Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
A/C DATA TAGS
A/C DIAGNOSTIC FAQs
A/C TYPES, ENERGY SOURCES
AGE of AIR CONDITIONERS & HEAT PUMPS
AIR CONDITIONER BTU CHART
AIR CONDITIONER COMPONENT PARTS
AIR FILTERS for HVAC SYSTEMS
AIR FLOW MEASUREMENT CFM
AIR HANDLER / BLOWER UNITS
BACKUP HEAT for HEAT PUMPS
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
CLEANING & Legionella BACTERIA
COMPRESSOR & CONDENSING COIL, A/C
CONDENSATE HANDLING, A/C
CONTROLS & SWITCHES, A/C - HEAT PUMP
COOL OFF HEAT Thermostat Switch
COOLING CAPACITY, RATED
COOLING COIL or EVAPORATOR COIL
DATA TAGS on AIR CONDITIONERS
DEFINITION of HEATING & COOLING TERMS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DUCT SYSTEM & DUCT DEFECTS
DUST, HVAC CONTAMINATION STUDY
EDUCATION, HVAC SCHOOLS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
EVAPORATOR COIL or COOLING COIL
EVAPORATIVE COOLING SYSTEMS
EXPANSION VALVES, REFRIGERANT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON THERMOSTAT SWITCH
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN NOISES, HVAC
GAS DETECTION INSTRUMENTS
GAS LAWS & CONSTANTS
GAUGE, REFRIGERATION PRESSURE TEST
HEAT LOSS (or GAIN) IN BUILDINGS
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HUMIDITY LEVEL TARGET
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MANUALS & PARTS GUIDES - HVAC
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
NOISE AIR CONDITIONER / HEAT PUMP
ODORS in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
OPERATING TEMPERATURES, AIR CONDITIONER
PORTABLE ROOM AIR CONDITIONERS
PRESSURE READINGS, REFRIGERANT
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
REFRIGERANTS & PIPING
RETROFIT SIZING for A/C or HEAT PUMPS
SEER RATINGS & OTHER DEFINITIONS
SPLIT SYSTEM AIR CONDITIONERS & HEAT PUMPS
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Charles' Law: this article describes and defines Charles Law, explaining the role of temperature in gas pressures, including examples of using Charles Gas Law to explain what happens to air in a water storage tank, LP gas in a gas tank, oil & fumes in an oil storage tank, or air conditioning /heat pump refrigerant liquid & gas volumes inside of an air conditioning or heat pump system.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Charles Law Describes How Water Tank Air Pressure Changes With Shifts in Air Temperature in the Water Tank
What about the effects of changes in ambient temperature around a water storage/pressure tank? Suppose we wonder if seasonal temperature changes might cause important changes in in-water-tank pressure. For simplicity we'll work with a fixed volume full tank of just air. We'll change the temperature of the tank and its air from 60 deg.F. to 90 deg.F.
As most people would guess from practical experience, raising the temperature of a container of air while keeping the container size fixed will increase the pressure of air in the container.
Charles' Law: V1/T1=V2/T2 says that if we raise the temperature of a cubic foot of air, the air will want to occupy a larger volume.
30gal of air (or 4 cu. ft.) of air at 33 psi and at 60 degF is changed to 90 degF (by the warming ambient air) while the container size is kept constant.
Charles would say: 4cu.ft./60degF = NEWCUFT/90degF or 0.066 = NEWCUFT/90 0.066 x 90 = NEWCUFT or about 6 cu. ft.
This is 2 cu. ft. more than where we started, or a 50% increase in the starting volume of air.
Technical note: when working with the gas laws and temperature, all temperatures have to be converted to Kelvins or "K" - their Kelvin equivalent before the law can be applied. The Kelvin temperature scale relates temperature to absolute zero, where 0 Kelvins = absolute zero. We can convert Fahrenheit to Kelvins using this simple formula: K = (degF + 459.67) / 1.8.
We can convert Kelvins to Fahrenheit using this formula: degF = (K x 1.8) - 459.67. And for folks who work with Celsius, we can convert Celsius to Kelvin with this formula: K = degC + 273.15, or we can conver4t from Kelvin back to degrees of temperature in Celsius with this formula: degC = K-273.15. (However for temperature intervals one degree Kelvin = one degree Celsius.) Also, 0 degrees Kelvin = -273.15 degC = -459.67 degF.
Continue reading at COMBINED GAS LAW or select a topic from the More Reading links shown below. or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References