HOW AIR FILTERS WORK - CONTENTS: How air filters work to remove particles from the air stream: impaction, interception, diffusion filtering methods. What airborne particle sizes are an IAQ concern? - particle size vs. air filter characteristics vs. indoor air quality. Air filter maintenance.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
How do HVAC air filters work:
This article explains and explain just how air filters for HVAC systems actually work to trap and remove particles from indoor air. This website answers almost any question you might ask about air filters for heating or air conditioning systems. The page top photograph is of a low-MERV HVAC filter in an air handler.
How do air filters actually remove particles from the airstream?
Here we explain the three methods by which HVAC air filters work to capture and remove airborne particle contaminants from building air: impaction filtering, interception filtering, and diffusion filtering.
In these articles we are referring to filters installed on central air conditioning or central heating systems that move air through air handlers and duct systems. Standalone "air cleaners" are generally ineffective in buildings.
In articles at this website we explain how an air conditioning service technician will diagnose
certain common air conditioning system failures or defects. We include photographs to assist readers in
recognizing cooling system defects.
This photograph (above-left) shows a soiled surface of a conventional air filter up close. The fibers are clearly visible but not the openings through which air has to pass.
If we look at a high efficiency, high MERV or HEPA air filter under a microscope we'll see a mat of randomly crisscrossed fibers of filter material (fiberglass, polypropylene, paper, or other materials).
The space between the filter fibers
will be larger than the smallest particle size which the filter is asserted to remove. So how do these filters stop the small particles? Let's look at three air filtration mechanisms in order of decreasing particle size:
Impaction filtering: First, some airborne particles smack directly into a filter fiber, either because they happen to be on that unlucky (for them) trajectory or more likely because the particle is so large that it can't pass through the opening, or
part of the particle smacks into the filter fiber.
Air filter scientists call this method "impaction". Impaction captures larger particles which in a HEPA system are those larger than about 0.4u.
Interception filtering: Second, some airborne particles moving in the airstream past the filter happen to be close enough to a filter fiber that
they stick to it.
How close? the particle has to be closer to the filter fiber surface than one radius or diameter of the particle itself. In other words, a 2u particle which is only 1u away from a fiber will probably stick to the fiber.
Air filter scientists call this method "interception". Interception captures particles mostly in the 0.3u size to 0.1u size.
Diffusion filtering: Third, very small particles, say below 1u in size, collide with larger gas molecules swirling around in the air turbulence
caused by air moving by the filter fiber.
This collision, called "diffusion" in filter science, causes the particle to zig zag out of the airstream passing through the filter opening and to stick to the filter surface.
What airborne particle sizes are an IAQ concern?
What mold, house dust dust, allergen fragment, mite fecal, cat dander, or other airborne particle sizes are a concern for indoor air quality?
In the photograph shown here the large black Stachybotrys chartarum mold spores can be seen against our eyepiece micrometer which, after
calibration, shows that these particular spores were about 7u x 15u in size.
The brownish tubular structures are fungal hyphae. Another, smaller fungal spore
is in the background. What's not addressed by some of the science in the air filtration and IAQ field is just what particle sizes are a worry.
In general, larger particles, say 30u or 50u or long fibers, say 200u, are so big that they tend to be filtered in the nose of a human breathing that air. (1u here means 1 micron in size).
A more complete discussion about the size and behavior of problematic indoor air particles which form
an indoor air quality concern can be read at PARTICLE SIZES & IAQ.
Continue reading at MISSING / LEAKY AIR FILTERS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
(Mar 2, 2015) Jessica Allen said:
How offten should the fliter be checked and changed in a apartment G20 series unit?Is it normal for my heater to click 12 times be for it actually ignites?And every time i hear the ingnite noise what does that mean ? I have lived in this apartment 4 years and just recently it started clicking 12 or 15 times be for my heater kicks on Please help
On the air filter check and change schedule, the answer is it depends on the filter type and indoor dust level and hours of operation of the system that draws air through the filter. I would start with a monthly inspection. If the filter is not visibly clogged or dirty after the first month, check again in 30 days.
For trouble with the igniters on a gas furnace you should call your heating service technician as there are both reliability and safety concerns involved.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Thanks to Mark Cramer, Tampa Florida, for assistance in technical review of the "Critical Defects"
section and for the photograph of the deteriorating gray Owens Corning flex duct in a hot attic. Mr. Cramer is a Florida home inspector and
home inspection educator.
Thanks to Jon Bolton, an ASHI, FABI, and otherwise certified Florida home inspector who provided photos of failing Goodman gray flex duct in a hot attic.
"Air Conditioning & Refrigeration I & II", BOCES Education, Warren Hilliard (instructor), Poughkeepsie, New York, May - July 1982, [classroom notes from air conditioning and refrigeration maintenance and repair course attended by the website author]
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones