Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FLOW MEASUREMENT CFM
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
CONDENSATION or SWEATING PIPES, TANKS
DEFINITION of HEATING & COOLING TERMS
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
ELECTRIC MOTOR OVERLOAD RESET SWITCH
EVAPORATIVE COOLING SYSTEMS
FAN LIMIT SWITCH
FAN NOISES, HVAC
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Gasketed air conditioner or heating filters, leaky air filters, washable air conditioning or heater air filters: This article explains and explain leaky air filters and the value of gasketed air filters, followed by comments on the effectiveness of washable air filters. This website answers almost any question you might ask about air filters for heating or air conditioning systems.
We explain how an air conditioning service technician will diagnose certain common air conditioning system failures or defects. In these articles we are referring to filters installed on central air conditioning or central heating systems that move air through air handlers and duct systems.
Standalone or portable "air cleaners" or "air purifiers" are generally ineffective in buildings. We include photographs to assist readers in recognizing cooling system defects.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Readers should also see our INDOOR AIR QUALITY IMPROVEMENT GUIDE article series. The page top photograph is of a low-MERV HVAC filter in an air handler.
A gasketed heating or air conditioning system air filter improves the filter effectiveness. The benefits of a high efficiency air filter material when used in an air handler and duct system are not fully realized if air bypasses the filter around its installation frame due to poor fit or poor installation.
[The filter shown here is not a high quality gasket-type air filter.] That's why some manufacturers emphasize the value of air-sealing gaskets on their products.
Simple observations made in the field will make for agreement with the manufacturers that filter bypass is an issue at some heating or air conditioning installations. When changing an air filter at a return air inlet or at an air handler, when the old filter has been removed, take a look inside the return duct at the return register, or inside the return plenum at the air handler, to see just how much debris is passing the filter.
[The photograph above shows how a badly-fit HVAC air filter can not only leak bypass air into the blower compartment but also it can collapse right into the blower fan - this is a potential fire hazard!]
On an old heating or air conditioning system where filters have been ineffective, not properly installed, leaky, or not maintained and changed on schedule, we often find quite a bit of debris entering the air handler and duct system.
This is in fact so common that most HVAC installers and technicians consider dirty ducts to be "normal". And they're quite correct: typical house dust that has collected inside of a duct system is not normally a toxic substance.
Washable re-usable air filters are very appealing from a cost viewpoint. I would look for data to indicate whether or not the washable filter runs at a lower MERV or filtering efficiency.
In our cascaded filter proposal (discussed at this website) we included and continued to use a washable filter that came with the equipment since it was not reducing the airflow CFM, but we preceded it with other filters for different purposes.
he photograph at above left shows a typical washable metal air filter used in central air conditioning systems, and at above right is a washable foam air conditioning filter used in a portable room air conditioner. Other types of washable air filters are available as well.
At left we illustrate a plastic and nylon washable air filter used in both window air conditioners and in wall-mounted split system air conditioner units.
Unlike the foam type air filter shown above, these plastic and nylon air filters withstand repeated cleaning without disintegrating.
The efficiency of these filters increases as debris begins to settle on the filter surface, but eventually the improvement in air filtration efficiency is offset by reduced airflow - so clean the air filters in accordance with the cooling unit manufacturer's instructions - typically monthly during constant use.
A metallic air filter (shown ) is not very efficient (effective) at trapping airborne particles when it is clean, though efficiency improves as it gets dirty. Other pleated, fabric or paper air filters that are also washable are more efficient at trapping airborne debris.
Be sure to read PARTICLE SIZES & IAQ for a description of the sizes and behaviors of some of the common particles that are an indoor air quality concern.
Continue reading at MISSING / LEAKY AIR FILTERS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about using gasketed & washable air filters and their effects of dirt & debris in HVAC duct systems..
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References