Find theDew Point for Building Condensation
How to read the dew point psychometric chart
DEW POINT TABLE - CONDENSATION POINT GUIDE - CONTENTS: How to find the dew point in building cavities. How to determine the dew point on building surfaces. What is the dew point ? Poor Construction Details Can Lead to Dangerous or Costly Rot to Timber Frame and other Wood Structures
How to Find the Dew Point for Any Temperature & Relative Humidity in a Building
Insulating foam sheathing is becoming fairly common in cold climates. But in most cases, it violates the rule of thumb that the
exterior of a building should be five to ten times more permeable than the interior. This is particularly true with foil-faced sheathings.
[Click to enlarge any image]
Some people argue that it’s all right to use insulating sheathing, because it warms up the wall cavity enough to prevent condensation
problems. This is supported by tests (based on 40 percent relative humidity indoors) done at the U.S. Forest Products Laboratory in
Madison, Wisc. As shown in our illustration above, To find the dew point for any temperature and relative humidity: Start with the temperature, move up to the current relative-humidity line.
Move left to the saturation curve, and down to find the dew point, as shown.
How can you gauge the dew point for
First, you need to calculate the dew point of the interior air during the winter. To be conservative, assume an indoor
relative humidity of 50 percent at 70°F.
That gives you a dew point of about 50°F, according to the chart at above left.
Or see DEW POINT CALCULATION for WALLS for making more precise dew point calculations.
Next, calculate how cold it must be outside before the inside surface of the sheathing will fall below the dew point. The inside surface of the sheathing is where condensation is most likely to occur.
You can calculate the temperature at any point in the wall if you know the total R-value inside and outside that point. The temperature rise through the wall and the R-values are in direct proportion.
For example, in Wall A, when it’s 32°F outside, the temperature at the sheathing surface is 7/18 of the way from 32 to 70, or 47°F, which is below the dew point of the interior air. In Wall B, with two inches of foam, the temperature at the sheathing surface is 53°F — safely above the dew point.
Since the average winter temperature in most of central and northern New England is at or below 32°F, Wall A appears risky unless you use one of the more
permeable rigid insulations (headboard or rigid fiberglass), or have a perfect air/vapor barrier. That’s not a bet you should make.
How to Read a Psychometric Chart to Find the Building Surface Dew Point
[Click to enlarge any image]
Several detailed psychrometric charts useful for determining the dew point are shown and linked-to just below. There moisture is expressed in vapor pressure in mmHg (millimeters of mercury). The curved relative-humidity lines intersect with the diagonal lines to show the dew point for various temperatures and levels of relative humidity.
Dry bulb (Tdb) temperature (chart bottom or "x" axis) is just the measured indoor temperature measured using a standard thermometer.
Relative humidity (RH) is the amount of water in the air. We use the term "relative" humidity because the amount of water that a given volume of air can hold decreases as temperatures drop. (Think of it as cold air being more dense, squeezing water molecules out of suspension in the air.)
So RH is the ratio of the actual water vapor pressure in the air to the water vapor pressure in air that is fully saturated (can't hold any more water) at that same temperature.
Wet bulb temperature (Twb) measures the amount of water that can be taken out of the air (by evaporation) - the old "sling psychrometer" used a simple mercury thermometer with a wet cloth over the sensing bulb to measure Twb by swinging the thermometer around at the end of a string - or properly: a sling psychrometer. Really.
Also see Tools for Measuring Humidity This article describes alternative methods for measuring indoor temperature, humidity, relative humidity.
See the left-most curve, the 100% relative humidity line for a simple case - that's air that is 100% saturated. So on the chart below, notice that on the left-most curve, the wet bulb temperature equals the dry bulb temperature - that is, when the air is fully saturated at 100% RH, no more air water can be evaporated out of the air.
Define Dew Point: Now the good part: the dew point (Tdp) is the temperature at which water vapor just starts to condense out of air that is cooling - for example when warm moisture-laden air contacts a cool surface inside of a wall cavity. Above the dew point the moisture stays in the air. At or below the dew point moisture leaves the air and in buildings, condenses on the cooler surface that the air is contacting. This also means that if you are measuring the relative humidity in a room, the RH number only has meaning if you measure the room temperature at the same time and location.
That's why, for example, when measuring basement humidity we will get different RH measurements in the center of the room than we will find right against a cool foundation wall - we discuss this in more detail at HUMIDITY LEVEL TARGET.
Dew Point Example: in the chart below, if the room temperature (Tdb) is 43 degC and the relative humidity (RH) is 20% (the curved line reading up from 43 degC) then the dew point is 15 degC (reading horizontally across to the left-most curved line and noting the dew point temperature scale set along that curve).
Dew Point Example 2: in the psychrometric chart given below, read up from 50 degC dry bulb temperature to the 20% RH curve, then follow the horizontal line from that point to the left to the outermost curve on the chart. If you don't go blind following this chart (click to enlarge it) you'll see that the Dew Point (Tdp) and also the wet bulb temperature (Twb) at the end of that line is 21 degC. Lots of variations of psychometric charts are available; they will all work about like this.
To convert temperatures from Fahrenheit to Celsius use: Tc = (5/9)*(Tf-32) where Tc= the Celsius temperature and Tf= the Fahrenheit temperature.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"Moisture Problems: Causes and Cures. Understanding moisture problems can steer you free of trouble", Steve Bliss: Building it Right, Solar Age, March 1983 p. 37, 38. -- Adapted with permission, from original material to form this web page article.
ASHRAE resource on dew point and wall condensation - see the ASHRAE Fundamentals Handbook, available in many libraries. The following three ASHRAE Handbooks are also available at the InspectAPedia bookstore in the third page of our Insulate-Ventilate section:
2005 ASHRAE Handbook : Fundamentals: Inch-Pound Edition (2005 ASHRAE HANDBOOK : Fundamentals : I-P Edition) (Hardcover), Thomas H. Kuehn (Contributor), R. J. Couvillion (Contributor), John W. Coleman (Contributor), Narasipur Suryanarayana (Contributor), Zahid Ayub (Contributor), Robert Parsons (Author), ISBN-10: 1931862702 or ISBN-13: 978-1931862707
2004 ASHRAE Handbook : Heating, Ventilating, and Air-Conditioning: Systems and Equipment : Inch-Pound Edition (2004 ASHRAE Handbook : HVAC Systems and Equipment : I-P Edition) (Hardcover)
by American Society of Heating, ISBN-10: 1931862478 or ISBN-13: 978-1931862479
"2004 ASHRAE Handbook - HVAC Systems and Equipment The 2004 ASHRAE HandbookHVAC Systems and Equipment discusses various common systems and the equipment (components or assemblies) that comprise them, and describes features and differences. This information helps system designers and operators in selecting and using equipment. Major sections include Air-Conditioning and Heating Systems (chapters on system analysis and selection, air distribution, in-room terminal systems, centralized and decentralized systems, heat pumps, panel heating and cooling, cogeneration and engine-driven systems, heat recovery, steam and hydronic systems, district systems, small forced-air systems, infrared radiant heating, and water heating); Air-Handling Equipment (chapters on duct construction, air distribution, fans, coils, evaporative air-coolers, humidifiers, mechanical and desiccant dehumidification, air cleaners, industrial gas cleaning and air pollution control); Heating Equipment (chapters on automatic fuel-burning equipment, boilers, furnaces, in-space heaters, chimneys and flue vent systems, unit heaters, makeup air units, radiators, and solar equipment); General Components (chapters on compressors, condensers, cooling towers, liquid coolers, liquid-chilling systems, centrifugal pumps, motors and drives, pipes and fittings, valves, heat exchangers, and energy recovery equipment); and Unitary Equipment (chapters on air conditioners and heat pumps, room air conditioners and packaged terminal equipment, and a new chapter on mechanical dehumidifiers and heat pipes)."
1996 Ashrae Handbook Heating, Ventilating, and Air-Conditioning Systems and Equipment: Inch-Pound Edition (Hardcover), ISBN-10: 1883413346 or ISBN-13: 978-1883413347 ,
"The 1996 HVAC Systems and Equipment Handbook is the result of ASHRAE's continuing effort to update, expand and reorganize the Handbook Series. Over a third of the book has been revised and augmented with new chapters on hydronic heating and cooling systems design; fans; unit ventilator; unit heaters; and makeup air units. Extensive changes have been added to chapters on panel heating and cooling; cogeneration systems and engine and turbine drives; applied heat pump and heat recovery systems; humidifiers; desiccant dehumidification and pressure drying equipment, air-heating coils; chimney, gas vent, fireplace systems; cooling towers; centrifugal pumps; and air-to-air energy recovery. Separate I-P and SI editions."
The National Institute of Standards and Technology, NIST (nee National Bureau of Standards NBS) is a US government agency - see www.nist.gov
"A Parametric Study of Wall Moisture Contents Using a Revised Variable Indoor Relative Humidity Version of the "Moist" Transient Heat and Moisture Transfer Model [copy on file as/interiors/MOIST_Model_NIST_b95074.pdf ] - ", George Tsongas, Doug Burch, Carolyn Roos, Malcom Cunningham; this paper describes software and the prediction of wall moisture contents. - PDF Document from NIS
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones