A/C or heat pump compressor/condenser unit installation mistakes:
This air conditioning repair article discusses the installation errors in air conditioning compressor and condensing units such as improper location, blocked air flow, out of level, or not properly supported.
We discuss required equipment clearance distances, refrigerant line piping support and routing, and problems with shrubbery or other air flow blockages that can cause overheating, higher operating costs, and reduced compressor motor life.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
A/C and heat pump compressor/condenser installation, location, and maintenance tips provided here include attention to compressor support pads and avoiding air conditioning refrigerant leaks are addressed.
If readers return to the first chapter or view the A/C chapter index, the major components of an air conditioning system are described, sketches and photographs are provided, and common defects for each component are listed along with visual or other clues that may suggest a problem or probable failure of A/C components.
Sketch at left provided courtesy of Carson Dunlop Associates.
If your air conditioning or heat pump system has lost its cooling capacity or won't start
see REPAIR GUIDE for AIR CONDITIONERS.
See HOW TO DETERMINE COOLING CAPACITY of air conditioning equipment if the system seems to be working but is inadequate to cool your building.
Typical outside air-cooled A/C compressors require a minimal clearance around the unit to provide adequate air flow so that the condenser coils will be cooled efficiently.
Both of the air conditioning installations shown above are tipping and the left hand compressor/condenser unit was actually leaning on the house wall!
Air conditioning compressor/condenser units mounted too close to a wall, surrounded by shrubs, or multiple units located too closely together may not receive enough cool air flow to function properly. The result can be a shorter compressor life (expensive) and/or less efficient cooling operation (higher operation costs).
These four air conditioner compressors were found jammed into a wall niche along a street in Queretero, Mexico. These units may have a short life before needing replacement.
Where there simply is not adequate space to provide proper air circulation around an air conditioning compressor or multiple compressors, it may be a good idea to let the building owner know that the units won't have a long life.
This collection of air conditioning compressors are too many too close together - they will be fighting for cooling air around the condenser unit, increasing operating cost and shortening air conditioner compressor life.
Adding to this scene is the overgrowth of shrubs along the compressor/condenser units. The owner didn't want to see these "ugly" devices but she should have kept the plants trimmed off of the units themselves to allow airflow.
The shade was a great idea however, so long as these are just air conditioning units and not heat pumps that want warmth in winter.
One of our clients was "punished" by their air conditioner installer when she said that she didn't want to see or hear the compressor/condenser units, and when she was installing nine of them at her large home.
The installer built a rack allowing the units to be stacked on top of one another, three across and three high, with very little air space between.
Then the installer put up a stockade fence just a few inches away from the compressor/condenser units. They were hard to see, it was true, and hard to service. But as the property manager confirmed, they were having to replace several of these units every few years.
I believe it was because the units ran excessively hot all the time, lacking adequate air and clearance. Photo withheld for privacy.
Please see our detailed article about refrigerant line piping installation, inspection, defects, repairs, found at REFRIGERANT PIPING INSTALLATION. Excerpts below:
Absence of slack in the coolant lines at the compressor units can cause leaks: should the compressor move, perhaps because its supporting pads settle, there will be likely leaks at these lines. You should review this question with your HVAC service person. This item may be deferred until next maintenance or service.
Protection from mechanical damage on all refrigerant lines is important to prevent leaks.
CarsonDunlop Associates' sketch (left) shows the indoor air handler unit, not the outside compressor/condenser unit, but the illustration makes clear that the refrigerant piping loop needs to be properly placed and the piping slope should be downwards from the evaporator unit towards the compressor/condenser unit.
Also, referring lines should not be buried underground. Details are at REFRIGERANT PIPING INSTALLATION.
Missing insulation on the refrigerant lines, particularly on the larger suction line, will cause condensation and drips from the lines in humid areas. I've seen very costly building damage where lines were not properly insulated indoors: condensate drips wet gypsum board walls, leading to a costly mold remediation project.
Blocking air flow through the outdoor A/C or heat pump compressor/condenser unit is a really bad idea that shortens equipment life (as the equipment runs hotter) and increases system operasting costs (for the same reason - hotter opeating temperature means lower efficiency during the cooling season).
Air conditioning or heat pump compressor/condenser units mounted too close to a wall, surrounded by shrubs, or multiple units located too closely together will probably not receive enough cool air flow to function properly.
And even worse, compressor/condenser units that are too close together not only have to fight for their incoming cooling air, but they may veed hot exhaust air to one another, increasing their operating temperatures still further.
Details about the recommended clearance distances for A/C or heat pump compressor/condenser outdoor units are found at CLEARANCE DISTANCE, HVAC
Outside A/C compressors are typically supported on a concrete pad, concrete blocks, or a vinyl pad such as the one shown in the photo at page top. The air conditioner compressor support pad should be level and secure against movement.
Compressors which are badly out of level may fail to function properly and need adjustment. Tipping and moving compressors can also cause can cause leaks in refrigerant lines, leading to costly air conditioning service calls to evacuate and recharge the system after repairing the refrigerant leak.
Do not try to move your A/C compressor yourself as you might cause a refrigerant leak or may otherwise damage the equipment.
Ask your A/C service technician to evaluate the effects of any out-of-level conditions of the compressor as well as to comment on the available slack in the refrigerant lines that may be needed to reposition the unit.
For slightly-tipped air conditioning compressors we generally leave them alone but we add support as needed to avoid further movement.
Tipping or leaning air conditioner compressors can lead to so much movement that the refrigerant lines crack and leak, leading to loss of cooling ability. In extreme cases, a tipped condenser unit may fail to operate properly. In the first photo above the compressor is leaning and creeping away from the building and has pulled its connecting wiring and refrigerant line taut.
I expect a problem soon with this unit. In the second photo everything looks awful: the two compressors are too close together and too close to the building wall for adequate air circulation, especially in the larger rear unit in the photo. The safety electrical switch for the air conditioner is falling off of the wall, and the rear unit is sliding off of its support pad. This was a poor air conditioning system installation.
Continue reading at CLEARANCE DISTANCE, HVAC or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see COMPRESSOR / CONDENSER REPAIR - topic home
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
My A/C compressor is out of level just slightly - is that going to make trouble? - Dimc
Dlmc: - requirement to level the air conditioning or heat pump compressor -
Yes the compressor should be level. That detail is found in the installation instructions for air conditioning and heat pump compressors.
Slightly out of level is unlikely to affect operation, but if you consider that the condenser coil expects to receive high temperature, high pressure refrigerant gas that it then cools to a liquid refrigerant, and that the liquid refrigerant needs to flow out of the condensing coil into the refrigerant line, a significant tip out of level may interfere with refrigerant flow and thus system operation.
Also a unit that is out of level and also not secured to a mounting pad may creep due to equipment vibration, risking development of a leak in the refrigerant lines or a torn electrical connection.
(June 11, 2014) Kathy J said:
Our new central air was just installed and we noticed the compressor unit is sitting on the plastic pad but not connected to it, able to slide around on it. Is this normal? Also, the lines going inside the house are covered with a lot of putty at the house (apparently to seal off the holes for insulation)
but the edges of the putty don't appear to be actually touching the vinyl siding of the house.
Did you try calling the installer to ask,that these details be corrected? Certainly if the compressor is really sliding around it will soon fail from a refrigerant line rip and leak or worse, an electrical wiring hazard.
(July 27, 2014) Anonymous said:
What is code in sterling heights mi for outdoor placement of an a/c compressor unit?
(Aug 5, 2014) fred said:
what is the distance or measurement of a condensing fan and condensing coil of a window type unit air conditioner?
In most jurisditions the HVAC equipment must be installed in accordance with the manufacturer's installation instructions. The instructions for your specific unit will call for particular clearances from nearby walls or obstructions that may vary for the different sides of the unit.
For details, in the More Reading links article index bove see the article titled
Got me on this one Fred. Window type air conditioners include the condenser and all coils within the same individual unit or case. Perhaps you're asking about something else.
(Oct 15, 2014) Ir.Muh.Faisal P said:
Can I remove fan motor outdoor that replace with spray water use pump motor fish aquarium. and then Outdoor Unit installed in house (it's likely Window AC). Heat condenser to deliver with water to cooling tower thru pvc pipe. It's considered for temporary use , for example Events etc. Completely event without release freon to air, pipe pvc release OK finish. green act.
I'm impressed and amazed but can't answer this one.
x(May 3, 2015) Anonymous said:
my boss wants to put a ductless split in for a computer lab he wants to locate the condenser package in the crawl space 3 or 4 ft height and non insulated floor. I know this is not a good idea heating the floor of the room your trying to cool, but being a confined space is there any code that needs to be fallowed.
At the very least building codes expect equipment to be installed according to the manufacturer's specifications. Start with those.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website