough cool air?
A/C not producing enough cool air - I had my air conditioning system gassed up last week - $210. ! The unit is not producing enough cold air. The unit is set on 72 and does great at nights but during the day where the temp. outside is reaching mid 90"s it's getting up to 80 in the house. Is my duct work screwed up? How do you repair trailer metal ducting? - Amanda
90 degrees outside and 83 inside with thermometer at 76. Cools off to 76 when sun starts to go down and house then gets cold. New capacitor and condensor just put in. Help. - Ginny 5/17/12
Amanda: if your system is not cooling there could be any of a number of problems - see the article above as a place to start. If your basic complaint is that the A/C temperature at the supply registers is cool enough but the volume of air flow is too weak, we'd start by:
Weak air conditioner air flow - is there a relationship between refrigerant charge level and weak cool air flow rate?
Les said: Weak air conditioner air flow: Our A/C was serviced two months ago and the repairman said it had a leak. $400 later it was recharged with coolant and now the ac is doing the same thing. Very little pressure coming out of vents and no cold air coming out. Does anyone know what I can do for the weekend? It is stifling!!!! See A/C Air Duct Problems
DanJoeFriedman (mod) said:
Les: A leak that was fixed by a re-charge is not as good a repair as a leak that was fixed by finding and fixing the leak - you'll just have to keep adding refrigerant.
But weak air flow out of the vents would not be due to a refrigerant leak; more likely a clogged filter or crushed or disconnected ductwork, or a blower fan problem.
Weak air Flow traced to Clogged Air Filters: Can Clogged Air Filters Affect the Room Thermostat?
(May 13, 2011) Jim said: If air conditioner filters are clogged will it cause the thermostat to shut off?
Jim: clogged A/C filters won't cause a room thermostat to shut off. The thermostat responds to room temperature. However clogged A/C filters that reduce air flow, cause coil frosting, or otherwise reduce or stop the flow of cool air into the room where the thermostat is located would mean that the thermostat would remain "un-satisfied" and should mean that the thermostat says "on" - continuing to call for cooling. See AIR FILTERS for HVAC SYSTEMS
Air Filters & Cooling System Amperage Draw: Could Removing the Air Filters Cause the Electric Motor in the Air Handler to Draw Higher Amps?
Question: got one for you. i put an ammeter on my air handler and it read 8.25 amps, I removed the filters and it went up to 9.75 lmao at the situation the amperage should have gone down. what gives here
Reply: causes of variations in electric motor efficiency and current draw measured in amps
Lost: this amps variation is beyond my expertise, but in general reducing the load on an electric motor will show up as lower amps or current draw, not higher amps. Here are two interesting explanations of amps or current variations on an electric motor that I found when researching the question:
2. Load variations and electric motor efficiency: A second possible source of seeing higher amps or current draw on your blower motor when you pulled out the air filters and thus reduced the load on the blower motor might be illuminated by this U.S. DOE pamphlet "Determining Electric Motor Load and Efficiency" - Quoting: "Most electric motors are designed to run at 50% to 100% of rated load. Maximum efficiency is usually near 75% of rated load. Thus, a 10-horsepower (hp) motor has an acceptable load range of 5 to 10 hp; peak efficiency is at 7.5 hp. A motor’s efficiency tends to decrease dramatically below about 50% load."
Question: what causes warm suction lines in an air conditioner or heat pump system? Warm A/C suction line (should be cold) and zone control dampers that stopped working
JMONTE said: warm A/C suction line question: After my condenser is turned on for about 4 minutes the suction line starts to get warm to the touch. can you tell me what the problem may be
JMONTE: If the HVAC suction line gets warm, you may be out of refrigerant, or the system may be running in heating mode if it's a heat pump. See OPERATING TEMPERATURES HVAC.
Becky, If a motorized HVAC zone control damper is not opening or closing, most likely the motor has failed, or the thermostat that operates that zone control is off or set in an incorrect position. See ZONE DAMPER CONTROLS
Becky said: motorized air conditioning zone dampers not working
My house has "zone" control with dampeners to close off the upstairs over the garage room unless that thermostat is on - the room is not cooling. I have located the damper under the house. What are some causes for the damper not opening and how to repair them? condensation, motor to damper? silicon glued properly?
Questions & answers or comments about air conditioner system diagnosis & repair
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References