Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SOLAR ENERGY SYSTEMS
AIR CONDITIONING & HEAT PUMP SYSTEMS
AIR LEAK MINIMIZATION
AIR LEAK SEALING PROCEDURE
AIR SEALING STRATEGIES
BIOGAS PRODUCTION & USE
EVAPORATIVE COOLING SYSTEMS
FLOOR FRAMING & SUBFLOOR for TILE
FLOOR POURED FINISH ON CONCRETE SLABS
FLOOR RADIANT HEAT Mistakes to Avoid
FLOOR TYPES & DEFECTS
FRAMING DETAILS for BETTER INSULATION
FRAMING DETAILS for DOUBLE WALL HOUSES
FRAMING METAL STUD PERFORMANCE
FREEZE-PROOF A BUILDING
FROST HEAVES, FOUNDATION, SLAB
GREEN BUILDING CONSTRUCTION CODES GUIDES
GREENHOUSE DESIGN for SOLAR HEATING
GREENHOUSE / SUNSPACE GLARE
HEAT LOSS in BUILDINGS
HEAT LOSS DETECTION TOOLS
HEAT LOSS INDICATORS
HEAT LOSS PREVENTION PRIORITIES
HEAT LOSS R U & K VALUE CALCULATION
HEAT LOSS RATE CALCULATIONS
HEATING SMALL LOADS
HOUSEWRAP INSTALLATION DETAILS
HUMIDITY LEVEL TARGET
INSULATION IDENTIFICATION GUIDE
INSULATION LOCATION - WHERE TO PUT IT
LEED GREEN BUILDING CERTIFICATION
LEED Building Designation & IAQ
MOISTURE CONTROL in BUILDINGS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
RADIANT SLAB FLOORING CHOICES
RADIANT SLAB TUBING & FLUID CHOICES
ROOFING INSPECTION & REPAIR
ROOF VENTILATION SPECIFICATIONS
ROOF ICE DAM LEAKS
SHEATHING, FOIL FACED - VENTS
STRUCTURAL INSPECTIONS & DEFECTS
SUMP PUMPS GUIDE
SWEATING (CONDENSATION) on PIPES, TANKS
THERMAL EXPANSION CRACKS in BRICK
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL IMAGING MOLD SCANS
THERMAL MASS in BUILDINGS
THERMAL TRACKING & HEAT LOSS
VAPOR BARRIERS & AIR SEALING at BAND JOISTS
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VAPOR BARRIERS & HOUSEWRAP
VAPOR CONDENSATION & BUILDING SHEATHING
VENTILATION in BUILDINGS
WATER SOFTENERS & CONDITIONERS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
WINDOWS & DOORS
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
This article discusses how to make accurate measurement of the performance of passive solar heating systems, and the effect of air infiltration and the effect of incidental solar gains on passive solar systems. References to texts and guidelines for sizing thermal mass and using thermal mass are included.
Readers should also see PASSIVE SOLAR PERFORMANCE PROBE and SOLAR HOUSE EVALUATION and readers concerned with accurate calculation of the passive solar designs and similar energy savings assessments should see PASSIVE SOLAR DESIGN METHOD. Contact us to suggest text changes and additions and, if you wish, to receive online listing and credit for that contribution.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
This article discusses how to accurately evaluate the performance of passive solar heating systems and the impact of air infiltration or incidental solar gains on passive heating performance. This material is reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss. The text below paraphrases, quotes-from, updates, and comments an original article, "Remember Thermal Mass?" (see links just above) from Solar Age Magazine and written by Steven Bliss.
How to make a more accurate estimate of the performance of passive solar heating systems
Question: The article entitled "The Best Passive Heating Data Yet" (Solar Age 7/83) seems to be an accurate overview of the Class B monitoring program. However the article does not clearly explain the limitations of the method of deriving the passive solar contribution to building energy demands.
Air infiltration rate skews passive solar gain estimates: While the auxiliary and internal gains of the passive solar heating system are directly measured, the solar contribution is arrived at indirectly by a subtractive technique. There is one potentially big source of error in this technique for estimating passive solar performance, namely the building's air infiltration rate. [See BLOWER DOORS & AIR INFILTRATION for added details about measuring a building's air infiltration rate.] Any error in estimating the air infiltration rate shows up as an error in the estimate of passive solar heat contribution.
Incidental solar gains can skew passive solar gain estimates: Incidental solar gains are another source of uncertainty in estimating the contribution of passive solar heating systems (or cooling systems) to a building's energy use. These include gains through non-south apertures (windows and doors) and the solar heating effect on conduction loads of the building's walls and roof.
For this reason, it would have been interesting to have included a few non-solar homes in the Class B program as controls. -- A.L., Madison WI.
According to Joel Swisher at SERI, the one-time air infiltration measurements made concurrently with the coheating procedure were used to separate out conductive losses from air infiltration losses to obtain the building heat loss coefficient. The overall losses due to air infiltration over the heating season are extrapolated from the blower door and tracer gas results and corrected for average monthly wind speeds.
As for the incidental solar gains, Swisher agrees that this presents a problem but that achieving true scientific controls is not a realistic goal, particularly in inhabited homes. In the 1982-83 season Class B study, SERI monitored non-solar homes for comparison purposes. When the subtractive methodology was applied to these homes, solar gains in the 5 to 20 percent range were found.
This would indicate that some of the poorer performing solar homes monitored are not doing much better than a non-solar home, which is likely to be the case.
Question: Commodor 64 Solar Software
Were there any heat loss and heat gain calculation programs for superinsulation design that ran on a Commodore 64 computer back in the 1980's? - Ed Bond, Washington MA
Most software for passive solar design calculations in the 1980's would work just fine for superinsulated houses. Of the 50 programs for solar calculations listed in the 1985 Spec Guide, five were heat loss/heat gain programs that would run on the Commodore 64. They were available from Compusolar (Jasper AR), and Solarcon (Ann Arbor MI).
Another possibility in that era was Canada's HOTCAN program, devised specifically for highly insulated, tightly-sealed houses. It was available from Hotcan Energy Software, Ottawa, ON, Canada.
House Heat Loss Guesstimating by Turning Off the Heat ?
Several readers have asked why we can't just turn down the heat, wait an hour, and observe the new temperature in a building to form an estimate of the building's rate of heat loss. This is an experiment worth performing, if simply to form a quick subjective view of how quickly a building cools off on a cold day. But there are some serious inaccuracies in the "just turn off the heat and wait" approach to estimating building heat loss.
Here are some things that would be missing from this experiment, and some of these factors are major influences on the variability of a home's rate of heat gain or heat loss. Just turning down the heat and measuring temperature loss in a building fails to measure, estimate, or account for these varying conditions:
Overall it makes sense to have a general idea how a house behaves, such as from the simple "turn down or off the heat" experiment, but you cannot accurately characterize a building's rate of heat loss, nor can you know just how leaky it is, nor will you know where the major sources of heat loss are, with just the simple test of turning heat off and measuring temperature change at an arbitrary time.
These difficulties lie behind other efforts to characterize homes and their energy efficiency. See ENERGY SAVINGS in buildings for our collection of energy-savings articles for buildings, and also see SOLAR ENERGY SYSTEMS and if you are using wind power, see WIND TURBINES & LIGHTNING.
When the object is to save energy in the form of heating or cooling costs, attacking the major points of un-wanted heat loss (or gain in a cooling climate) are likely to be most cost-effective.
Some thoughts on setting priorities of attention are at ENERGY SAVINGS PRIORITIES.
Here we include solar energy, solar heating, solar hot water, and related building energy efficiency improvement articles reprinted/adapted/excerpted with permission from Solar Age Magazine - editor Steven Bliss.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers on how to evaluate the performance of passive solar heating systems in homes.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References